<?xml version="1.0" encoding="UTF-8"?>
<!-- GXML Toolbox V3.11 R20091211;  http://www.gaeb-toolbox.de/ 
 gtcConverter.dll used version 2013.04.11  -->
<GAEB xmlns="http://www.gaeb.de/GAEB_DA_XML/200407">
 <GAEBInfo>
  <Version>3.1</Version>
  <VersDate>2009-12</VersDate>
  <Date>2025-10-27</Date>
  <Time>17:57:10</Time>
  <ProgSystem>/ GXML Toolbox V3.11 R20091211</ProgSystem>
  <ProgName>ARRIBAp V14.4.355</ProgName>
 </GAEBInfo>
 <PrjInfo>
  <NamePrj>20-A03</NamePrj>
  <LblPrj>Kulturanum neu gestimmt</LblPrj>
  <Cur>EUR</Cur>
  <CurLbl>Euro</CurLbl>
  <AlterBidPerm>Yes</AlterBidPerm>
 </PrjInfo>
 <Award>
  <DP>83</DP>
  <AwardInfo>
   <Cur>EUR</Cur>
   <CurLbl>Euro</CurLbl>
  </AwardInfo>
  <OWN>
   <Address>
    <Name1/>
    <PCode/>
   </Address>
  </OWN>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Deckblatt</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:12pt;Color:rgb(0,0,0);">L E I S T U N G S B E S C H R E I B U N G</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:12pt;Color:rgb(0,0,0);">Los 48 - Photovoltaikanlagen</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bauvorhaben:</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                             </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Projekt-/ Objektnummer 287-JKU</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Gemeinschaftsschule </span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Kulturanum Neu Gestimmt</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Schule und Sporthalle</span>
     <br/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Erlanger Allee 151, 07747 Jena </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auftraggeber: </span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                            </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Kommunale Immobilien Jena</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Paradiesstraße 6</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                                   </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">07743 Jena</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:70.60mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Gewerk:</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                                      </span>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Photovoltaikanlagen</span>
    </p>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:63pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <page/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Baustellenbeschreibung</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:11pt;Color:rgb(0,0,0);">Allgemeine Vorbemerkungen zum Leistungsverzeichnis</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Kommunale Immobilien Jena plant in der Erlanger Allee in Jena die Errichtung eines Schulkomplexes, bestehend aus Schule und Sporthalle (Kulturanum).</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die in den folgenden Vorbemerkungen aufgeführten Punkte sind bei der Kalkulation zu beachten und in die Einheitspreise einzukalkulieren.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Allgemeine Technische Vertragsbedingungen für Bauleistungen (ATV) gemäß VOB Teil C DIN 18 299 (Die Nummerierung ist sinngemäß DIN 18 299 entnommen.)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">0.1 Angaben zur Baustelle</span>
    </p>
    <p style="text-align:left;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.1. Lage der Baustelle</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Baugelände des Vorhabens liegt an der Erlanger Allee Nr. 151, an der östlichen Grenze der Stadt Jena, Ortsteil Lobeda. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Baugrundstück grenzt im Nordwesten an das Wohngebiet Jena-Lobeda an, im Norden an Vegetationsflächen und im Osten und Süden an öffentliche Verkehrsflächen. Im Westen benachbart sind Grünflächen sowie ein erhöhter Gleisauslauf einer Endhaltestelle Straßenbahn</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Grundstück hat eine starke Hanglage, von Norden nach Süden abfallend mit insgesamt mehr als 21 m Höhenunterschied (ca. 190 bis 212 m ü NHN). </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:11pt;Color:rgb(0,0,0);">0.1.3. Angaben zum Gebäude </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das vorhandene Schulgebäude (ohne laufenden Schulbetrieb) ist ein Typenschulbau aus dem letzten Jahrzehnt der DDR-Zeit. Es befindet sich auf einem Plateau in der westlichen Grundstückshälfte. Westlich, südlich und östlich des Gebäudes liegen Schulhofflächen. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Eine freistehende Einfeld-Sporthalle wird in Vorbereitung der Baumaßnahme abgebrochen., ebenfalls ein Nordöstlich schließen in diesem Bereich frühere Sportfreiflächen an.  </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">In der Anlage zur Angebotsaufforderung sind die Geschossgrundrisse zur allgemeinen Übersicht dargestellt. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">In der Angebotsaufforderung sind die Gebäude des Bauvorhabens wie folgt bezeichnet:</span>
     <br/>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Teilobjekt Schule </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Bestands-Schulgebäude</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Schulgebäude ist ein Schulbau des Typus Gera 72 aus den 1970er Jahren. Er wurde weitest gehend in Stahlbeton-Fertigteilbauweise errichtet. Das Bestandsgebäude besteht aus 3 Gebäudeflügeln, die in einer H-förmigen Grundrisskontur angeordnet sind. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der hangseitige Nordflügel ist ein nicht unterkellerter gedrungen kubischer 4-Geschosser (ehemals Fachraumtrakt). Mit dem untersten Geschoss ist er an der Nordseite in den Hang gesetzt, an seiner Südseite ist dieses ebenerdig. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der straßenseitige Südflügel ist ein schmaler, länglicher Baukörper (ehemals Klassenraumtrakt). </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Beide Teile werden auf allen Geschossen durch den &#x22;Verbindungsbau zusammengebracht.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die beiden letzteren Gebäudeteile sind durch einen Kriechkeller unterlagert. Der südliche Klassenraumtrakt tritt aus dem Niveau des modellierten Geländes mit einem Sockel ca. 80cm heraus, welcher zur Kriechkellerebene gehört. Darüber bestehen die Geschosse Hofgeschoss (= großenteils ebenerdiges Sockelgeschoss), Erdgeschoss, 1. und 2. Obergeschoss.  </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Schulneubau und Mensaanbau</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der schmale Südflügel des bestehenden Schulgebäudes wird auf der Südseite auf ganzer Gebäudelänge und in allen Geschossebenen mit einem Anbau ergänzt. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Dieser Anbau hat eine Tiefe von ca. 10m. Damit hat der Flügel dann neu Gesamtabmaße von 18x59m statt zuvor 8x59m. Der Anbau ermöglicht die Neueinordnung eines Flurs, benötigter zusätzlicher Unterrichtsräume sowie die Neuorganisation der vertikalen Erschließung (Treppenhäuser und Aufzug). </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Aula/Mensa wird als Neubau auf der Ebene des ebenerdigen Hofgeschosses westlich am Nordflügel plaziert. Mit Grundabmaßen von ca. 36x18m wird der eingeschossige Baukörper der Mensa an der Nordseite -wie der anschließende Bestandsflügel- in den Hang hineingesetzt. An seiner Südseite öffnet er sich ebenerdig mit seiner Fassade zum Eingangshof. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Mensaanbau hat eine geplante Grundfläche von 630m².</span>
     <br/>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Abmessungen: </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Schulgebäude</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Nordriegel - ehemaliger Fachraumtrakt 15 x 31m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Südriegel - ehemaliger Klassenraumtrakt 59 x 8m </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Anbau an Klassenraumtrakt  59 x 10 m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Verbinder 11x8m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Geschosshöhen i.M. 3,30m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Höhe FB 2. OG über Gelände - durchschnittlich 9,40m.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Bruttogrundfläche von 1.630m²</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Mensa</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Mensagebäude 32,5 x 17,7 m, Höhe (bis Attika) 6,20 m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:3.90mm 8.90mm 14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Anschluss an &#x22;Fachraumtrakt&#x22; 3,50 x 13,50 m, Höhe 4,40 m</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">BGF (R) Schulbaukörper und Mensaanbau 7091m² </span>
     <br/>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Teilobjekt Sporthalle</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die geplante Sporthalle ist als Ersatzneubau freistehend separat östlich des Klassenraumtraktes vorgesehen. Mit Grundabmaßen von 30,50 x 42,00m soll sie in etwa 20,5m östlicher Entfernung von der Schule als Solitär in die Freianlagen eingebettet werden. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Halle ist baukörperlich gegliedert in den höheren Hallenbaukörper mit dem Sportraumvolumen und eine niedrigeren Nebenraumflügel. Im höheren Hallenbaukörper sind östlich auch die Geräteraumflächen und die technischen Funktionsflächen für die Lüftungsanlagen übereinander in zwei Ebenen integriert.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Sporthalle besitzt eine geplante Bruttogrundfläche von 1330m² (R).</span>
     <br/>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.4. Verkehrsverhältnisse auf der Baustelle</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Baufeld ist über die Erlanger Allee erreichbar. Die Zufahrtsbreiten und Straßenradien sind beschränkt. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es besteht eine Grundstückszufahrt des Schulstandorts am östlichen Rand des Geländes von einer seitlichen Stichstraße der Erlanger Allee auf dem zu Zöllnitz gehörenden Flurstück 703/1. Diese Grundstückszufahrt muss auch zukünftig weiter genutzt werden.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Eine zweite Baustellenzufahrt von der Erlanger Allee von Südwesten wird eingerichtet. Es ist einzukalkulieren, dass phasenweise wegen parallel laufender Arbeiten anderer Gewerke nur eine der Zufahrten nutzbar ist.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Baustellenzufahrt wird durch den Auftraggeber beantragt. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Entwurf für den Baustelleneinrichtungsplan liegt den Ausschreibungsunterlagen bei und bildet die Grundlage für den BE-Plan des Auftragnehmers. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Werden für Transporte im Zusammenhang mit den Leistungen der vorliegenden Ausschreibungsunterlagen weitere Verkehrseinschränkungen bzw. Verkehrsrechtliche Anordnungen und Sondernutzungen notwendig, sind diese durch den Auftragnehmer in Eigenverantwortung zur Genehmigung zu beantragen und diese zu erwirken. Wenn in der Leistungsbeschreibung nicht als separate Position aufgeführt, ist dieses einschließlich der Gebühren in die Einheitspreise einzukalkulieren. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die angrenzenden öffentlichen Zufahrtsstraßen sind von Verschmutzungen und Verunreinigungen durch den Baustellenbetrieb freizuhalten, ggf. erforderliche Reinigungsarbeiten, die auf Verschmutzungen durch den Auftragnehmer zurückzuführen sind, sind durch den Auftragnehmer unverzüglich, d.h. am Tag der Verschmutzung und unaufgefordert zu veranlassen und werden nicht gesondert vergütet. Kommt der Auftragnehmer dieser Verpflichtung nicht nach, ist der Auftraggeber berechtigt, die Reinigung auf Kosten des Auftragnehmers durchführen zu lassen. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Sofern die Verschmutzungen der öffentlichen Straßenflächen nicht klar einem Verursacher zugeordnet werden können, ist der Auftraggeber berechtigt, eine Reinigung durchführen zu lassen und die dafür entstehenden Kosten auf mehrere Auftragnehmer entsprechend deren Baustellenanwesenheit und Bautätigkeiten zu verteilen.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.5 Für den Verkehr freizuhaltende Flächen: </span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Angaben sind dem den Vergabeunterlagen beigefügten Baustellen-Einrichtungsplan zu entnehmen.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Alle Zufahrtsbereiche, insbesondere für Feuerwehr und Rettungsfahrzeuge auf der Baustelle sind ständig freizuhalten. Darauf ist insbesondere bei der Baustelleneinrichtung und der Materialanlieferung zu achten.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.7. Anschlüsse </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Baustromanschluss und Bauwasseranschluss werden in ausreichender Dimension vom AG zur Verfügung gestellt. Abrechnung siehe Vertragsbedingungen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auf der Baustelle werden folgende Anschlüsse hergestellt und vorgehalten: </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- 1 Bauwasserhauptverteiler</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Baustromversorgung</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- 1x Krananschluss </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- 1x Baustromhauptverteiler </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Baustromverteiler pro Geschoss</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">nach Baufortschritt (nach Information an die Bauüberwachung 5 Werktage Vorlauf) </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Baustellenbeleuchtung steht nur als aus arbeitsschutzrechtlicher Sicht erforderliche Grundbeleuchtung der Verkehrswege zur Verfügung. Weitere notwendige Arbeitsplatzbeleuchtung ist durch den AN zu stellen, die Kosten sind bei der Kalkulation zu berücksichtigen. Alle Leuchtmittel sind abends auszuschalten.