<?xml version="1.0" encoding="UTF-8"?>
<!-- GXML Toolbox V3.3 R20230829;  http://www.gaeb-toolbox.de/ 
 gtcConverter.dll used version 2024.07.02  -->
<GAEB xmlns="http://www.gaeb.de/GAEB_DA_XML/DA83/3.2">
 <GAEBInfo>
  <Version>3.2</Version>
  <VersDate>2013-10</VersDate>
  <Date>2026-05-08</Date>
  <Time>12:07:36</Time>
  <ProgSystem>/ GXML Toolbox V3.3 R20230829</ProgSystem>
  <ProgName>iTWO_64 V25.0.772</ProgName>
 </GAEBInfo>
 <PrjInfo>
  <NamePrj>1356</NamePrj>
  <LblPrj>PA Stadt Seelze IGS Berthold Brecht, Sanierung + Erweiterung</LblPrj>
  <Cur>EUR</Cur>
  <CurLbl>Euro</CurLbl>
 </PrjInfo>
 <Award>
  <DP>83</DP>
  <AwardInfo>
   <Cur>EUR</Cur>
   <CurLbl>Euro</CurLbl>
  </AwardInfo>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>LEISTUNGSBESCHREIBUNG</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <span style="font-family:Arial;font-weight:bold;font-size:16pt;Color:rgb(0,0,0);">LEISTUNGSBESCHREIBUNG</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">über die</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-weight:bold;font-size:12pt;Color:rgb(0,0,0);">Lieferung und Montage von  Fernmeldetechnische Anlagen</span>
     <br/>
     <br/>
     <br/>
     <br/>
     <br/>
     <br/>
     <br/>
     <br/>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <br/>
     <br/>
     <br/>
     <br/>
     <br/>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauvorhaben:</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umbau und Erweiterung der Bertolt-Brecht-Gesamtschule</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Humboldtstr. 14</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30926 Seelze </span>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewerk:</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">542-F22 - Fernmeldetechnische Anlagen</span>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">             </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauteil C/F</span>
    </p>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:-141pt;margin-left:226pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauherr:</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stadt Seelze</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rathausplatz 1</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30926 Seelze</span>
    </p>
    <page/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>1.0 Objekt- und Anlagenbeschreibung</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IV.  Vorbemerkungen zum Leistungsverzeichnis</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">=====================================</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1.0  Objektbeschreibung</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">===================</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Allgemein</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Stadt Seelze beabsichtigt die Erweiterung und den Umbau der Bertolt-Brecht-Gesamtschule in Seelze.</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Geplant ist ein Erweiterungsbau als Neubau, bestehend aus einem 4-geschossigen Baukörpern (Bauteil A).</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In den Gebäudetrakten B, C, D, E werden Umbaumaßnahmen vorgenommen, ebenso im Bauteil H, einem ehemaligen Kioskgebäude. </span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die bestehende Sporthalle, Bauteil F, erhält einen Anbau (1-Feld-Sporthalle).</span>
     <br/>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Gebäudekomplex befindet sich an einer befestigten Straße und ist verkehrstechnisch gut zu erreichen. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Folgende Arbeiten sind auszuführen:</span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bestand Bauteil C:</span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <ul style="text-indent:0pt;margin-left:85pt;margin-right:127pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellen eines Kabelzugplanes</span>
     </li>
    </ul>
    <ul style="text-indent:0pt;margin-left:85pt;margin-right:127pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erweiterung einer Brandmeldeanlage</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erweiterung einer Sprachalarmierungsanlage</span>
     </li>
    </ul>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Neubau Sporthalle (Bauteil F): </span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <ul style="text-indent:0pt;margin-left:85pt;margin-right:127pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellen eines Kabelzugplanes</span>
     </li>
    </ul>
    <ul style="text-indent:0pt;margin-left:85pt;margin-right:127pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Errichtung einer Brandmeldeanlage</span>
     </li>
     <li>
      <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Errichtung einer Sprachalarmierungsanlage</span>
     </li>
    </ul>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Arbeiten sind ab ca. August 2026 bis ca. September 2027 (Unterbrechungen sind mit einzukalkulieren) auszuführen..</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Sonstiges</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bautageberichte</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bautageberichte sind wöchentlich bei der Objektüberwachung einzureichen.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauzeitenplan</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer hat, sofern keine andere Frist vereinbart wird, innerhalb von 2 Wochen nach der Auftragserteilung einen detaillierten Ausführungsterminplan (Bauzeitenplan) auf der Grundlage der verienbarten Vetragsfristen aufzustellen. Einzelheiten sind mit dem Auftraggeber rechtzeitig vorher abzustimmen. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Veröffentlichungen</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer verpflichtet sich, alle ihm zugänglich gemachten oder bekannt gewordenen Unterlagen, Daten, Informationen, Erkenntnisse usw. vertraulich zu behandeln und nicht an Dritte weiterzugeben. Der Auftragnehmer darf Veröffentlichungen über die ausgeführten Leistungen nur mit vorheriger schriftlicher Zustimmung des Auftraggebers vornehmen.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Baustelleneinrichtung</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Räume zur Lagerung können nicht zur Verfügung gestellt werden Sozial- und Lagercontainer können nach Abstimmung mit der örtlichen Bauleitung aufgestellt werden.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eine separate Vergütung erfolgt hierfür nicht.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Baustellenreinigung/ Bauabfälle</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer ist gehalten, Abfälle nach Möglichkeit zu vermeiden,wenigstens zu reduzieren. Anfallende Abfälle, Bauschutt Verpackungen und dergl. bleiben Eigentum des AN. Sie sind sofort nach Abschluss der Tätigkeit zu beseitigen, spätestens jedoch wöchentlich. Bei Nichteinhaltung dieser Regelung wird der Abfall nach vorherige Abmahnung zu Lasten des Verursachers beseitigt. Bei fehlender Zuordnungsmöglichkeit z.B. bei allgemeinen Abfällen, werden die Entsorgungskosten anteilig auf die anwesenden Gewerke umgelegt.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Baubewachung</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eine Baustellenbewachung ist nicht vorhanden; der Auftragnehmer übernimmt allein die Verantwortung für die sichere Lagerung und Verwahrung seiner Maschinen, Geräte, Hilfsbetriebsstoffe, Materialien, Einrichtungen usw. bis zum Ende seiner Gesamtbauleistung. Eine Baustellenbewirtschaftung ist nicht möglich.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rechnungslegung</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es gelten EVM 215, Ziffern 10 - 15.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Aufmaße sind als steigendes Aufmaß zu führen, d. h. die bereits aufgemessenen und ggf. revidierten Positionen sind in den einzelnen Aufmaßen der Teilrechnungen ebenfalls mit aufzuführen. Die Seiten sind durch zu nummerieren. Auf jedem Aufmassblatt müssen die Spalten mit Positionen und den dazu gehörigen Räumen aufgeführt sein. Sollte es Kürzungen oder Zugaben in den einzelnen Teilaufmaßen geben, so sind diese für die nächste Teilrechnung, nach Klärung etwaiger Differenzen, einzupflegen. </span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sollten Nachtragspositionen zum Tragen kommen, so sind diese spätestens in der dazugehörigen Teilrechnung aufzuführen. Weiterhin sind die Kopien der Einkaufsrechnungen und ein </span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kalkulationsnachweis mit anzufügen !</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Einreichung der zu genehmigenden Schaltpläne müssen alle relevanten Positionen ( auch Nachträge ) mit den Einheitspreisen des LV´s zwecks Kostenüberwachung mit eingereicht werden.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sollte die Aufmaßpflege, sowie die Rechnungsstellung nicht so erfolgen wie oben beschrieben, können die Aufmaße einschl. Rechnung ungeprüft zurückgegeben werden.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Unklarheiten über das o. g. Verfahren ist die Bauleitung (Fachplaner) vor Beginn der Arbeiten anzusprechen. Eine Klärung von Unklarheiten nach Rechnungsstellung wird nicht akzeptiert.</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
    </p>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>2.0 Zusätzliche technische Vorbemerkungen (ZTV)</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3.0 </span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliche technische Vorbemerkungen (ZTV)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TGA Elektrischer Strom / Starkstrom</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">============================================</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>CAD-Pflichtenheft</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CAD-Pflichtenheft</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitens Auftragnehmer ist, falls vorhanden, das CAD-Pflichtenheft des Auftraggebers bei der Erstellung der Montage- und Revisionsunterlagen zu beachten und anzuwenden. Der Auftragnehmer selbst hat dieses vor der Erstellung der Planungen beim zuständigen Fachplaner abzufordern.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Lagermöglichkeiten</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagermöglichkeiten</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nach Festlegung mit dem Hausmeister kann ein Raum zur Lagerungen gewisser Mengen und zur Unterbringung der Mitarbeiter während der Bauzeit zur Verfügung gestellt werden.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Erstellung Nachtragsangebot</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellung Nachtragsangebot</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Falls im Zuge der Maßnahme festgestellt wird, dass zusätzliche Leistungen zu den Leistungen dieser Ausschreibung zu erbringen sind, hat der Auftragnehmer einen Nachtrag mit folgenden Unterlagen einzureichen:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Nachtragsangebot</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kalkulationsnachweis</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Einkaufs-/ Einstandspreisnachweis (Angebot Lieferant)</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Kalkulationsnachweis muss folgenden Inhalte pro Position haben:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Positionsnummer</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Einkaufspreis</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zuschlag nach VHB 221</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Minutenanzahl</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Lohnanteil/ Minute nach VHB 221</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Angebotspreis pro Stück</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hierfür wird vom zuständigen Fachplanungsbüro eine Vorlage bei  Auftragsvergabe übermittelt, die dafür verwendet werden kann.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Montageunterlagen</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Montageunterlagen</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TGA Elektrischer Strom / Starkstrom</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TGA Fernmeldetechnik / Schwachstrom</span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">----------------------------------------------------</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Die Anfertigung aller Montage- und Werkstattzeichnungen</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anfertigung aller Montage- und Werkstattzeichnungen obliegt dem Auftragnehmer.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vom Auftraggeber werden CAD-Zeichnungsdateien (als DXF- oder AutoCAD- DWG und zugehörige PDF-Dateien) der Grundriss- und Schnittpläne und ggf. Lagepläne für die Aufstellung der Unterlagen per Datenträger zur Verfügung gestellt. Zu Kontrollzwecken erhält der AN die zugehörigen Zeichnungen als farbige Plots (1-fach).</span>
     <br/>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Er hat diese, soweit es zur ordnungsgemäßen Vertragserfüllung gehört, auf etwaige Unstimmigkeiten und Durchführbarkeit zu überprüfen und den Auftraggeber auf entdeckte oder vermutete Mängel schriftlich hinzuweisen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Montagepläne sind rechtzeitig vor Montagebeginn in farbiger-Ausfertigung (2-fach) und im Datenformat (DXF oder AutoCAD-DWG und zugehörigen PDF-Dateien) mittels Datenträger zur Einsichtnahme einzureichen.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer hat folgende Pläne zu fertigen:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1. Grundrisszeichnungen mit den eingetragenen Installationen einschließlich der Hauptleitungswege mit  </span>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Kabeltrassen und Installationskanälen</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2. Aufstellungspläne von Geräten</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3. System- und/oder Übersichtsschaltbilder</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4. Aufbauzeichnungen</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5. Belegungspläne</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">6. Stromlaufpläne</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Änderungen oder Ergänzungen dieser Pläne nach Auftragsvergabe werden, soweit notwendig, während der Bauzeit auf der Baustelle von der Fachbauleitung manuell - mit Unterschrift - vorgenommen.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Diese Änderungen werden Bestandteil des Auftrages und sind entsprechend bei der Ausführung zu berücksichtigen.</span>
     <br/>
     <br/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer verpflichtet sich, die Montagezeichnungen bis zum Ende der Bauzeit vollständig auf der Baustelle zu bewahren und geeignete Maßnahmen gegen Beschädigung und/oder Verlust zu ergreifen.</span>
    </p>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Revisionsunterlagen</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Revisionsunterlagen</span>
    </p>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Zur Revision sind zu fertigen und bei Abnahme</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Revision zu fertigen und bei Abnahme der Leistungen dem Auftraggeber zu übergeben sind:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Revisionsunterlagen Elektrotechnik</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In den Bestands- und Revisionsunterlagen ist der Zustand der Anlage zum Zeitpunkt der Abnahme zu dokumentieren.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Unterlagen sind 3-fach (in Ordnern) sowie digitalem Datenträger (als dwg und pdf Dateien) zu liefern. Für Zeichnungen ist zusätzlich 1 Satz Papierpausen als Anlage zur Schlussrechnung zu liefern.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Erstellung von Zeichnungen gilt:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Mindestformat ist DIN A4, das Höchstformat DIN A0. Lagepläne sind im Maßstab 1:200, Grundrisspläne für die Hausinstallation im Maßstab 1:100 oder 1:50, Zentralen im Maßstab 1:20 auszuführen. Abweichungen bedürfen der Genehmigung der Bauleitung.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In den Installationsplänen sind alle elektrischen Betriebsmitteln, Anlagenteile, Verteilerkästen usw. einschl. deren Stromkreisbezeichnungen sowie Kabeltrassen darzustellen. Die Zeichnung soll außerdem alle für eine Orientierung erforderlichen Hinweise, wie Nordpfeil, angrenzende Straßen mit Namen, Geschoss- und Raumbezeichnungen usw. enthalten und in der unteren rechten Ecke mit einem Schriftfeld versehen sein. Das Schriftfeld muss Aufschluss über das Objekt, die Grundstücksbezeichnung, die Art der Anlage, den Zeichnungsinhalt, das System, die ausführende Firma und den Zeichnungshersteller geben, sowie die Unterschriften der beteiligten Firma und Sachbearbeiter mit Datum sowie die Angabe des Zeichnungsmaßstabes und der Blattgröße enthalten.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Unterlagen sind mit Inhaltsverzeichnis in Ordnern (keine A4-Schnellhefter- mappen) zu liefern, außerdem sind zu allen gelieferten Unterlagen Dateien auf Datenträger gemäß den aufgeführten Spezifikationen zu liefern.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Folgende Unterlagen sind bis zur Abnahme zu erbringen:</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Installationspläne mit den elektrischen Betriebsmitteln, wie Verteilerkästen, Antriebe etc. einschl. deren </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Stromkreisbezeichnungen sowie Kabeltrassen: in Dateiformat DXF oder DWG und PDF.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Übersichtsschemata der Anlagen als Prinzip bzw. Blockschaltbild: in Dateiformat DXF oder DWG und PDF.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Übersichts- bzw. Stromkreispläne der Verteiler: in Dateiformat DXF oder DWG und PDF</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Messprotokolle über das Ergebnis der Inbetriebnahme: in Dateiformat Word-, Excel- und PDF-Datei</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- CEKonformitäts-Kennzeichnung bzw. -erklärung gemäß EWG-Beschluss 901683 für die vorgesehenen</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Industrieerzeugnisse bzw. -produkte (CE-Kennzeichen): in Dateiformat Word-, Excel-, PDF-Datei.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Dokumentation über Beleuchungsmessungen: in Dateiformat Word-, Excel- und PDF-Datei.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Prüfzertifikate für die Kabel FE 180/E30, E60 und Kabelträgersysteme mit „FE“: nur Papier erforderlich.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Prüfprotokoll des Sachverständigen über die Hauptprüfung nach DIN BDE 0828 als Anlage zum </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Abnahmeprotokoll des  AG: in Papierform und PDF erforderlich.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Formlose Bestätigung, aus der hervorgeht, dass bei der Errichtung der elektrischen Anlage und </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Einrichtungen die einschlägigen DIN VDE-Bestimmungen sowie UVV (DGUV Vorschrift 3) uneingeschränkt </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Berücksichtigung gefunden haben: in Papierform und PDF erforderlich.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- die Bedienungs- und Wartungsunterlagen: in Dateiformat Word-, Excel-, PDF-Datei.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- die Gerätelisten als Betriebsmittelübersicht für Wartungs- und  Ersatzbeschaffung: in Dateiformat Word-, </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Excel-, sowie PDF-Datei.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fließ-, Stromlauf- und Schaltschemata als Bestandszeichnungen für Technikzentralen, jeweils ein Schema </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  (farbig angelegte Papierpause) auf einer wasserfesten Platte aufgezogen, mit Folie abgedeckt, mit </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  schlagfestem Umleimer versehen, versenkte Aufhänger, Filzabstandklötze: in Dateiformat Word-, Excel- </span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  sowie PDF-Datei.</span>
    </p>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <BoQ ID="AAAAAAAAIBBDAAAA">
   <BoQInfo>
    <Name>542-F22</Name>