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Ein Telefon für Notrufe ist von jedem Auftragnehmer selbst zu stellen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.8 Lagerplätze/Sanitäreinr./Wege/Straßen </span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auf der Baustelle werden folgende Elemente der Baustelleneinrichtung gestellt und vorgehalten: </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Toilettencontainer/Waschgelegenheiten</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Baustellenabsperrung und Baumschutz</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Baustellenallgemeinbeleuchtung</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auf dem Baugrundstück befinden sich als Lagerflächen nutzbare befestigte Flächen (ehemalige Schulhöfe). Darüber hinaus werden durch den AG keine gesicherten oder abgeschlossenen Aufenthaltsräume, Umkleidebereiche o.Ä. zur Verfügung gestellt. Es werden seitens des AG keine Flächenbefestigungen oder Baustraßen hergerichtet.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es ist insbesondere mit wechselnden Einschränkungen der Zufahrtsmöglichkeiten zu rechnen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AG wird vor Beginn der Bauausführung eine Beweisaufnahme durchführen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Lage der vorhandenen bzw. durch den AN zu ergänzenden Baustraßen geht aus dem beiliegenden BE-Plan-Entwurf hervor.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die geplanten Transport- und Montagetechnologien sind vor Ort zu prüfen einschließlich der erforderlichen Maßnahmen für BE-Flächen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Weitere ggf. erforderliche Lagerflächen sind durch den AN eigenverantwortlich herzurichten, zu unterhalten und nach Fertigstellung der Leistungen wieder in den Ursprungszustand zu versetzen. </span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Baustelle ist jederziet gegen unbefugtes Betreten zu sichern (Bauzaun geschlossen halten). Der AN hat dafür Sorge zu tragen, dass arbeitstäglich nach Feierabend die Baustelle verschlossen wird (Gebäudeausgänge, Bautüren bzw. Bauzauntor) und die Beleuchtung ausgeschaltet ist. </span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.9 Bodenverhältnisse/ Baugrund</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Baugrunduntersuchungen wurden für den Standort durchgeführt und liegen als geo- und abfalltechnischer Untersuchungsbericht vor.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.10 Grundwasser</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">In den während der Baugrunduntersuchung durchgeführten Kern- und Kleinrammbohrungen wurde kein Zutritt von Schicht./Grundwasser festgestellt.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.13. Lärmschutz</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Ruhestörende Arbeiten zwischen 20.00 und 7.00 Uhr sind zu auszuschließen. Die Festlegungen der &#x22;Allgemeinen Verwaltungsvorschrift zum Schutz gegen Baulärm&#x22; sind einzuhalten.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Abweichende Arbeitszeiten hat der AN mit der Ordnungsbehörde, der örtlichen Bauüberwachung und dem Nutzer abzustimmen. Etwaige Gebühren für Sondergenehmigungen trägt der AN ohne den AG zu belasten.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.14 Schutzmaßnahmen an Bauwerken, Bäumen, Verkehrsflächen u.ä.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Vor Beginn der Arbeiten sind das vorhandene Gelände und die anschließenden öffentlichen Bereiche gemeinsam mit dem Auftraggeber auf evtl. Besonderheiten und den Zustand zu begutachten. Darüber ist ein Protokoll zu führen und von beiden Seiten zu bestätigen. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Schutzmaßnahmen gegen Beschädigung oder Verschmutzung an angrenzenden Gebäuden oder Bauteilen sind rechtzeitig und eigenverantwortlich vor Ausführungsbeginn vorzunehmen, hierzu gehören auch die entsprechenden Bausicherungsmaßnahmen.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Werden an bestehenden Anlagen und Einrichtungen Schäden verursacht, z. B. an Straßenbelägen oder Bordsteinen der Zufahrtsstraßen, so ist der AN verpflichtet, diese unverzüglich auf eigene Kosten zu beseitigen.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.15. Versorgungsleitungen</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die erforderlichen Schachtscheine und Genehmigungen sind durch den AN selbstständig bei der zuständigen Behörde einzuholen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Im Bereich der Baustelle in Betrieb bleibende bzw. neu errichtete Ver- und Entsorgungsleitungen dürfen nicht beschädigt werden und sind gegebenenfalls zu sichern. Der Auftragnehmer hat für den Schutz der Zuführungen von Kabeln, Leitungen, Kanälen und Einrichtungen während der Arbeiten zu sorgen. Er haftet für sämtliche, durch die Unterlassung, eventuell entstehende Schäden. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.17. Kampfmittel</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bei begründetem Verdacht ist die Bauüberwachung bzw. der AG zu informieren.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.18 Gegebenenfalls gemäß der Baustellenverordnung getroffene Maßnahmen:</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Auftraggeber hat einen Sicherheits- und Gesundheitsschutzkoordinator gemäß Baustellenverordnung (BaustellV) beauftragt. Dies entbindet den Auftragnehmer nicht von seiner Verantwortung zur Erfüllung der Arbeitsschutzpflichten (BaustellV § 5.3) nach dem Arbeitsschutzgesetz, Betriebssicherheitsverordnung, Arbeitssicherheitsgesetz und dem Regelwerk der Berufsgenossenschaften. </span>
     <br/>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.20 Art und Umfang von Schadstoffbelastungen</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Im Rahmen der Voruntersuchungen wurde ein Gutachten &#x22;Abfalltechnischer Untersuchungsbericht - Gebäudeschadstoffkataster&#x22; erstellt.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.22 Vorarbeiten</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Im Vorfeld der Rohbauarbeiten erfolgt der Abbruch der Turnhalle sowie nichtkonstruktive Abbrucharbeiten im Bestandsschulgebäude und Außenbereich. </span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.23 Arbeiten anderer Unternehmer auf der Baustelle</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es muss damit gerechnet werden, dass parallel zu den Leistungen des AN auf dem Baugelände, insbesondere am Standort Schulbaustelle oder im Bauwerk auch Arbeiten durch andere Unternehmer durchgeführt werden müssen. Diese Arbeiten sind zu dulden und von Behinderungen freizuhalten. Sie berechtigen nicht zu Terminverlängerungen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Zusammenwirken mit den anderen Unternehmern ist in Zusammenarbeit mit der örtlichen Bauüberwachung abzustimmen.</span>
     <br/>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.1.24 Vermessung   </span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Durch den AG wird ein Vermesser beauftragt, der einen Höhenfestpunkt und je Neubau-Gebäudeflügel zwei Achsen einmisst und absteckt. Die weitere Grobabsteckung und die Einmessung der Hauptachsen der Gebäude, Meterrisse und alle weiteren Vermessungsleistungen, die zur Erstellung der eigenen Leistung erforderlich sind, sind durch den AN auszuführen, die benötigten vermessungstechnischen Angaben hat der AN selbst zu erbringen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die verbindlichen Höhenmarkierungen und -punkte sind durch den AN in Zusammenarbeit mit der Bauüberwachung anzulegen.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Evtl. Unstimmigkeiten sind dem AG und den planenden Ingenieuren sofort zur Kenntnis zu geben, damit umgehend eine für alle Beteiligten verbindliche Klarstellung herbeigeführt werden kann. Dies ist in den Einheitspreis einzukalkulieren und wird nicht separat vergütet.</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">0.2 Angaben zur Ausführung</span>
    </p>
    <p style="margin-right:6pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.2.1 Arbeitsabschnitte, Arbeitsunterbrechungen</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Gebäude soll in einem Zug errichtet werden.</span>
     <br/>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Planungsvorbereitung nach Auftragserteilung / Zeitplan</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Nach Auftragsvergabe durch den Auftraggeber werden dem AN vor dem geplanten Baubeginn freigegebene Ausführungspläne einschließlich (digital) ausgegeben. Die Arbeitsvorbereitung des Auftragnehmers ist dementsprechend anzupassen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Sollten darüber hinaus Planunterlagen erforderlich sein, so ist dies der Bauüberwachung des Auftraggebers mit entsprechendem Planungsvorlauf für die Erstellung dieser Unterlagen anzuzeigen. Grundsätzlich sind entstehende Behinderungen aus Unkenntnis der Planung auszuschließen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Eventuell wird im Zuge der Bauabwicklung die Ausführungsplanung an die Bedingungen vor Ort angepasst (Index). Die Planausgabe seitens des Auftraggebers erfolgt wie bisher beschrieben.</span>
     <br/>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Baustelle ist ausreichend zu besetzen. Mit der Abgabe des Angebotes hat der AN seine Leistungsfähigkeit diesbezüglich nachzuweisen (geplante Besetzung der Baustelle, durchschnittliche Anzahl AK vor Ort).</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Baustellen-Einrichtungsplan und Bauablaufplan</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AN legt innerhalb von 15 Werktagen nach Auftragserteilung einen detaillierten Baustelleneinrichtungsplan auf der Grundlage des BE-Planentwurfes des AG vor. Dieser ist entsprechend Baufortschritt vom AN zu aktualisieren.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Weiterhin ist innerhalb von 15 Werktagen nach Auftragserteilung ein detaillierter Bauablaufplan für die im nachfolgenden LV beschriebenen Leistungen auf der Grundlage der Terminvorgaben des AG vorzulegen und mit der Bauüberwachung abzustimmen.</span>
     <br/>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.2.6 Besondere Anforderungen Entsorgung</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bauabfälle sind strikt zu trennen nach mineralischen Stoffen, nicht mineralischen Stoffen und schadstoffhaltigen Bauabfällen. Zur Einhaltung dieser Trennpflicht sind auf der Baustelle in Abstimmung mit der Bauüberwachung entsprechende Voraussetzungen zu schaffen, wie eine ausreichende Anzahl von Sammelbehältern und Vorhalteflächen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Verwertbare Bestandteile von Bauabfällen, Straßenaufbruch und Bodenaushub sind ei¿dener Verwertung zuzuführen. Bauabfälle sind zugelassenen Entsorgungsanlagen zuzuführen, vgl. entsprechende Regelungen der Gewerbeabfallverordnung des Bundes.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.2.7. Gerüste, Hebezeuge, Aufzüge, Lagerräume u.ä.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Alle Leistungen zur Baustelleneinrichtung, die nicht im nachfolgenden Leistungsverzeichnis gesondert beschrieben und für die Ausführung der ausgeschriebenen Leistung erforderlich sind, sind in die Einheitspreise einzukalkulieren. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Notwendige Einsätze von Kränen, Autodrehkränen und anderen Hebezeugen sind einzurechnen, ebenso wie die Leistungen zu deren Auf- und Abbau sowie Herrichten und Rückbau der Standplätze / Aufstellfläche.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Hinweis: Im BE-Plan-Entwurf sind für den Kranstandort entsprechende Vorschläge dargestellt. </span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Längenorientierte Arbeits- und Schutzgerüste werden durch das Gewerk Gerüstbau bereit gestellt (siehe Pkt. 0.4. der Vorbemerkungen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Gerüstbauanforderungen für die vom Gewerk Gerüstbau zu stellenden Gerüste sind mindestens 10 Werktage vor Bedarf anzumelden. </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Auftragnehmer (AN) hat die nach Arbeitsstättenverordnung und Arbeitsstättenrichtlinie geforderten Maßnahmen für seine Beschäftigten selbst zu erbringen (z.B. Aufenthaltscontainer). </span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Vom AN ist ein Ersthelfer zu benennen, dieser muss ständig (bei entsprechender Firmenanwesenheit) auf der Baustelle anwesend sein.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">0.3 Allgemeine Hinweise</span>
    </p>
    <p style="text-align:left;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.3.1. Kalkulationshinweise</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für die in diesem Leistungsverzeichnis aufgeführten Arbeiten sind alle Transportkosten sowie alle Aufwendungen, die für den Transport und den Einbau (z.B. Hebezeuge, Abstützungen, Unterkeilungen, Montagehilfsmittel usw.) benötigt werden, einzukalkulieren, soweit im LV-Text nichts anderes beschrieben ist.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Zwischenlagerkosten werden nicht gesondert vergütet.</span>
    </p>