    <LblBoQ>Gefahrenmeldeanlage Bauteil C+F</LblBoQ>
    <Date>2026-05-08</Date>
    <OutlCompl>AllTxt</OutlCompl>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn> 1</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn>Bereich</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn>Abschnitt</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Item</Type>
     <Length>4</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Index</Type>
     <Length>1</Length>
     <Num>No</Num>
     <Alignment>left</Alignment>
    </BoQBkdn>
    <NoUPComps>4</NoUPComps>
    <LblUPComp1 Type="Unknown">Löhne</LblUPComp1>
    <LblUPComp2 Type="Unknown">Stoffe</LblUPComp2>
    <LblUPComp3 Type="Unknown">Geräte</LblUPComp3>
    <LblUPComp4 Type="Unknown">Sonstiges</LblUPComp4>
    <Ctlg>
     <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
     <CtlgType>miscellaneous</CtlgType>
     <CtlgName>DIN276_08</CtlgName>
    </Ctlg>
    <Ctlg>
     <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
     <CtlgType>miscellaneous</CtlgType>
     <CtlgName>DIN276_18</CtlgName>
    </Ctlg>
    <Ctlg>
     <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
     <CtlgType>miscellaneous</CtlgType>
     <CtlgName>DIN276 neu</CtlgName>
    </Ctlg>
    <Ctlg>
     <CtlgID>AAAAAAAAIBJOBHOI</CtlgID>
     <CtlgType>work category</CtlgType>
     <CtlgName>Leistungsbereichkatalog</CtlgName>
    </Ctlg>
   </BoQInfo>
   <BoQBody>
    <BoQCtgy ID="AAAAAAAAIBFJAAAA" RNoPart="1">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>Bauteil C (Bestand)</span>
      </p>
     </LblTx>
     <BoQBody>
      <Remark ID="AAAAAAAAIBFJAJDI">
       <Description ID="R20190607093418960000030">
        <CompleteText>
         <DetailTxt>
          <Text>
           <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
            <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">KG 450 Kommunikations-, sicherheits- und informationstechnische Anlagen</span>
           </p>
          </Text>
         </DetailTxt>
         <OutlineText>
          <OutlTxt>
           <TextOutlTxt>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span>KG 450 Kommunikations-, sicherheits- und informationstechnische Anlagen</span>
            </p>
           </TextOutlTxt>
          </OutlTxt>
         </OutlineText>
        </CompleteText>
       </Description>
      </Remark>
      <BoQCtgy ID="AAAAAAAAIBFJBFBI" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 454 Elektroakustische Anlagen</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>454</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>454</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <BoQCtgy ID="AAAAAAAAIBFJBOEI" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 454 Sprachalarmierungsanlage (DIN VDE 0833-4)</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBFJCHIA">
            <PerfNo>16</PerfNo>
            <PerfLbl>Technische Forderungen</PerfLbl>
            <Description ID="R20251104135233366000123">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:25.00mm 37.50mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:25.00mm 37.50mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">        </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABT-CU-11LT</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bestandsanlage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20230125142506903000134">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle vorgenannten Technischen Forderungen sind, falls nicht anders in den Texten beschrieben, vom Bieter in den Positionen einzukalkulieren und werden somit nicht separat vergütet.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>vorgenannte Technische Forderungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Item ID="AAAAAAAAIBFJEKKI" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749393002052">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-indent:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachte, mikroprozessorgesteuerte Systemsprechstelle</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4,5&#x22; - Touch-Screen Display</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frei programmierbare Funktions-Tasten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Audio-Eingänge für den Anschluss von externen Audio-Quellen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bis zu 5 Tastenerweiterungen anschließbar</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingebauter Lautsprecher und Intercom-Funktion</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussbuchse für Headset</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PoE</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungsversorgung</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PoE (RJ45), oder über zusätzlichen Netzteil-Eingang 48 VDC / 15 W</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LCD-Anzeige</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auflösung 272 x 480, 4,5rdquo; Touchscreen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Audioausgänge</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Kanäle (Monitorlautsprecher, Headset)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Audioeingänge</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Kanäle / 2x Klinkenstecker 3,5 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsleistung Monitorlautsprecher</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,5 W</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruckpegel</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">78 dBA (@1m, 1 W)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kopfhörerausgang (Headset)</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Klinkenstecker 3,5 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mikrofon</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektret, Schwanenhals</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Tasten</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5 + PushToTalk, zusätzlich drei Kontrollleuchten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebstemperatur</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-8°C bis 60°C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">150x55x210 mm (BxHxT)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1,4 kg</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABT-DMS-LCD</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Digitale Systemsprechstelle</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJGHEA" RNoPart="20">
            <Qty>22.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749403002055">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandaufbaulautsprecher für AB-Verkabelung, 2x6W,100V, zertifiziert gemäß EN 54-24</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x6W Alarmierungs- Lautsprecher- System, redundante Beschallung, mit resonanzarmes Gehäuse, Federschnappverschlüsse auf der Rückwand für schnelle Montage und Anschluss, hochschalldurchlässige Frontabdeckung mit feiner Perforation, geeignet für horizontale und vertikale Wand oder Deckenmontage.2 Stück leistungsstarke und feuchtigkeitsimprägnierte 5“ Oval- Beitbandchassis mit Hochtonkegel eingebaut, 2 Stück hochwertige 100V-Anpassungs-Übertrager mit je:1/1-1/2-1/4 Leistungsanpassung, sowie 2 integrierte Keramikklemmen und 2 Thermosicherungen. RoHS-Konform</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten :</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit (Musik):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 (15)W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen 100V:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 3 1,5 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzbereich:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">230  18.379 Hz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck 1W/1m/max:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">97,8/112,8dB</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecher:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 5“ Oval- Breitbandchassis mit </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hochtonkegel </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz(Chassis):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 8 Ohm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Gehäuse/Lochblech:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">weiß, ähnlich RAL 9016 </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">       </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ca. L 252 x B192 x H 82mm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:44.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ca. 2,30 kg</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">WSW 125-6ABEN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wandaufbaulautsprecher A/B 2x6W</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJIDHA" RNoPart="30">
            <Qty>116.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749408002057">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metall-Deckeneinbaulautsprecher für AB-Verkabelung,2x6W,100V, zertifiziert gemäß EN 54-24</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x6W Alarmierungs- Lautsprecher- System, redundante Beschallung, kunststoffbeschichtetes Metallgehäuse mit weißem Metalleinbaurahmen, für mechanisch sicheren Halt in der Decke, 3 Federschnappverschlüsse für schnelle Montage und Anschluss, hochschalldurchlässige Frontabdeckung mit feiner Perforation, 2 Stück leistungsstarke und feuchtigkeitsimprägnierte 6“ Oval- Breitbandchassis mit Hochtonkegel eingebaut, 2 Stück hochwertige 100V-Anpassungs-Übertrager mit je:1/1-1/2-1/4 Leistungsanpassung, sowie 2 integrierte  Keramikklemmen und 2 Thermosicherungen. Mit Feuertopf zur Erhöhung der passiven Sicherheit.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metall- Gehäuse ist mit weißer Kunststoffbeschichtung versehen, geeignet für Wand- und Deckenmontage.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RoHS-Konform.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit (Musik):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 (12)W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen 100V:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 3 1,5 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzbereich:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">       </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">116  20.112 Hz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck 1W/1m/max:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">93,6/109,8 dB</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecher:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 6“ Oval- Breitbandchassis </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Hochtonkegel </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz(Chassis):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 8 Ohm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deckenausschnitt:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ca. 238mm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Gehäuse/Lochblech:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">weiß RAL 9010</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ca.Ø 268 x  217 mm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:50.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ca. 2,1 kg</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CSM 125-6ABEN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Deckeneinbaulautsprecher A/B 2x6W</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJJPPA" RNoPart="40">
            <Qty>4.000</Qty>
            <QtySplit>
             <Qty>4.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>454</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749412002058">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Druckkammerlautsprecher 15 Watt, 100V</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UV-beständiges 15W Druckkammer-System, integrierte Keramikklemme und Thermosicherung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse aus schlagfestem ABS-Kunststoff.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP66 zertifiziert und wetterfest.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wand- und Deckenmontage durch U-förmige, rostfreie V2A-Universalhalterung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluß erfolgt über ein 1 Meter langes herausgeführtes Anschlußkabel.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RoHS-Konform.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">15 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">670 Ohm/100 V</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">15/7,5/3,75/1,9 Watt</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übertragungsbereich:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">330 - 8000 Hz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck (1 W/1 m):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">108 dB</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HSP 15E EN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Druckkammerlautsprecher 15 Watt</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJLLKA" RNoPart="50">
            <Qty>142.000</Qty>
            <QtySplit>
             <Qty>142.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>454</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749418002060">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnungsschild mind. 60 x 20 mm zur dauerhaften Kennzeichnung von Lautsprecher, Verstärker etc. Ausführung als Resopalschild mit weisser Gravur.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschriftung Verstärker: Verstärker-Nr.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschriftung Lautsprecher: Verstärker-Nr.-Lautsprecherkreis-laufende Nummer (Bsp.: V1-K12-06) mit Schrauben montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Kennzeichnungsschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJNGAI" RNoPart="60">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749421002061">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss der neuen Linien an die bestehende SAA-Anlage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Arbeiten erfolgen in Abstimmung und Zusammenarbeit mit der zuständigen Wartungsfirma der bestehenden Anlage.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsumfang:</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abstimmung der Anschlussbedingungen mit der Wartungsfirma</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontrolle der vorhandenen SAA-Anlage auf freie Kapazitäten und geeignete Anschlusspunkte</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss der neuen Leitungen gemäß Herstellerangaben und gültigen Normen</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktionsprüfung der neuen Anlagenteile im Zusammenspiel mit der bestehenden SAA-Anlage</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation und Kennzeichnung der neuen Anschlüsse</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übergabe der Prüfergebnisse und Abstimmungsnachweise an den Auftraggeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Anschluss an die bestehende SAA-Anlage in Abstimmung mit der Wartungsfirma</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFJPAHA" RNoPart="70">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749424002062">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beistellen von Personal für die Sachverständigenabnahme der Sprachalarmierungsanlage , Vergütung des Sachverständigen durch den AG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellen Personal Sachverständigenabn.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGMJAAA" RNoPart="80">
            <Qty>70.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508063220156000003">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SPL-Messung</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruckpegelmessung des Alarmsignals gem. DIN VDE 0833-4 incl. Protokoll, Preis je Messpunkt</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>SPL-Messung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGMKHGI" RNoPart="90">
            <Qty>70.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508063220161000004">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">STI-Messung</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprachverständlichkeitsmessung gem. DIN VDE 0833-4 incl. Protokoll, Preis je Messpunkt</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>STI-Messung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGMMDCI" RNoPart="100">
            <LumpSumItem>Yes</LumpSumItem>
            <Qty>1.000</Qty>
            <QU>psch</QU>
            <Description ID="R20260508063220168000005">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung der Anlagendokumentation</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anfertigung der Bestandspläne mit Darstellung der Positionen im Grundriss</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung der Blockschaltbilder, Stromlaufpläne</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Dokumentation der Gerätehersteller</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bedienungsanleitung des Systems sowie der Komponenten</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ausführung 3-fach gebunden sowie als CD mit allen Unterlagen</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betriebshandbuch für die Sprachalarmzentrale</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betriebs- und Wartungsbuch für die Sprachalarmanlage</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Dokumentation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGIAKKA" RNoPart="110">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749427002063">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inbetriebsetzung der SAZ</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einmessung der SAZ durch Herstellerfirma.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einschl. Hersteller-Zertifikat über die Werksfertigung der Zentraleinheit, sowie eine Einheitlichkeitsbescheinigung des Herstellers des gesamten Beschallungssystems.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellung eines Inbetriebnahmeprotokolls sowie eines Messprotokolls mit mindestens folgenden Angaben:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ruhestromaufnahme im Netzbetrieb</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stromaufnahme im Netzbetrieb im Alarmfall</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Ruhestromaufnahme im Batteriebetrieb</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stromaufnahme im Batteriebetrieb im Alarmfall</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Impedanzen und Leistungen der Lautsprecherlinien</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Impedanzen und Last in W je Arbeitsverstärker </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Funktionsprüfung der Überwachung gem. DIN VDE 0833-4</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die verwendeten Messgeräte für akustische Messungen müssen der Klasse 1 entsprechen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Typen der verwendeten Messgeräte für akustische Messungen, Impedanzen und Batteriestrommessungen sind hier anzugeben:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">akustisches Messsystem</span>
                </p>
                <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Impedanzmessgerät</span>
                </p>
                <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inbetriebsetzung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIBGIDFOI" RNoPart="2">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 456 Gefahren- und Alarmanlagen</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>456</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>456</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <BoQCtgy ID="AAAAAAAAIBGIDPCA" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Brandmeldeanlage</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBGHADOA">
            <PerfNo>8</PerfNo>
            <PerfLbl>Technische Vorbemerkungen</PerfLbl>