    <p style="margin-right:3pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Aufmaße</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Vor Rechnungslegung ist eine Aufmaßeinreichung bzw. ein Aufmaß mit der Objektüberwachung des Auftraggebers erforderlich.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Aufmaße sind leserlich und eindeutig sowie positionsbezogen (Angabe LV - Pos.) zu erstellen. Sind Positionen unklar oder nicht leserlich, können diese in der Rechnungsprüfung nicht berücksichtigt werden. Folgende Genauigkeitsregeln sind zu beachten: </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Abrechnung nach m3 - max. 3 Nachkommastellen</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Abrechnung nach m2 bzw. lfdm. max. 2 Nachkommastellen</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auf den Aufmaßblättern sind das Bauvorhaben und die ausführende Firma anzugeben. </span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Aufmaßblätter sind fortlaufend zu nummerieren. Bei kumulierten Aufmaßen ist der Leistungszuwachs deutlich zu kennzeichnen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Den Aufmaßblättern sind ausreichend Aufmaßzeichnungen beizufügen, die Zuordnung zu den Orten muss eindeutig und nachvollziehbar sein. Alle Aufmaßblätter sind vom Aufsteller zu unterschreiben. Rechnungen sind generell die Originalaufmaßblätter beizulegen. </span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.3.2. Zusammenarbeit</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AN hat für die Dauer des Vertrages einen fachlich befähigten Projektleiter zu bestellen, der berechtigt ist, selbstständig und jederzeit Entscheidungen für den AN zu treffen. Der Projektleiter ist dem AG und der örtlichen Bauüberwachung bei Vertragsabschluss schriftlich zu benennen. Jeder Wechsel in der Person des Projektleiters ist dem AG und der örtlichen Bauüberwachung unverzüglich schriftlich anzuzeigen.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Ein Polier oder Vorarbeiter, der fachlich und persönlich geeignet und deutschsprachig ist, muss während der Arbeitszeit auf der Baustelle anwesend sein.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Bauüberwachung wird in periodischen Abständen (mind. 1x wöchentlich) Baubesprechungen einberufen. Der Firmenbauleiter oder sein Stellvertreter haben an diesen Besprechungen teilzunehmen. Unentschuldigte Nichtteilnahme an Besprechungen berechtigt den Auftragnehmer nicht, koordinative oder technische Entscheidungen, welche in der Besprechung getroffen wurden, zu beeinspruchen oder daraus terminliche oder vertragliche Konsequenzen zu formulieren. </span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Sicherung und Bewachung aller Leistungen und Materialien des vom Auftragnehmer zu erstellenden Werkes obliegt dem Auftragnehmer. Der Auftragnehmer ist für die Verwahrung und Unterbringung seiner Werkzeuge, Materialien, Geräte, Bau- und Hilfsstoffe selbst verantwortlich. Schadensersatzansprüche gegen den Auftraggeber sind ausgeschlossen.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Auftragnehmer hat sicherzustellen, dass die Objektüberwachung des Auftraggebers jederzeit den ungehinderten Zutritt zur Baustelle hat und über alle relevanten technischen Angelegenheiten informiert wird. Die Objektüberwachung ist zu Weisungen gegenüber dem Auftragnehmer berechtigt, jedoch nicht zu Vertragsänderungen.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Reinigung der Arbeitsbereiche ist eine Nebenleistung nach VOB, Teil B, auf die ausdrücklich hingewiesen wird. Sollte der Auftragnehmer seiner Reinigungspflicht auch trotz Aufforderung durch die Bauüberwachung des Auftraggebers nicht nachkommen, wird eine Reinigung durch Dritte durch dessen Bauüberwachung veranlasst, und die Kosten werden auf den AN umgelegt.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Auf der Baustelle herrscht striktes Alkoholverbot, innerhalb der Gebäude besteht generell Rauchverbot.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.3.3. Normen und Vorschriften</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die für das jeweilige Gewerk bestehenden Normen und Richtlinien sind anzuwenden.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Qualitätsangaben und Güteanforderungen sind Mindestangaben. Sie gelten als Vertragsbestandteil und dürfen bei der Ausführung ohne Genehmigung des Auftraggebers nicht gemindert werden. Änderungen während der Bauzeit gehen zu Lasten des Auftragnehmers.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Soweit in der Leistungsbeschreibung auf Technische Spezifikationen, z.B. nationale Normen, mit denen Europäische  Normen umgesetzt werden, europäisch technische Bewertungen, gemeinsame technische Spezifikationen,  Internationale Normen, Bezug genommen wird, werden auch ohne den ausdrücklichen Zusatz: &#x22;oder gleichwertig&#x22; immer gleichwertige Technische Spezifikationen in Bezug genommen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">0.3.4 Sonstige Leistungen</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Ein Exemplar der Planunterlagen und das Leistungsverzeichnis sind auf der Baustelle aufzubewahren.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Auftragnehmer hat dem Auftraggeber in geeigneter Form über den Personal- und Geräteeinsatz, Materiallieferungen, die Arbeitsleistungen, den Arbeitsfortschritt und über besondere Vorkommnisse aktuell zu berichten. Hierzu zählen auch Begehungen mit der Berufsgenossenschaft und dem Gewerbeaufsichtsamt. Dem Auftraggeber sind alle Unfälle, Erste Hilfe - Fälle und Schadensfälle unverzüglich mitzuteilen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Das Bautagebuch ist der Bauüberwachung wöchentlich unaufgefordert vorzulegen. In den Bautagesberichten sind u.a. aufzunehmen:</span>
    </p>
    <ul style="margin-left:14pt;font-family:symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Name der Firma und Baustelle</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">fortlaufende Nummerierung</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Datum</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Temperatur um 7.00 Uhr (morgens), windgeschützte Stelle</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Witterungsverhältnisse</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Anzahl der Arbeitnehmer nach Lohngruppen/  Qualifikation</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Maschineneinsatz</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">ausgeführte Leistung mit Ortsangabe (Geschoss / Achsen) und Bezug zum betroffenen Vorgang (Vorgangsnummer /  Planbezeichnung)</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">besondere Maßnahmen und Vorkommnisse</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Anweisungen der Bauüberwachung und des SiGe-  Koordinators</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Unterschrift des Bauleiters des Auftragnehmer</span>
     </li>
    </ul>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <ul style="font-family:symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Bestandsunterlagen zum Nachweis </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Seitens Auftraggeber/Nutzer werden inhaltliche und formale Vorgaben an die Gewerkedokumentation gestellt, welche nachfolgend erläutert werden. </span>
      <br/>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Sämtliche Unterlagen sind durch den AN spätestens 10 Werktage vor Abnahme digital und auf Anforderung zusätzlich auf Papier (1fach) zu übergeben.</span>
      <br/>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Nachfolgende Übersicht veranschaulicht die geforderte Gliederung und stellt exemplarisch den Umfang der geforderten Dokumentation dar:</span>
      <br/>
     </li>
    </ul>
    <ul style="margin-left:14pt;font-family:symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Deckblatt mit folgenden Angaben: Bauvorhaben, Gewerk, Leistungsinhalt, Bauzeit, ausführendes Unternehmen mit  Ansprechpartner und Kontaktdaten</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Fachbauleitererklärung, Fachunternehmererklärung </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Verzeichnis Nachauftragnehmer </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bautagebücher, Abnahmebescheinigungen sonstige Bescheinigungen</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Materialnachweise mit eindeutigen Produktbezeichnungen, Produktdatenblätter, Konformitätserklärungen, Übereinstimmungserklärungen (inkl. Zuordnung zu den Positionen des Leistungsverzeichnisses)</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Prüfberichte der verwendeten Baumaterialien, Angaben zur produktbezogenen Prüfung, Überwachungsprotokolle</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Wartungs- und Pflegehinweise, Zulassungen, Lieferscheine, Geräteverzeichnisse, Bedienungsanweisungen, Technische Dokumentation, Fotodokumentation des AN,   Revisionszeichnungen, Entsorgungsnachweise, sonstige erforderliche Nachweise,</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Zertifikate und Zulassungen</span>
     </li>
    </ul>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Die Erstellung der Bestandsunterlagen wird nicht gesondert vergütet und ist in die Einheitspreise einzukalkulieren.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">0.4 Arbeitshöhen, Gerüststellung</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Von folgenden lichten Rohbauraumhöhen ist bei der Kalkulation in den einzelnen Geschossen auszugehen:</span>
     <br/>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Schulgebäude (Bestand und Neubau)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitshöhe üOK Decke HG</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 3,20 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitshöhe üOK Decke EG</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 3,20 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitshöhe üOK Decke 1.OG</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 3,20 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitshöhe üOK Decke 2.OG   </span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 3,20 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:11pt;Color:rgb(0,0,0);">Mensa</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitshöhe üOK Decke EG</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 5,20 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-style:italic;font-size:11pt;Color:rgb(0,0,0);">Sporthalle</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm 50.00mm 69.90mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">hoher Hallenteil</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 9,00 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:10.00mm 30.00mm 50.00mm 69.90mm;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">niedriger Hallenteil</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                  </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">max. 4,00 m</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:11pt;Color:rgb(0,0,0);">Durch das Gewerk Gerüstbau werden folgende Gerüste errichtet:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Längenorientierte Arbeits- und Schutzgerüste der Lastklasse 3 für die Fassadeneinrüstung</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Längenorientierte Arbeits- und Schutzgerüste der Lastklasse 2 an den Innen¿tewänden der Sporthalle (bis UK Binder)</span>
    </p>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Leistungsbezogene Beschreibung der Photovoltaikanlage</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Leistungsbezogene Beschreibung der Photovoltaikanlage</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Folgende Dächer sind des Objekte Kulturanum sind mit einer Photovoltaikanlage auszurüsten</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Sporthalle Nebentraktdach</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel (Bereich Bestand)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">- Mensaanbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">nachfolgender Dachaufbau ist im Rahmen der erweiterten Werkplanung bei der Angebotsabgabe bei der Auswahl der UK zu berücksichtigen</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Sporthalle Hauptdach Dachaufbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">10mm Dachabdichtung Bitumenbahnen 2lagig</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">tw. Gefälledämmkeile</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">200mm Dämmung Mineralfaser WLS 040</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">5mm Dampfsperre Bitumenbahn (durchtrittsicher)</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">165mm Stahltrapezblechdeckung Stat.-Pos. DA-01</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">d=1mm, Positivlage, m. Akustiklochung,</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">mit Sickenfüller MiWo</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Sporthalle Nebentraktdach Dachaufbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">10mm Dachabdichtung Bitumenbahnen 2lagig</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">20-160mm Gefälledämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">120mm Grunddämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">5mm Dampfsperre Bitumenbahn 1-lagig</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">200mm Stahlbetondecke</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Bestandsschule Nordflügel Dachaufbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bitumenabdichtung 2lagig 10mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">20-220mm Gefälledämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">120mm Grunddämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Dampfsperre bitum. 5mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">zem. Ausgleichsestrich ca. 50mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">bestehende Stb.-Hohlplattendecken 250mm</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Bestandsschule Südflügel Dachaufbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bitumenabdichtung 2lagig 10mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">20-170mm Gefälledämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">160mm Grunddämmung EPS WLS 032</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Dampfsperre bitum. 5mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">zem. Ausgleichsestrich ca. 50mm</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">bestehende Stb.-Hohlplattendecken 250mm</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;text-decoration:underline;font-size:11pt;Color:rgb(0,0,0);">Mensaanbau Dachaufbau</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Dachaufbau Mensaanbau hoher Teil:</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">bereichsweise Plattenbeschwerung der Dachhaut auf Bautenschutzmatte</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">10mm Dachabdichtung Bitumenbahnen 2lagig</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">20-180mm Gefälledämmung Mineralfaser WLS040 (Brandschutzanforderung)</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">120 mm Grunddämmung Mineralfaser</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">5mm Dampfsperre Bitumenbahn 1lagig</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es sind durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % geplant.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die zu errichtende Photovoltaikanlage (kurz PV-Anlage) soll im Netzparallelbetrieb mit Überschusseinspeisung arbeiten.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für jede der o.g. Dachflächen ist je ein dreiphasiger Wechselrichter mit einer passenden AC- Nennleistung  passend zu den Modulleistungen, geplant. Die Anordnung der WR erfolgt dabei auf den jeweiligen Dächern mittels eigener Aufständerung und Schleppdach. An den selben Standorten werden auch die DC-seitigen Überspannungsschutzeinrichtungen angebracht.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);"/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Trennungsabstände zum Blitzschutz sind einzuhalten. Die Einbindung in die innere Blitzschutzanlage erfolgt bauseits über Überspannungsschutzableiter Typ 1/2.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die DC-Kabel sollen entsprechend Verlegeplan nach Polung getrennt in Kabelschutzrohren/ feuerTrassen  verleg. Die Verkehrswege werden zusätzlich mit begehbarens Abdeckungen ausgestattet.</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Verlegung der AC- und Datenkabel efolgt bauseits über die vorhandenen Steigepunkte/Steigeleitern durch das Gebäude zum Hausanschlusspunkt (NSHV/ TST- Raum) .</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Seitens des PV Anlagenerrichters muss, auf Basis der übergebenen Planung, die erweiterte Werkplanung für die UK auf Basis des gewählten Systems und der o.g Dachaufbauten erstellt werden.</span>
    </p>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Anschluss aller Komponenten an den Potentialausgleich ist ebenfalls Bestandteil der zu erbringenden Leistungen. Der Aufbau der Kommunikation und Anlagenüberwachung erfolgt durch den AN, der erforderliche Netz-Zugang (TCP-IP)  wird bauseits gestellt.</span>
    </p>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Alle angebotenen Wechselrichten müssen neben einem TCP-IP Wartungsport auch einen freigeschaltenen kostenfreien  TCP-IP Webzugang (html) mit allen Erzeugungsdaten bereitstellen.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Inbetriebnahme der gesamten Anlage und die Einweisung in den Betrieb für den</span>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Betreiber erfolgt durch den Auftragnehmer.</span>
    </p>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für die Gebäudeautomation (GA) ist für den Wechselrichter ein potentialfreier Kontakt als Sammelstörmeldung zur Verfügung zu stellen. Der Kontkat ist dem Gewerk Gebäudeautomation am Wechselrichter mit Datenblatt zu übergeben.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die PV-Anlage ist schlüsselfertig, funktions- und netzanschlussbereit unter Beachtung der technischen Anschlussbedingungen des zuständigen Netzbetreibers und den allgemein anerkannten Regeln der Technik zu errichten. Sie muss zum Zeitpunkt der Zuschaltung den in Deutschland geltenden Vorschriften entsprechen. Zuständiger Netzbetreiber sind die Stadtwerke Jena.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);"/>
    </p>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Vorschriften und Angebotsgrundlagen</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Vorschriften und Angebotsgrundlagen (speziell PV)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es gelten neben den zutreffenden brandschutztechnischen, gesetzlichen und ministeriellen Bestimmungen insbesondere:</span>
    </p>
    <ul style="text-indent:17pt;margin-left:18pt;margin-right:1pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">die jeweils gültigen gesetzlichen und behördlichen Vorschriften</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">die gültigen Bestimmungen des Verbandes Deutscher Elektrotechniker (VDE) und DIN-Normen</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">die Arbeitsschutz- und Unfallverhütungsvorschriften der zuständigen Berufsgenossenschaften</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">die arbeitsschutzrechtlichen und berufsgenossenschaftlichen Vorgaben und Bestimmungen für Arbeiten auf Dächern sind vom AN unbedingt einzuhalten. </span>
     </li>
    </ul>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Insbesondere ist auf eine genügende Absturzsicherung an den Gebäudekanten zu achten. </span>
    </p>
    <ul style="text-indent:17pt;margin-left:18pt;margin-right:1pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">DGUV A 1 - Allgemeine Vorschriften </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">DGUV A 3 - Elektrische Anlagen und Betriebsmittel</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">DGUV C 22 - Bauarbeiten (Persönliche Schutzausrüstungen gegen Absturz) </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Berufsgenossenschaftliche Regeln für die Sicherheit und Gesundheit bei der Arbeit BGR 203 (Dacharbeiten) und die DIN EN 516 Einrichtungen zum Betreten des Dachs</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Arbeitskleidung und Arbeitsschutzbestimmungen gemäß den Vorschriften der Berufsgenossenschaft</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Verordnung über Allgemeine Bedingungen für den Netzanschluss und dessen Nutzung für die Elektrizitätsversorgung in Niederspannung (Niederspannungsanschlussverordnung - NAV)</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Bestimmungen und Richtlinien des für Jena zuständigen Netzbetreibers, insbesondere die &#x22;Technischen Anschlußbedingungen&#x22; (TAB) für den Parallelbetrieb von PV-Eigenerzeugungsanlagen mit dem Niederspannungsnetz Netzbetreibers.</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">VDE AR-N 4105</span>
     </li>
    </ul>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Übergabe</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Es werden folgende Bedingungen zugrunde gelegt:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Anlage muss in absolut betriebsfertigem Zustand übergeben werden.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Anlage muss durch den örtlichen Energieversorger abgenommen sein.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Erfüllung der Brandschutzvorschriften und Schallschutzforderungen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die vom AG benannte Person muss in die Anlage eingewiesen sein.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Funktioniert die Anlage nicht einwandfrei oder werden die garantierten Leistungen nicht erreicht, hat der AN die notwendigen Verbesserungen zu seinen Lasten vorzunehmen. Für die Beseitigung der bei der Abnahme erhobenen Beanstandungen wird eine angemessene Frist eingeräumt, die nicht überschritten werden darf.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AG behält sich vor, einzelne Anlagenteile vor Fertigstellung des Gesamtprojektes durch Teilabnahme zu übernehmen, bzw. zu betreiben. Sollten weitere Teilabnahmen, Abnahmen und Nachabnahmen erforderlich werden, so sind diese mit den o.a. Betriebs- und Funktionsprüfungen, einschließlich Anfertigen der Protokolle auszuführen. Sämtliche Kosten, die dem AG und dessen Beauftragten durch zusätzliche Abnahmen bis zur mangelfreien Abnahme der Gesamtleistungen durch den Bauherrn entstehen, sind vom ausführenden Unternehmer zu tragen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Kennzeichnung der Anlage und ihrer Komponenten hat gemäß der Broschüre &#x22;Brandschutzgerechte Planung, Errichtung und Instandhaltung von PV-Anlagen&#x22; zu erfolgen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Liefer- und Leistungsumfang</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Gemäß VOB/C Lieferung aller Teile frei Baustelle und fertiger, betriebsbereiter Montage der Photovoltaikanlage.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Nebenleistungen gem. DIN 18299, DIN 18385</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Weiterhin sind folgende Leistungen für die Photovoltaikanlage zu erbringen:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">(in Einheitspreisen einkalkuliert)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <ul style="text-indent:17pt;margin-left:36pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Sämtliche Anlagenteile sind in den Potentialausgleich einzubeziehen. </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Dem Angebot ist ein Blockbild der projektierten Anlage beizulegen, aus dem die Aufteilung (Strings), die Beschaltung und die Anzahl der Anlagenkomponenten hervorgeht.</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Dokumentationen sind entsprechend DIN EN 62446 zu erstellen</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die maximal erlaubte Modultoleranz beträgt -0 und +3%.</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Anschließen an Befestigungen anderer Gewerke ist nur mit ausdrücklicher Zustimmung des AG gestattet. </span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Offene Anlagenteile, z.B. Rohrenden, sind bei jeder Montageunterbrechung durch geeignete Maßnahmen gegen Eindringen von Fremdteilen mit Sicherheit zu verschließen.</span>
      <br/>
     </li>
    </ul>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Abnahme</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für die Durchführung der Prüfung ist das erforderliche Personal vom Auftragnehmer kostenfrei zu stellen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die bei der Abnahme durch die Bauführung festgestellten Mängel werden dem Auftragnehmer schriftlich mitgeteilt, und sind innerhalb der gesetzten Fristen zu beseitigen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Abnahme- und Revisionsunterlagen werden je 3 fach erstellt und sind zusätzlich 1fach auf Datenträger (CD) mind. 2 Wochen vor Abnahme zu übergeben.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der Inhalt der digitalen Unterlagen muss vollständig den Unterlagen in Papierform entsprechen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die vorgegebene Ordnerstruktur der Bestandsdokumentation des Auftraggebers liegt dieser Auschreibung bei. </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Übergabe einer vollständigen Dokumentation ist ein wesentlicher Bestandteil der Leistung. Ohne vorliegende Dokumentation erfolgt keine Abnahme. Dazu gehört auch eine Einweisung in alle technischen und sicherheitsrelevanten Anlagen.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Transport </span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für den Transport und die Verbringung der Module auf das Dach stehen bauseits keine Leistungen zur Verfügung.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Bei Transporten im und am Gebäudes ist die vorhandene Bausubstanz so zu schützen, dass Beschädigungen bzw. Zerstörung ausgeschlossen sind.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Wird es während der Transporte erforderlich, vorhandene Absperrmaßnahmen zu demontieren, sind diese nach erfolgtem Transport gem. UVV unverzüglich, eigenverantwortlich und kostenfrei wiederherzustellen. </span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Wartung</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für die in der Leistungsbeschreibung beschriebenen Anlage ist vom Bieter ein Wartungsvertrag nach anliegendem Vertragsmuster des AG und in Anlehnung an das AMEV Vertragsmuster  anzubieten.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Termine</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Unter Beachtung der vom Auftraggeber vorgegebenen Termine (jedoch spätestens 4 Wochen nach Beauftragung) ist die komplette Werkplanung in 3facher Ausfertigung zu erstellen. Aus diesen Angaben müssen alle relevanten Angaben für die Fremdgewerke ersichtlich sein (ELT/ Bau/ Statik).</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Erst nach Genehmigung der Unterlagen durch den AG bzw. dessen Beauftragten kann die Bestellung der Module erfolgen, Genehmigung erfolgt kurzfristig.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Weitere Termine siehe BVB des AG</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Zum vertraglichen Fertigstellungstermin muss die mängelfreie Abnahme vollzogen sein.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Zeichnungen</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Zeichungen sind Bestandteil der Ausschreibung.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Die Planunterlagen können als Datei digital über die homepage des Auftraggebers bezogen werden.</span>