            <Description ID="R20260508075507400000136">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nachfolgend ist eine Brandmeldeanlage mit Zentrale nach VDE 0833, DIN 14675, DIN EN 54 und VdS-Richtlinien ausgeschrieben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Brandmeldeanlage mit Zentrale</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507401000137">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzubieten ist ein Ringleitungssystem mit erhöhter Kurzschluss- und Unterbrechungstoleranz durch beidseitige Überwachung jeder Ringleitung (Loop). Für eine maximale Betriebssicherheit sind alle Ringbusteilnehmer mit Kurzschlussisolatoren und Leitungstrenner auszustatten. Bei Drahtbruch, Erdschluss oder anderen Störungen in der Brandmeldeanlage muss die Auslösung des Hauptmelders bzw. der Übertragungseinrichtung (X31) verhindert sein.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ringleitungssystem mit erhöhter Kurzschluss- und Unterbrechungstoleranz</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507401000138">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Brandfrüherkennung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- örtliche Alarmierung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Alarmierung erfolgt durch von der Zentrale abgesetzte akustische Signalgeber.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Weiterleitung der Gefahrenmeldungen und Störmeldungen erfolgt auf die Feuerwehr-Leitstelle des Landkreises. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Überwachung erfolgt in Ringbus- Technologie.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es erfolgt z.Teil eine Vollüberwachung in festgelegten Bereichen und  z.T  Teilüberwachuneng in restlichen Bauabschnitten mit einer generellen flächendeckender Alarmierung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Standort der Brandmelderzentrale ist vorgesehen im tagsüber besetzten Hausmeisterraum EG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Die Funktion der Zentrale ist wie folgt festgelegt:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507402000139">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anlage ist von einem nach DIN 14675 zertifizierten Errichter aufzubauen und in Betrieb zu setzen, inkl. Inbetriebsetzungs- protokoll.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dies setzt eine Zertifizierung nach DIN 14675 voraus. Der Errichter ist bei Angebotsabgabe zu benennen!</span>
                </p>
                <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Errichterfirma:</span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zertifikat DIN 14675:</span>
                </p>
                <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Registrier-Nr.:</span>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <TextComplement MarkLbl="63" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gültig bis: </span>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eine Kopie der Zulassungsurkunde ist dem Angebot beizufügen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingesetzt werden.</span>
                </p>
                <TextComplement MarkLbl="66" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>DIN 14675 zertifizierten Errichter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507403000140">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bezeichnungen und Beschriftungen müssen mit denen in den Zeichnungsunterlagen und Bedienungs- und Wartungsunterlagen übereinstimmen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meldergruppen-Nummern müssen mit Klartextergänzungen im Hinblick auf die bauliche Lage der Gruppen versehen sein (Ortsangaben).</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bezeichnungen und Beschriftungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507406000141">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1. Der Antrag für die Aufschaltung einer Übertragungs-   einrichtung für Brandmeldungen an die Brandmelde- auswerteanlage der Berufsfeuerwehr ist rechtzeitig schriftlich bei der </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzstelle:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Konzzessionär:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu stellen. In Ausnahmefällen ist auch eine telefonische Terminabsprache möglich.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2. Bei Antragstellung für die Aufschaltung der BMZ an die Brandmeldeauswerteanlage sind einzureichen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">a) Fertigstellungsanzeige</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">b) Linienbelegungsverzeichnis</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">c) Prinzipschaltbild (Blockschaltbild)</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">d) Eine schriftliche Erklärung der Fachfirma (Anlage 2), dass die Brandmeldeanlagen den unter Punkt 2.1</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    genannten Bestimmungen sowie den Richtlinien für automatische Brandmeldeanlagen (Form 2095) des </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Verbandes der Schadenversicherer e.V. entspricht. Sind mehrere Firmen an der Errichtung der </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Brandmeldeanlage beteiligt, so hat der Betreiber die Teilbestätigungen vorzulegen. Hierzu ist das Form-</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    blatt der Anlage 2 zu verwenden.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">e) Bei erstmaliger Antragstellung ist der Nachweis zu erbringen, dass die errichtende Fachfirma den </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Anforderungen des Punktes 1.4 genügt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">f) Der Nachweis eines Wartungsvertrages im Sinne des Punktes 2.3 ist zu erbringen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">g) Ein Nachweis im Sinne des Punktes 2.10 ist zu erbringen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3.</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Kontrolle der Brandmeldeanlage am Tag der Inbetriebnahme und Aufschaltung sind ferner der örtlichen Feuerwehr vorzulegen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">a) Wartungsbuch</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">b) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rufnummern und Anschriften von mindestens drei Personen, die nach Auslösung der Brandmeldeanlage </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    telefonisch benachrichtigt werden können.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">c) Linien-Belegungsplan für alle Meldelinien</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">d) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein Einsatz- und Feuerwehrplan nach DIN 14095. Hierfür steht bei der Berufsfeuerwehr, Abt. 37.40 </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Vorbeugender Brandschutz, eine Musterakte zur Verfügung. Die Pläne für die Alarmakte der Feuerwehr </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    sind in der Größe von max. DIN A3 anzufertigen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">e) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist ein (oder wenn notwendig mehrere) Schlüssel für das Objekt bereitzuhalten, der in dem Feuerwehr-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    schlüsselkasten (FSK) hinterlegt werden soll.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4. Bei der Abnahme der Brandmeldeanlage müssen folgende Personen anwesend sein:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Jeweils ein Vertreter des Auftraggebers, der Errichterfirma , des Konzessionärs und der Berufsfeuerwehr</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inbetriebnahme</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507406000142">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vom AN sind nach Beendigung des Abnahmeverfahrens komplette Bestandsunterlagen anzufertigen sowie Prüfprotokolle, Bedienungs- und Wartungsanleitungen und Ersatzteillisten zusammenzustellen und dem Fachingenieur zur Prüfung und Weiterleitung an den AG innerhalb der vertraglich vereinbarten Frist zu übergeben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bestandsunterlagen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507407000143">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle vorgenannten Technischen Forderungen sind, falls nicht anders in den Texten beschrieben, vom Bieter in den Positionen einzukalkulieren und werden somit nicht separat vergütet.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>vorgenannte Technische Forderungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20260508075507408000144">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Brandmeldeanlage muss gemäß VDE 0833, Teil 1, Abs. 5.3.2 und 5.3.4 für Gefahrenmeldeanlagen sowie der Musterbauordnung und den Herstellerrichtlinien durch einen autorisierten Fachbetrieb gewartet werden.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einreichung der Wartungsverträge wie in den zusätzlichen Technischen Vorbemerkungen gefordert !</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wartung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <PerfDescr ID="AAAAAAAAIBGHKNAA">
            <PerfNo>8014</PerfNo>
            <PerfLbl>Hinweis</PerfLbl>
            <Description ID="R20260508075507409000146">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Zuge des Projekts soll die bestehende Brandmeldeanlage erweitert werden. Die Anlage wurde gemäß DIN 14675 errichtet und entspricht den aktuellen sicherheitstechnischen Anforderungen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Sicherstellung der Funktionsfähigkeit sowie zur Wahrung von Garantie- und Gewährleistungsansprüchen darf die Erweiterung ausschließlich mit Produkten des Herstellers </span>
                 <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Esser (FlexES)</span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> erfolgen. Eine Kombination mit Produkten anderer Hersteller ist ausgeschlossen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Erweiterung muss vollständig in das vorhandene System integriert werden, das auf Technik von Esser basiert. Nur so kann der durchgängige Betrieb im einheitlichen Systemverbund gewährleistet werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer hat dies bei der Angebotserstellung zu berücksichtigen und die uneingeschränkte Systemkompatibilität der eingesetzten Komponenten sicherzustellen. Entsprechende Nachweise über die Herstellerkonformität sind mit dem Angebot einzureichen.</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Im Zuge des Projekts soll die bestehende</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Remark ID="AAAAAAAAIBGHPFPI">
            <Description ID="R20260508075507417000148">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zentrale und Zubehör:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>erweiterung Zentrale und Zubehör:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBGHMNFI" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507414000147">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modularer mikroprozessorgesteuerter Brandmelder-Computer. Geprüft und zugelassen entsprechend folgenden Richtlinien und Normen:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VDE 0100 - Allgemeine Bestimmungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VDE 0833 - Gefahrenmeldeanlagen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- DIN 14675 - Aufbau von Brandmeldeanlagen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VdS-Richtlinien</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- EN54 Teil 2,4 und 13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Basisvariante zum Aufbau einer Brandmelderzentrale mit senkrechtem Ausbau für max. 18 Modulsteckplätze für z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">esserbus-Module.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausbau inkl. Energieversorgungsmodul, EV-Anschlußmodul, Gehäuserückwand 2 für senkrechten Einbau, Steuerungs-Modul, Gehäuserahmen, Basis-Modulträger.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Softwareunterstützung für max. 5 Ringleitungen esserbus/esserbus-PLus</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kombinierbare Ring-/Stichleitungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technik mit dezentraler Intelligenz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Frei konfigurierbare Funktionalität</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der eingesetzten Module</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erhöhte Verfügbarkeit durch Not-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">redundanzfunktion der Ringmodule</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrale Notredundanz für Über-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wachungsflächen bis 48.000m² oder mehr</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als 512 Brandmelder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- vernetzbar über Systembus essernet</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bedienfeld mit 5,7&#x22; TFT-Display</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kapazitive Tastatur zur berührungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sensitiven und intuitiven Bedienung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmgesteuertes Nachtdesign mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">interaktivem Tastaturmenü</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnittstellen: essernet, USB,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ethernet, RS 485, TTY</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von ringbusversorgten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischen-, akustischen- und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprachalarmgebern in versch.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierungsber. via esserbus-PLus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kaskadierbare Energieversorgung bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">450 Watt gem.EN54-4</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Länge der Ringleitung (esserbus) bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu 3,5 km</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von verschiedenen Eingangs-/</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangs-Buskopplern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierte Schnittstellen zum Betrieb</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der erforderlichen Feuerwehrperipherie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">z. B. Feuerwehranzeigetableau,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehrbedienfeld</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ereignisspeicher mit 10.000 Einträgen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von VdS-anerkannten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funkkomponenten mit komfortabler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feldstärkemessung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Parametrierung, Kalibrierung und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Programmierung via USB direkt</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Galvanische Trennung der Analogringe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">möglich</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung 230 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennfrequenz 50...60 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom 0,8 A (pro Netzteil)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom: 192 mA (ohne Bedienteil)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">348 mA (mit Bedienteil)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Strom f. ext. Verbraucher 3 x 24 VDC/3 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamt-Ausgangsstrom max. 6A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akkukapazität 2 x 24 V / 24 Ah</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse IP 30</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse ABS, 10% glasfaserverstärkt,V-0</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich Pantone 538</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen (BxHxT) 450x960x185 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808395</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Brandmeldezentrale</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJIAEOA" RNoPart="20">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507421000149">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bedienteil (Human Machine Interface HMI)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit farbfähigem 5,7&#x22; TFT-Display.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingebaut in Frontrahmen des Brandmelde-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Computer inkl. Gehäuseschloß, Scharnier-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einheit und Befestigungsmaterial.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmekmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kapazitive Tastatur zur berührungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sensitiven und intuitiven Bedienung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmgesteuertes Nachtdesign mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">interaktivem Tastaturmenü</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionaler Anschluss einer Gruppen-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einzelanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionale Nutzung als abgesetztes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bedienteil</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- grafikfähig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionale farbliche Darstellung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zugangsebenen über Accesscode</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steuerbar</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionaler Anschluß eines Protokoll-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">druckers</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom ca. 156 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -5 °C ... 45 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe schwarz, ähnlich RAL9005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 1 kg</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B:450 mm H:320 mm T:30 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808324</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Anzeige- und Bedienteil FlexES 5,7&#x22; Anzeige QVGA</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJICGDI" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507425000150">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modulträger in Kunststoff-Montagewanne</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Brandmelder-Computer zur Aufnahme</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von bis zu 4 frei wählbaren Modulen mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steckbaren Anschlussklemmen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 175 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 170 mm H: 120 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 25 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808322</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Erweiterungs-Modulträger 1 (EM1) mit 4 freien Steckplätzen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJIEDOI" RNoPart="40">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507429000151">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1-fach Ringlinien-Modul für max. 127</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Busteilnehmer mit intergrierter Energie-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">versorgung für Prozeßanalogmelder,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein-/Ausgangs-Koppler oder optional für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">busversorgte Signalgeber.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktionserweiterung für busversorgte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierung durch Softwareupgrade</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optional möglich.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- bis zu 3500 m Ringleitungslänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kombinierbare Ring-/Stichleitungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technik</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verknüpfungen sind über Baugruppen u.