    </p>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:71pt;margin-right:3pt;text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Allgemeine Technische Vertragsbedingungen</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Allgemeine Technische Vertragsbedingungen</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Stoffe und Bauteile müssen DIN-, Güte und Maßbestimmungen entsprechen (VOB). </span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Stoffe und Bauteile, die nach den behördlichen Vorschriften einer Zulassung bedürfen, müssen</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">amtlich zugelassen sein. Stoffe und Bauteile, für welche weder DIN-Normen bestehen, noch eine amtliche Zulassung vorgeschrieben ist, dürfen nur mit Zustimmung des Auftraggebers (AG) verwendet werden.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Stoffe und Bauteile müssen dem Verwendungszweck entsprechend korrosionsgeschützt</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">sein. Für die Ausführung gelten ebenfalls die anwendbaren DIN- und EN-Normen, VDI/VDE-Richtlinien, Bestimmungen amtlicher Institutionen und behördlichen Vorschriften, sowie die anerkannten Regeln der Technik.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Stemm-, Fräs- und Bohrarbeiten am Bauwerk dürfen nur im Einvernehmen mit dem AG</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">durchgeführt werden. Baustoffe, die zerstörend auf Anlagenteile wirken können, dürfen</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">nicht verwendet werden. </span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">In jedem Fall ist die Koordination zwischen den einzelnen Gewerken rechtzeitig und lückenlos durchzuführen. Die eigenen Leistungen sind auch im Hinblick auf ergänzende Fremdleistungen auf zumutbare Durchführung zu konzipieren.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für die technische Anlage sind Demontagemöglichkeiten, leichte Bedienung und unkomplizierte Wartung vorzusehen.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Für Alternativangebote, anderer als in der Ausschreibung angegebene Bauteilkomponenten, deren Auslegung Berechnungen zugrunde liegen, und/oder deren Auslegung oder Einstellwerte einen Einfluss auf das Gesamtsystem haben, ist der rechnerische Nachweis vom AN zu erbringen bzw. auf die Nutzungsanforderungen auszulegen.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Leistungen, welche bei der Abnahme nicht überprüft werden können, sind entsprechend dem Baufortschritt einer Zwischenabnahme zu unterziehen. </span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AN hat die Anlage auf einwandfreie Funktion zu überprüfen. Sofern die Gesamtfunktion erst bei voller Nutzung oder Maximalbelastung festgestellt werden kann, wird diese Überprüfung bei der Abnahme ausgeklammert und nachvollzogen.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AN hat bei der Ausführungsbearbeitung wirtschaftliche Gesichtspunkte bei der Konstruktion und den Anlagenteilen vorrangig zu berücksichtigen. Etwaige Änderungsvorschläge sind einzureichen. Der AG kann vom AN den Nachweis einer wirtschaftlichen Auslegung vor oder während der Ausführungszeit verlangen. Stellt sich innerhalb der Gewährleistungsfrist heraus, dass der AN keine wirtschaftliche Lösung verwirklicht hat, so fallen ihm die Kosten für eine spätere vom Bauherrn veranlasste Änderung zur Last.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:11pt;Color:rgb(0,0,0);">Der AN gewährleistet, dass eine vom AG benannte Person so eingewiesen wird, dass ein einwandfreier Betrieb sichergestellt ist.</span>
    </p>
    <p style="margin-right:1pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <BoQ ID="DBBCAAAA">
   <BoQInfo>
    <Name>PV</Name>
    <LblBoQ>Los 48 PV- Photovoltaikanlage</LblBoQ>
    <Date>2025-10-27</Date>
    <OutlCompl>AllTxt</OutlCompl>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn>Titel</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Item</Type>
     <Length>3</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <NoUPComps>2</NoUPComps>
    <LblUPComp1>Material</LblUPComp1>
    <LblUPComp2>Lohn</LblUPComp2>
    <Ctlg>
     <CtlgID>DBABHLCI</CtlgID>
     <CtlgType>cost group DIN 276-1 2008-12</CtlgType>
     <CtlgName>DIN276-1_08</CtlgName>
    </Ctlg>
    <Ctlg>
     <CtlgID>DAGMHLCI</CtlgID>
     <CtlgType>cost group DIN 276-06</CtlgType>
     <CtlgName>DIN276_06</CtlgName>
    </Ctlg>
   </BoQInfo>
   <BoQBody>
    <BoQCtgy ID="DBBDAAAA" RNoPart="1">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>Baustellengemeinkosten</span>
      </p>
     </LblTx>
     <BoQBody>
      <Itemlist>
       <Item ID="DBBDAEHI" RNoPart="10">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einrichtung, Vorhalten und Räumung der Baustelle, Gestellung Werkzeuge, Materialtransporte auf dem Anlagengelände, Montageaufsicht und Montageversicherung.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Toiletten und Baustrom werden vom AG gestellt.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Baustelleneinrichtung</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBDAMLI" RNoPart="20">
        <Qty>5.000</Qty>
        <QtySplit>
         <Qty>5.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gerüste, Leitern</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Gerüste sind entsprechend den geltenden Unfallverhütungsvorrschriften auszuführen. Insbesondere der BGV A3.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die erforderliche Absturzsicherung muss für die Sicherung der Flachdächer (Flachdächer A2, B1.2- PV.Anlage) geeignet sein. </span>
             <br/>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die erforderliche Absturzsicherung muss für die Sicherung der Arbeiten auf dem Dach geeignet sein</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die entsprechenden notwendigen Höhen des Daches können den beiliegenden Schnitten entnommen werden.</span>
             <br/>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist besondere Sorgfalt erforderlich!</span>
            </p>
            <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es handelt sich um ein Flachach, </span>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschädigungen an Dachaufbau und Abdichtung sind zu vermeiden.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kosten für die Absturtzsicherung sind je Dach entsprechend zu kalkulieren:</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Mensaanbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Anbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
             <br/>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Absturzsicherung an den Gebäudekanten je Dach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBDBFHI" RNoPart="30">
        <Qty>5.000</Qty>
        <QtySplit>
         <Qty>5.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastenaufzug für die Ausführung der ausgeschriebenen Montagearbeiten:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">anfahren, aufbauen, vorhalten, umsetzen und wieder abbauen und abfahren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(notwendige Höhe siehe Angaben im Schnitt OK Dach)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastenaufzug für den Auf- / Abbau und den Materialtransport zu den Dachflächen sind in dieser Position enthalten. </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kosten für den Lastenaufzug sind je Dach entsprechend  zu Kalkulieren:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Mensaanbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Anbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Lastenaufzug</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
      </Itemlist>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="DBBEAAAA" RNoPart="2">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>Technische Bearbeitung</span>
      </p>
     </LblTx>
     <BoQBody>
      <Itemlist>
       <Item ID="DBBEAEHI" RNoPart="10">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Unterlagen nach Auftragserteilung (bis Montagebeginn)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Werkplanung soll mindestens beinhalten:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufstellplan</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Strang- und Verschaltungsplan</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektroplan</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übersichtsschaltbild mit Darstellung aller Schutzeinrichtungen</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ertragsprognose mit einer anerkannten Software.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Systemstatik bzw. Einzelstatik für das gewählte Montagesystem</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausführlicher Dachaufbau siehe Vorbemerkungen und übergebene Zeichnungen</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nachweis / Auslegungsnachweis der ausgewählten Kabel und Sicherungen für den jeweiligen Einsatzzweck</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Datenblätter ALLER Komponenten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbindung der Anlage in das Einspeisemanagement und Abstimmung mit dem AG</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überspannungsschutz</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verschaltung, Kabelverlegung sind vom AG bzw. seinem Vertreter vor Beginn der Arbeiten zu bestätigen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für jeweils alle fünf Teilanlagen</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Mensaanbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Anbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist ein Nachweis zur Abstimmung der Schnittstellen mit der Gebäudeleittechnik mit der MSR Firma beizubringen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Unterlagen sind in folgender Ausfertigung zu liefern:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 3-fach als Papier</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 1-fach digital</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Werkplanung Photovoltaik</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEBGOI" RNoPart="20">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wind- und Schneelastauslegung inkl Systemstatik passend zum gewählten UK- System und den spezifischen Dachaufbauten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übergabean den AG je Dach</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Mensaanbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Anbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
             <br/>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>erweiterte Werkplanung UK System</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEBOCI" RNoPart="30">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DAGMHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beweissicherung</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vor Baubeginn, während und nach Abschluss der Bauarbeiten ist durch den AN im Rahmen eines Beweissicherungsverfahrens die bestehende Baustellensituation (Dach) nachweisbar zu dokumentieren. Die Feststellung hat beweiskräftig zu erfolgen.</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Festgestellte Schäden sind protokollarisch und fotografisch (Foto mit eingeblendetem Datum) zu dokumentieren. Die Angaben sind durch den AG zu bestätigen. Die Beweissicherung muss mind. umfassen:</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fotodokumentation vor, während und nach der Baudurchführung in digitaler Form (jpg - Format)</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fotodokumentation der Bauleistungen (jpg- Format)   (chronologisch geordnet, beschriftet) </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dokumentation der Beweissicherung ist 1-fach vor Beginn der Arbeiten dem AG zu übergeben. Die Schlussbeweissicherung spätestens zur Abnahme.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übergabe je Dach</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Nordflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestandsschule Südflügel</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Mensaanbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Anbau</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sporthalle Hauptdach</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Beweissicherung</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBECHBI" RNoPart="40">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DAGMHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauzeitenplan</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellung eines Bauzeitenplan als Feinablaufplan mit einer Aufgliederung in die wesentlichen durchzuführenden Leistungen, nach Wahl des AN, als Balkenplan. Ablieferung und Ausfertigung in digitaler Form.</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vorlagetermin: 30 Tage vor Baubeginn.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Bauzeitenplan</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBECODI" RNoPart="50">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anmeldung der Photovoltaikanlage und Antragsstellung für den Einspeisezähler und die Abnahme beim zuständigen Energieversorgungsunternehmen incl. Bereitstellen aller erforderlichen Dokumentationen, Abstimmungen mit dem EVU und AG.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nachfolgend aufgeführte Unterlagen bzw. Aussagen dem Netzbetreiber zu übergeben:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- maßstabsgerechter Lageplan, aus dem die Bezeichnung (Gemarkung, Flur, Flurstück) und die Grenzen des Grundstücks/der Grundstücke sowie der Aufstellungsort(e) der Erzeugungsanlage(n) hervorgehen</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- vollständig ausgefülltes Datenerfassungsblatt der Erzeugungsanlage(n) (Vordruck des Netzbetreibers verwenden)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anzeige zur Inbetriebsetzung auf dem Formular &#x22;Anmeldung zum Netzanschluss&#x22; mit Datum und Unterschrift durch den aufgeführten Elektrofachbetrieb</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bestätigung des Herstellers/Errichters nach DGUV A3, § 5 Absatz 4 und Betriebsbereitschaftserklärung zur Inbetriebsetzung (Vordruck des Netzbetreibers verwenden).</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nachfolgend aufgeführte Unterlagen sind dem Auftragnehmer Starkstrom (electronic stadtroda) zu übergeben:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Prüfbericht Netz- und Anlagenschutz</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Datenblätter </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Übersichtsschaltbild</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Weitere Anforderungen sind auf der Internetpräsenz des Netzbetreibers und der Netzverträglichkeitsprüfung zu entnehmen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Anmeldung PV-Anlage bei Netzbetreiber</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEGHOI" RNoPart="60">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DAGMHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zuarbeit für Anmeldung der Anlage bei einem Direktvermarkter</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausfüllen aller notwendigen Antragsformulare und Beistellung und Zusammenstellung aller technischen Unterlagen</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Zuarbeit für Anmeldung der Anlage als Direktvermarkter</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEDOMI" RNoPart="70">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zuarbeit für die Erstellung eines Feuerwehrplans an den Auftragnehmer Ingenieurbüro Kunstmann</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Zuarbeit für Feuerwehrplan</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEEIFA" RNoPart="80">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DAGMHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauherrenabnahme und Einweisung</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einweisung entsprechend den Mindestanforderung einer Kundeneinweisung nach der Besonderen Güte und Prüfbestimmungen P3 des RAL Gütezeichen Solarenergieanlagen (GZ 966) der Photovoltaikanlage mit des vom Bauherrn benannten Nutzers, Teilnahme an der Bauherrenabnahme, Erläuterungen zur Betriebsweise und zum Aufbau der Photovoltaikanlage, Schalthandlungen, Havariefälle, Protokollierung der Einweisung und Verteilung der Unterlage an AG / Betreiber kompeltt durchführen und dokumentieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Bauherrenabnahme und Einweisung der Photovoltaikanlage</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEEPPI" RNoPart="90">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DAGMHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschilderung und Kennzeichnung nach RAL/VDE</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnung am Hausanschluss und der Hauptverteilung mit dem Hinweisschild &#x22;PV-Anlage&#x22; gemäß der Broschüre &#x22;Brandschutzgerecht Planung, Errichtung und Instandhaltung von PV-Anlagen&#x22;.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Beschilderung und Kennzeichnung nach RAL/VDE</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBEFHBI" RNoPart="100">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellung der erweiterten Anlagendokumention entsprechend den Anforderungen DIN EN 62446 sowie den Forderungen zu Gliederung und Dokumentation des Auftraggebers.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzlich muss vor Inbetriebnahme eine Isolations-, Spannungs- und Strommessung bei einer minimalen Einstrahlung von 500 W/m² durchgeführt und protokolliert werden.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Diese Messungen müssen bei nasser Witterung (150-300 W/m² Einstrahlung) wiederholt durchgeführt und protokolliert werden.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dokumentation muss jeweils einfach als Papierversion und einfach als digitale Version spätestens 4 Wochen nach der Endabnahme der Bauleitung übergeben werden.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kosten für die Erstellung der Anlagendokumentation sind, wenn nicht separat aufgeführt, in die Einheitspreise einzukalkulieren und werden nicht gesondert vergütet.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die vorgegebene Ordnerstruktur der Bestandsdokumentation des Auftraggebers liegt dieser Ausschreibung bei.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Erweiterte Anlagendokumentation</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
      </Itemlist>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="DBBFAAAA" RNoPart="3">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>PV-Anlage gleichstromseitig</span>
      </p>
     </LblTx>
     <BoQBody>
      <Itemlist>
       <Item ID="DBBFAEIA" RNoPart="10">
        <Qty>280.000</Qty>
        <QtySplit>
         <Qty>280.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß Auslegung liefern, montieren und anschließen:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Spezifikationen Solarmodul:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kristallines Modul, mit eingebauten Bypassdioden und hochtransparenter, spezialgehärteter Glasabdeckung.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit verwindungssteifem Rahmen aus Aluminiumprofilen</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inklusive vorkonfektionierten Kabeln und Steckern</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">10 Jahre Produktgarantie</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mindestens 25 Jahre lineare Leistungsgarantie,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsgarantie 92% für 10 Jahre, 83% für 25 Jahre</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zertifiziert nach IEC 61215</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV geprüft und zertifiziert, CE-Kennzeichnung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wind- / Schneelast bis 5400 Pa</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektrische Daten bei 1000 W/m², 25°C; AM = 1,5:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennleistung: mind. 440 Wp</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Toleranz: -0 Wp (Positiv-Sortierung)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Solarmodule 440 W für netzgekoppelte PV-Anlagen</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFAPPI" RNoPart="20">
        <Qty>54.000</Qty>
        <QtySplit>
         <Qty>54.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplette Unterkonstruktion für das Mensadach gemäß Plan </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Befestigung der Module an dem Montagesystem ist, sofern keine genormten Anschlüsse verwendet werden, durch die Vorlage einer allgemeinen bauaufsichtlichen Zulassung des Deutschen Instituts für Bautechnik (DIBt) nachzuweisen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller notwendigen Befestigungsprofile, Modulklemmen, Schrauben, Muttern, Unterlegscheiben aus Edelstahl, </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV / LGA zertifiziert</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauaufsichtliche Zulassung des DIBt</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dachhaut ist durch zusätztliche Streifen von Bautenschutzmatten unter der UK  vor Beschädigung zu schützen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">HINWEIS Mensaanbau Dachaufbau:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-bereichsweise Plattenbeschwerung der Dachhaut auf Bautenschutzmatte</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-10mm Dachabdichtung Bitumenbahnen 2lagig</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-20-180mm Gefälledämmung Mineralfaser WLS040 (Brandschutzanforderung)</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-120 mm Grunddämmung Mineralfaser</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-5mm Dampfsperre Bitumenbahn 1lagig</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>UK Mensadach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFBDHI" RNoPart="30">
        <Qty>51.000</Qty>
        <QtySplit>
         <Qty>51.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplette Unterkonstruktion Sporthalle Anbau gemäß Plan </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Befestigung der Module an dem Montagesystem ist, sofern keine genormten Anschlüsse verwendet werden, durch die Vorlage einer allgemeinen bauaufsichtlichen Zulassung des Deutschen Instituts für Bautechnik (DIBt) nachzuweisen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller notwendigen Befestigungsprofile, Modulklemmen, Schrauben, Muttern, Unterlegscheiben aus Edelstahl, </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV / LGA zertifiziert</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauaufsichtliche Zulassung des DIBt</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dachhaut ist durch zusätztliche Streifen von Bautenschutzmatten unter der UK  vor Beschädigung zu schützen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">HINWEIS Sporthalle Nebentrakt Anbau:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-10mm Dachabdichtung Bitumenbahnen 2lagig</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-20-160mm Gefälledämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-120mm Grunddämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-5mm Dampfsperre Bitumenbahn 1-lagig</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-200mm Stahlbetondecke</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>UK Sporthalle Anbau</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFGIMI" RNoPart="40">
        <Qty>98.000</Qty>
        <QtySplit>
         <Qty>98.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplette Unterkonstruktion Sporthalle Hauptdach gemäß Plan als durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Befestigung der Module an dem Montagesystem ist, sofern keine genormten Anschlüsse verwendet werden, durch die Vorlage einer allgemeinen bauaufsichtlichen Zulassung des Deutschen Instituts für Bautechnik (DIBt) nachzuweisen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller notwendigen Befestigungsprofile, Modulklemmen, Schrauben, Muttern, Unterlegscheiben aus Edelstahl, </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV / LGA zertifiziert</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauaufsichtliche Zulassung des DIBt</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dachhaut ist durch zusätztliche Streifen von Bautenschutzmatten unter der UK  vor Beschädigung zu schützen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">HINWEIS Sporthalle Hauptdach:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-10mm Dachabdichtung Bitumenbahnen 2lagig</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">tw. Gefälledämmkeile</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-200mm Dämmung Mineralfaser WLS 040</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-5mm Dampfsperre Bitumenbahn (durchtrittsicher)</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-165mm Stahltrapezblechdeckung Stat.-Pos. DA-01</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-d=1mm, Positivlage, m. Akustiklochung,</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-mit Sickenfüller MiWo</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>UK Sporthalle Hauptdach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFHMJI" RNoPart="50">
        <Qty>46.000</Qty>
        <QtySplit>
         <Qty>46.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplette Unterkonstruktion Bestand Nordflügel gemäß Plan </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Befestigung der Module an dem Montagesystem ist, sofern keine genormten Anschlüsse verwendet werden, durch die Vorlage einer allgemeinen bauaufsichtlichen Zulassung des Deutschen Instituts für Bautechnik (DIBt) nachzuweisen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller notwendigen Befestigungsprofile, Modulklemmen, Schrauben, Muttern, Unterlegscheiben aus Edelstahl, </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV / LGA zertifiziert</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauaufsichtliche Zulassung des DIBt</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dachhaut ist durch zusätztliche Streifen von Bautenschutzmatten unter der UK  vor Beschädigung zu schützen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">HINWEIS Schule Nordflügel Bestand:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-Bitumenabdichtung 2lagig 10mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-20-220mm Gefälledämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-120mm Grunddämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-Dampfsperre bitum. 5mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-zem. Ausgleichsestrich ca. 50mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-bestehende Stb.-Hohlplattendecken 250mm</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>UK Schule Bestand Nordflügel</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFGMBI" RNoPart="60">
        <Qty>31.000</Qty>
        <QtySplit>