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkzentralen hinaus möglich</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verwaltung von Funkkomponenten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- permanente Überwachung aller</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschalteten Melder, Koppler und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierungseinrichtungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überwachung der Ringleitungen auf</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kurzschluss, Drahtbruch und Störung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnelle Reaktivierung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">busversorgten Signalgeber nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kurzschluss</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kunststoffschutzgehäuse mit LED-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeigen zur schnellen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Indikation des Betriebszustandes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierte Leitungsisolatoren für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">beidseitigen Leitungsschutz</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">17 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom ca. 17 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 110 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 27 mm H: 93 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 112 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808331</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Modul (ebM) esserbus-Modul (ebM)</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJIGGAI" RNoPart="50">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507432000152">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerk-Interface-Modul für max. 16</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkteilnehmer. Protokoll ähnlich</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 19245 Teil 1 (Profibus)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Topologie: Ringstruktur, Unterbrechungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Kurzschlusstoleranz.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffschutzgehäuse mit LED-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeigen zur schnellen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Indikation des Betriebszustandes</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel IY(St)Y n x 2 x 0,8 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabellänge max. 1000 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(zwischen 2 Teilnehmern)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808340</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>essernet-Modul 62,5 kBd (enM) 62.5kBd</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJIIEII" RNoPart="60">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507437000153">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Komplettes Kunststoffgehäuse zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufnahme von 2 Akkumulatoren 12V/24Ah.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Befestigungsmaterial, ohne</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akkumulatoren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808313</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Akku-Erweiterungsgehäuse für 2 x 12 V/24 Ah</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJIKBII" RNoPart="70">
            <Qty>4.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507439000154">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 018006</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">VdS-Nr.: G104071</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Akku SUN Batterie SB12-24 V0,12 VDC / 24</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJILNJI" RNoPart="80">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507442000155">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragschienen für Wandmontage</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage- und Tragegestell für die Wandmontage von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmelderzentralen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IQ8Control, ES Line, Compact und FlexES Control mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">jeweils drei Gehäuseteilen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einfaches Ausrichten und Befestigen an einer Tragwand</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch horizontale Abstandsstreben, die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach der Montage entfernt werden können, um die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelführung hinter den Gehäusen zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vereinfachen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durch zusätzliche Kabeleinführungen können Leitungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">seitlich aus Kabel- und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationskanälen hinter die BMZ geführt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die BMZ-Gehäuse werden mit metrischen Schrauben am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gestell untereinander befestigt.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anordnung der Käfigmuttern entspricht den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungspunkten für IQ8Control, ES Line,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Compact und FlexES Control.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 744444</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Tragschienen für Wandmontage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJINNHI" RNoPart="90">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507446000156">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zweipoliger Ableiter bestehend aus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Basiselement und gestecktem Schutzmodul,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit potentialfreiem Fernmeldekontakt zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unabhängigen Störungsweiterleitung.</span>
                 <br/>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung: 230 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung AC: 255 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung DC: 255 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennlaststrom AC: 25 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamtableitstoßstrom (80/20)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">[L+N-PE] 5 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kombinierter Stoß: 6 kV</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kombinierter Stoß [L+N-PE]: 10 kV</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzpegel [L/N-PE]: max. 1500 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzpegel [L-N]: max. 1250 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechzeit [L/N-PE]: max. 100 ns</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechzeit [L-N]: max. 25 ns</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: IP 20</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße: B x H x T (mm) 90 x 66 x 18</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 764732</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Überspannungs-Schutzmodul für Netzanschluß 230V</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJAAAA" RNoPart="100">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507451000157">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verbinden Sie das Stromversorgungsmodul mit vier</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mitgelieferten Abstandshaltern und nutzen Sie den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Platz für den Einbau weiterer Komponenten.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808333</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montageplatte für Koppler auf Netzteil Montageplatte für Koppler auf</span>
                  <br/>
                  <span>Netzteil</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJBJNI" RNoPart="110">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507458000158">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multimode LWL Konverter ST für essernet</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der LWL-Konverter setzt elektrische in optische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signale zur störsicheren Datenübertragung unter</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwierigen Umgebungsbedingungen um, bei denen z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Einsatz von Kupferleitungen nicht möglich ist. Der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mischbetrieb von LWL (Lichtwellen-Leiter) und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">konventioneller Verdrahtung innerhalb eines Netzwerkes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ist zulässig.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 784768</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Multimode LWL Konverter ST für essernet Um eine funktionstüchtige</span>
                  <br/>
                  <span>Übertragung der Daten sicherzustellen, müssen an beiden Enden des</span>
                  <br/>
                  <span>Übertragungsweges einheitliche LWL Konverter betrieben werden.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJDIGI" RNoPart="120">
            <Qty>35.000</Qty>
            <QtySplit>
             <Qty>35.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIBJOBHOI</CtlgID>
             <CtlgCode>063</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075507466000159">
             <STLBBau>
              <STLBBauCtlg>
               <CtlgName>STLB-Bau</CtlgName>
               <VersDate>2023-04</VersDate>
               <WCtg>063</WCtg>
               <Group>5042</Group>
              </STLBBauCtlg>
              <STLBBauID>
               <ArtChrIdent>12652</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>90</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>12648</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>5</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>16394</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>1</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>16393</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>2</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>10164</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>1</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>2136</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>15</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>24262</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>0</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