         <Qty>31.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplette Unterkonstruktion Bestand Nordflügel gemäß Plan</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als durchdringungsfreie Unterkonstruktionen (UK) in Verbindung mit einer nachgewiesener optimierten Ballastierung in Südausrichtung in 10-15 % </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Befestigung der Module an dem Montagesystem ist, sofern keine genormten Anschlüsse verwendet werden, durch die Vorlage einer allgemeinen bauaufsichtlichen Zulassung des Deutschen Instituts für Bautechnik (DIBt) nachzuweisen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller notwendigen Befestigungsprofile, Modulklemmen, Schrauben, Muttern, Unterlegscheiben aus Edelstahl, </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TÜV / LGA zertifiziert</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauaufsichtliche Zulassung des DIBt</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typenprüfung / Typenstatik für Windlasten nach Eurocode 1:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN 1991-1-4 für 17 m Gebäudehöhe, Windzone I und Geländekategorie III , für</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schneelasten bis Schneelastzone Ia</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Dachhaut ist durch zusätztliche Streifen von Bautenschutzmatten unter der UK  vor Beschädigung zu schützen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile, aller Nebenarbeiten</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-style:italic;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">HINWEIS Schule Südflügel Bestand:</span>
             <br/>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-Bitumenabdichtung 2lagig 10mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-20-170mm Gefälledämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-160mm Grunddämmung EPS WLS 032</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-Dampfsperre bitum. 5mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-zem. Ausgleichsestrich ca. 50mm</span>
             <br/>
             <span style="font-family:Arial;font-style:italic;font-size:10pt;Color:rgb(0,0,0);">-bestehende Stb.-Hohlplattendecken 250mm</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>UK Schule Bestand Südflügel</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFBLBA" RNoPart="70">
        <Qty>2260.000</Qty>
        <QtySplit>
         <Qty>2260.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>m</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive. aller Montageteile, Steckverbinder und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Gleichstromkabel müssen so verlegt werden, dass sie keiner direkten Sonneneinstrahlung ausgesetzt sind.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der benötigte Kabelquerschnitt richtet sich nach der Anlagenauslegung. Es muss ein max.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungsverlust von 1,0% unter STC gewährleistet sein. Mindestquerschnitt: 4 mm² Kupfer.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(2 Strings) </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verlustberechnung muss vor Montage dem AG in nachprüfbarer Form zur Verfügung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gestellt werden (z.B. Excel - Tabelle).</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auf induktionsarme Verlegung der Strangverkabelung ist zu achten.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Spezifikationen:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu-Litze verzinnt, doppelt isoliert,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beständigkeit: sehr gute Witterungs- und UV-Beständigkeit,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Einsatz im Freien,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">hydrolyse- und mikrobenbeständig, adhäsionsarm,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abriebfest</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Halogenfreiheit: nach DIN VDE 0482 Teil 267 / EN 50267-2-1 / IEC 60754-1 (entspricht</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN VDE 0472 Teil 815)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Flammwidrigkeit: nach DIN EN 60332-1-2</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse: doppelt isoliert, Schutzklasse II</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Temperaturbereich: fest verlegt - 40°C bis + 90°C</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. 120°C am Leiter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung: 0,6/1 kV, bis max. 1800 V Gleichspannung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Strombelastbarkeit: 70 A bei freier, einzelner Verlegung und 60°C Umgebungstemp.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mindestbiegeradius: ca. 8x Leitungsdurchmesser für flexiblen Einsatz, ca. 4x</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungsdurchmesser für feste Verlegung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ: PV1-F (TÜV Bauart geprüft nach 2 PfG 1169/08.2007)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leiteraufbau feindrähtig nach VDE 0295, Klasse 5 / IEC 60228 Cl.5</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verlegung außerhalb des Montagesystems in Kabelschutzrohren aus korrosionsgeschütztem und UV-beständigem Material mit Anschluss an den Potentialausgleich.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dachdurchdringungen sind nicht  zugelassen. Die Befestigung der Verkabelung erfolgt an der UK der PV Anlage.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller Klemm- und Befestigungsmaterialien sowie aller notwendigen Kleinteile</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einzukalkulieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Gleichstromverkabelung Module-Wechselrichter</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFCHMA" RNoPart="80">
        <Qty>965.000</Qty>
        <QtySplit>
         <Qty>965.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>m</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbindung des PV-Gestells und der Wechselrichter an den Potentialausgleich durchgängige leitende Verbindung der PV-Montagegestelle untereinander</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel in UV-beständiger Ausführung bzw. Verlegung in Kabelschutzrohren aus</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">korrosionsgeschütztem und UV-beständigem Material</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für den Potentialausgleich des Montagesystems, der Wechselrichter, der Kabelkanäle, der Überspannungsableiter, der Datenfernübertagung inklusive aller Klemm- und Befestigungsmaterialien</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erdungsleiter muss parallel und in möglichst engem Kontakt mit den DC- und AC-Kabel verlegt werden</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inklusive Kennzeichung/Beschriftung der PA- Leiter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mindestquerschnitt 16 mm² Cu oder Äquivalent in Al/Edelstahl</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss an PAS</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Potentialausgleich/Erdung</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFKJEA" RNoPart="90">
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß Auslegung des Anbieters 15 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Montage erfolgt an der Wand/Gestell </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trafoloser Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Wirkungsgrad / Euro-Eta: mind 98,2% / 97,8%</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">MPP-Bereich ca  260 - 800 Vdc</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl DC-Eingänge / Anzahl MPP-Tracker min. 4 / 2</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximale Eingangsspannung 1000 V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximaler Eingangsstrom 12 A / Strang</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsseite Nennspannung 3/N/PE, AC, 230V / 400V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzfrequenz 50 Hz, dreiphasige Einspeisung,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">automatische Netzsynchronisation einschließlich </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Parallelbetrieb mehrerer Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter elektronischer DC-Freischalter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit RJ45, S0 und RS485-Schnittstelle</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. eingangsseitige Freischaltstelle /</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DC disconnet switch</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Garantie: mindestens 5 Jahre</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 65</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CE-Kennzeichnung, IEC 61727, VDE 0126-1-1</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">programmierbarer potentialfreier Kontakt für eine Sammelstörmeldung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der potentialfreie Kontakt ist in einer Klemmdose bis in die RLT Zentrale zu führen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Beschaltung des potentialfreien Kontaktes erfolgt durch das Gewerk MSR auf den nächstgelegenen ISP.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SolarCloud fähig /Web-IP Zugriff lokal oder über Internet.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der VDE-AR-N 4105</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wirkleistungsreduzierung bei Überfrequenz (ab 50,2 Hz mit Kennlinie)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blindleistungsbereitstellung (cosphi von 0,80 untererregt bis 0,80 übererregt )</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Externer zentraler NA-Schutz in einfehlersicherer Ausführung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der nach neuestem EEG Einspeisemanagement ( Möglichkeit zur ferngesteuerten Begrenzung der Einspeiseleistung durch den Verteilnetzbetreiber)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Standort der bauseitigen Daten- Netzwerkdose wird wettergschützt an bauseitig dem Gestell</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluss mit einem 10 m Patchkabel an die bauseitige Netzwerkdose ist in die Position einzukalkulieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Netzeinspeisewechselrichter 15 kVA</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFDKOA" RNoPart="100">
        <Qty>3.000</Qty>
        <QtySplit>
         <Qty>3.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß Auslegung des Anbieters 25 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Montage erfolgt an der Wand/Gestell </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trafoloser Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Wirkungsgrad / Euro-Eta: mind 98,2% / 97,8%</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">MPP-Bereich ca 430 - 800 Vdc</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl DC-Eingänge / Anzahl MPP-Tracker min. 6 / 3</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximale Eingangsspannung 1000 V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximaler Eingangsstrom 12 A / Strang</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsseite Nennspannung 3/N/PE, AC, 230V / 400V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzfrequenz 50 Hz, dreiphasige Einspeisung,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">automatische Netzsynchronisation einschließlich </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Parallelbetrieb mehrerer Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter elektronischer DC-Freischalter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit RJ45, S0 und RS485-Schnittstelle</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. eingangsseitige Freischaltstelle /</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DC disconnet switch</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Garantie: mindestens 5 Jahre</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 65</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CE-Kennzeichnung, IEC 61727, VDE 0126-1-1</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">programmierbarer potentialfreier Kontakt für eine Sammelstörmeldung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der potentialfreie Kontakt ist in einer Klemmdose bis in die RLT Zentrale zu führen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Beschaltung des potentialfreien Kontaktes erfolgt durch das Gewerk MSR auf den nächstgelegenen ISP.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SolarCloud fähig /Web-IP Zugriff lokal oder über Internet.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der VDE-AR-N 4105</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wirkleistungsreduzierung bei Überfrequenz (ab 50,2 Hz mit Kennlinie)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blindleistungsbereitstellung (cosphi von 0,80 untererregt bis 0,80 übererregt )</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Externer zentraler NA-Schutz in einfehlersicherer Ausführung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der nach neuestem EEG Einspeisemanagement ( Möglichkeit zur ferngesteuerten Begrenzung der Einspeiseleistung durch den Verteilnetzbetreiber)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Standort der bauseitigen Daten- Netzwerkdose wird wettergschützt an bauseitig dem Gestell</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluss mit einem 10 m Patchkabel an die bauseitige Netzwerkdose ist in die Position einzukalkulieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Netzeinspeisewechselrichter 25 kVA</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFEAAA" RNoPart="110">
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß Auslegung des Anbieters 50 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Montage erfolgt an der Wand/Gestell </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trafoloser Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Wirkungsgrad / Euro-Eta: mind 98,2% / 97,8%</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">MPP-Bereich ca 500 - 800 Vdc</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl DC-Eingänge / Anzahl unabhäng MPP-Tracker min. 12 / 6</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximale Eingangsspannung 1000 V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximaler Eingangsstrom 12 A / Strang</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsseite Nennspannung 3/N/PE, AC, 230V / 400V</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzfrequenz 50 Hz, dreiphasige Einspeisung,</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">automatische Netzsynchronisation einschließlich </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Parallelbetrieb mehrerer Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter elektronischer DC-Freischalter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit RJ45, S0 und RS485-Schnittstelle</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. eingangsseitige Freischaltstelle /</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DC disconnet switch</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Garantie: mindestens 5 Jahre</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 65</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CE-Kennzeichnung, IEC 61727, VDE 0126-1-1</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">programmierbarer potentialfreier Kontakt für eine Sammelstörmeldung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der potentialfreie Kontakt ist in einer Klemmdose bis in die RLT Zentrale zu führen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Beschaltung des potentialfreien Kontaktes erfolgt durch das Gewerk MSR auf den nächstgelegenen ISP.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SolarCloud fähig /Web-IP Zugriff lokal oder über Internet.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der VDE-AR-N 4105</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wirkleistungsreduzierung bei Überfrequenz (ab 50,2 Hz mit Kennlinie)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blindleistungsbereitstellung (cosphi von 0,80 untererregt bis 0,80 übererregt )</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Externer zentraler NA-Schutz in einfehlersicherer Ausführung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einhaltung der Bestimmungen der nach neuestem EEG Einspeisemanagement ( Möglichkeit zur ferngesteuerten Begrenzung der Einspeiseleistung durch den Verteilnetzbetreiber)</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Standort der bauseitigen Daten- Netzwerkdose wird wettergschützt an bauseitig dem Gestell</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluss mit einem 10 m Patchkabel an die bauseitige Netzwerkdose ist in die Position einzukalkulieren.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Netzeinspeisewechselrichter 50 kVA</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFJFDI" RNoPart="120">
        <Qty>1.000</Qty>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vorgefertigter externer NA-Schutz 4fach bis 4x 30 kVA</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl Überwachungsrelais, 8 Leistungsschütze </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl 2 Netzpuffer 24 VDC</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TT - Netz allpolig</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl Gehäuse vormontiert für 4 separate PV Anlagen und aller weiteren Vorgaben aus VDE-AR-N 4100, 4105 und TAB</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung inkl. notwendigem Zubehör, Montage, Inbetriebnahme und Dokumentation</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>externer NA-Schutz 4fach bis 4x 30 kVA</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFPAAA" RNoPart="130">
        <Qty>1.000</Qty>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vorgefertigter externer NA-Schutz 1fach bis 70 kVA</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl Überwachungsrelais, 2 Leistungsschütze </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl Netzpuffer 24 VDC</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TT - Netz allpolig</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl Gehäuse vormontiert für PV Anlagen und aller weiteren Vorgaben aus VDE-AR-N 4100, 4105 und TAB</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lieferung inkl. notwendigem Zubehör, Montage, Inbetriebnahme und Dokumentation</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>externer NA-Schutz 1fach bis 1x 70 kVA</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFKDAA" RNoPart="140">
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wechelrichtergestell mit ausreichender Ballastierung </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung passen zu den ausgelegten Wechselrichtern</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x 15 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Wechselrichtergestell dient der </span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einfachen, schnellen Montage von Wechselrichtern auf Flachdächern mit Bitumen oder Kunststoff Abdichtung. Das Dach schützt den Wechselrichter gegen UV-Strahlung und Bewitterung und verbessert so dessen Performance und Gebrauchsdauer. </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Um Beschädigungen an der Dachhaut zu vermeiden, sind die  Auflagen des Gestelles ist mit einer Bautenschutzmatte zu versehen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Wechselrichtergestell 15 kVA inkl Ballastierung und Dach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFIFGI" RNoPart="150">
        <Qty>3.000</Qty>
        <QtySplit>
         <Qty>3.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wechelrichtergestell mit ausreichender Ballastierung</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung passen zu den ausgelegten Wechselrichtern</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x25 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Wechselrichtergestell  dient der </span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einfachen, schnellen Montage von Wechselrichtern auf Flachdächern mit Bitumen oder Kunststoff Abdichtung. Das Dach schützt den Wechselrichter gegen UV-Strahlung und Bewitterung und verbessert so dessen Performance und Gebrauchsdauer. </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Um Beschädigungen an der Dachhaut zu vermeiden, sind die  Auflagen des Gestelles ist mit einer Bautenschutzmatte zu versehen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Wechselrichtergestell 25 kVA inkl Ballastierung und Dach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFLJEA" RNoPart="160">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wechelrichtergestell mit ausreichender Ballastierung </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung passen zu den ausgelegten Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x 50 kVA</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Wechselrichtergestell dient der </span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einfachen, schnellen Montage von Wechselrichtern auf Flachdächern mit Bitumen oder Kunststoff Abdichtung. Das Dach schützt den Wechselrichter gegen UV-Strahlung und Bewitterung und verbessert so dessen Performance und Gebrauchsdauer. </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Um Beschädigungen an der Dachhaut zu vermeiden, sind die  Auflagen des Gestelles ist mit einer Bautenschutzmatte zu versehen.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsorgung anfallender Abfälle bzw. Verwertung anfallende Wertstoffe (z.B. Verpackungen) gemäß Kreislaufwirtschafts- und Abfallgesetz. Die Kosten sind einzukalkulieren.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Wechselrichtergestell 50 kVA inkl Ballastierung und Dach</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBFEPCA" RNoPart="170">
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EEG konforme Inbetriebnahme inklusive Dokumentation für den Netzbetreiber, digitale Kopie für AG</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inbetriebnahme der kompletten Solaranlage, Datenfernüberwachung sowie Fernwirktechnik der SWJN &#x3e; 100 kWp inklusive Fertigung eines Inbetriebnahmeprotokolls.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Inbetriebnahme</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
      </Itemlist>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="DBBGAAAA" RNoPart="4">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>PV-Anlage wechselstromseitig</span>
      </p>
     </LblTx>
     <BoQBody>
      <Itemlist>
       <Item ID="DBBGAEIA" RNoPart="10">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wechselstromverkabelung Wechselrichter</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss an bauseitig verlegter Leitung bis </span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x NYY-J 4x25 mm²</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x NYY-J 4x16 mm²</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x NYY-J 4x35 mm²</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der vom AN Elektro verlegte Kabelquerschnitt richtet sich nach der Werkplanung des AN Photovoltaik und dessen  Anlagenauslegung (Wechselrichter). </span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zusätzlicher Anschluss an den  Potentialausgleich bis 1x16 mm²</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inklusive aller Klemm- und Befestigungsmaterialien  sowie aller notwendigen Kleinteile</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Wechselstromverkabelung</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBGAOMI" RNoPart="20">
        <LumpSumItem>Yes</LumpSumItem>
        <Qty>1.000</Qty>
        <QtySplit>
         <Qty>1.000</Qty>
         <CtlgAssign>
          <CtlgID>DBABHLCI</CtlgID>
          <CtlgCode>442</CtlgCode>
         </CtlgAssign>
        </QtySplit>
        <QU>psch</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. aller Montageteile und aller Nebenarbeiten liefern und montieren:</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnung aller AC-Kabel an beiden Enden mit wetterfester, beständiger Beschriftung nach DIN VDE 0100: &#x22;Wechselrichter Nr.&#x22;</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnung aller Kommunikations-Kabel an beiden Enden mit wetterfester, beständiger Beschriftung nach DIN VDE 0100: &#x22;Wechselrichter Nr.&#x22;</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnung am Hausanschlusskasten und der Gebäudehauptverteilung mit dem Hinweisschild &#x22;PV-Anlage&#x22; gemäß der Broschüre &#x22;Brandschutzgerechte Planung, Errichtung und Instandhaltung von PV-Anlagen&#x22;</span>
            </p>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Beschilderung / Kennzeichnung AC-Kabel und Kommunikationskabel</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBGCAIA" RNoPart="30">
        <Qty>240.000</Qty>
        <QU>m</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Weitspannkabelrinne 110 mm x 200 mm, </span>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit einem Trennsteg,</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Überbrückung von Stützabständen bis 6 Meter, </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Verstärkung eingearbeitete Sicken alle 300 mm,</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durchgängig gelochter und abgekanteter Seitenholm</span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Verstärkung und als Kabelschutz. </span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Werkstoff: feuerverzinkt ZN500 </span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Weitspannkabelrinne 200 mm</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBGCIEA" RNoPart="40">
        <Qty>140.000</Qty>
        <QU>m</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deckel 200 mm mit Drehriegeln, für Weitspannkabelrinne </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Weitspannkabelleiter mit der Seitenhöhe 110 </span>
            </p>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wie zuletzt beschrieben.</span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Deckel</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
       <Item ID="DBBGCPCA" RNoPart="50">
        <Qty>48.000</Qty>
        <QU>St</QU>
        <Description>
         <CompleteText>
          <DetailTxt>
           <Text>
            <p style="text-align:justify;line-height:12pt;margin-top:0pt;margin-bottom:0pt;width:215px;tab-stops:19.90mm;">
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wand- und Stielausleger, Ausführung mittelschwer, mit angeschweißter Kopfplatte, zur Befestigung an U-Hängestiel-Systemen oder direkt an Wände und Konstruktionen</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Werkstoff:</span>
             <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerverzinkt ZN 500</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessung:</span>
             <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">210 x 60 mm</span>
             <br/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragfähigkeit:</span>
             <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
             <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3 kN </span>
            </p>
           </Text>
          </DetailTxt>
          <OutlineText>
           <OutlTxt>
            <TextOutlTxt>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span>Ausleger</span>
             </p>
            </TextOutlTxt>
           </OutlTxt>
          </OutlineText>
         </CompleteText>
        </Description>
       </Item>
      </Itemlist>
     </BoQBody>
    </BoQCtgy>
   </BoQBody>
  </BoQ>
 </Award>
</GAEB>