             </STLBBau>
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehr-Laufkarte DIN 14675, Format DIN A3, aus Karton in geschützter Folie,</span>
                 <br/>
                 <TextComplement MarkLbl="1" Kind="Owner">
                  <ComplCaption>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mindestdicke der Karte </span>
                  </ComplCaption>
                  <ComplBody>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;190&#x27;</span>
                  </ComplBody>
                  <ComplTail>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> mym, </span>
                  </ComplTail>
                 </TextComplement>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Grundrisspläne werden im DXF-Format auf Datenträger zur Verfügung gestellt.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Feuerwehr-Laufkarte DIN A3</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJHJGI" RNoPart="130">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507475000161">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beistellen von Personal für die Sachverständigenabnahme der Brandmeldanlage, Vergütung des Sachverständigen durch den AG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellen Personal Sachverständigenabn.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJJFKI" RNoPart="140">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075507480000162">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abnahme der Brandmeldeanlage mit dem Betreiber und der Feuerwehr, einschl. Beistellung von Personal und Werkzeugen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einweisung des Betreibers in Funktion und Bedienung der BMA..</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anlegen eines Betriebshandbuches entsprechend den DIN- und DIN-VDE-Normen, bzw. wenn VDS-Anlage gefordert nach den VDS Richtlinien.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Abnahme/ Einweisung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJLEDI" RNoPart="150">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075507486000163">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation/ Pläne</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung 3-fach, 2-fach auf Datenträger (CD) Zusammenstellen von Anlagenbeschreibung, Bedienungs- und Wartungsanleitungen, Ersatzteilliste mit Fabrikat + Bestellnummer, Schalt- u. Klemmenpläne der eingebauten Geräte, Installationspläne mit Angaben der Haupttrassen, Prinzipschaltpläne, Betriebshandbuch, Meldegruppenverzeichnis entsprechend den gesetzlichen Vorgaben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Dokumentation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJJNDEI" RNoPart="160">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507490000164">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die vorhandene Brandmeldeanlage wird mit der neu zu installierenden BMA vernetzt. Sämtliche Arbeiten erfolgen in enger Abstimmung mit der zuständigen Wartungsfirma sowie dem Hersteller der Bestandsanlage, um eine normgerechte Funktion und eine sichere Kommunikation beider Systeme zu gewährleisten.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsumfang:</span>
                 <br/>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abstimmung und Festlegung der technischen Schnittstellen mit Wartungsfirma und Hersteller</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überprüfung der bestehenden BMA hinsichtlich Anschlussfähigkeit und Kommunikationsschnittstellen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Durchführung von Funktions- und Kommunikationsprüfungen gemäß geltenden Normen und Herstellervorgaben</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung und Aktualisierung der Anlagendokumentation einschließlich Schemata</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Übergabe der Prüfprotokolle sowie aller Abstimmungsunterlagen an den Auftraggeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Vernetzung der bestehenden Brandmeldeanlage (BMA) mit der neu zu errichtenden Anlage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Remark ID="AAAAAAAAIBJKBLFI">
            <Description ID="R20260508075507495000166">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder und Signalgeber:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melder und Signalgeber:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBJJPCGI" RNoPart="170">
            <Qty>14.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507494000165">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multisensormelder mit zwei integrier-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ten optischen Rauchsensoren mit unter-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schiedlichen Streulichtwinkeln sowie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zuzsätzlicher Thermosensor-Auswertung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Erkennung von Schwelbränden bis hin</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu offenen Bränden mit gleich-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mäßigem Ansprechverhalten.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vergleich der Rauchsensorsignale zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rauchklassifizierung und Reduzierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von Täuschungsalarmen, wie z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch Wasserdampf oder Staub.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durch die hervorragenden Detektions-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eigenschaften ist der Melder außerdem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in der Lage, die in der Norm beschriebenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Testfeuer TF1 und TF6 zu erkennen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Melder ist auch für höhere Anwendungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">temperatur bis +65 °C geeignet.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Melder verfügt über eine auto-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">matische Verschmutzungserkennung. Der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Status der Verschmutzung kann über die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Programmier- und Service Software</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausgelesen und angezeigt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Betrieb mit Einzeladressierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Ringbussystemen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Leitungstrenner ist im Melder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Flache Bauweise</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Mikroprozessorgesteuerte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalverarbeitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vollständige Selbstüberwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Verschmutzungserkennung und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhewertnachführung gemäß geltender</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Normen und Richtlinien</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Falschalarmunterdrückung bei Betauung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch spezielle Oberfläche</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Trenner integriert im Melder, nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">pr EN 54-17</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zentrierte 360° Alarmanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Separate Betriebsanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Detektion nach dem Vorwärts- und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rückwärtsstreuprinzip</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vergleich von Brandkenngrößenmustern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN VDE 0833-2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-360° thermische Überwachung mit einem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sensor</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Alarm- und Betriebsdatenspeicherung,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter Betriebsstundenzähler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Möglichkeit der zeit- und ereignisge-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steuerten Sensorabschaltung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zugelassen nach DIN EN 54-7/-5 B /-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Powered Loop Fähig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Kurzschluss-/unterbrechungstolerant</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 8 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 60 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom ohne Kommunikation ca. 18 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungsfläche max. 110 m²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungshöhe max. 12 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftgeschwindigkeit 0 ... 25.4 m/s</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 65 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 43 (mit Sockel + Option)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 110 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikatio EN 54-7/-5 B /-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 49 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(62 mm inkl. Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20105130701</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 802374</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>O2T Multisensor Melder IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKCKCA" RNoPart="180">
            <Qty>119.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507498000167">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multisensormelder mit integriertem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischem Rauchsensor sowie zusätzlicher</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Thermomeldersensor-Auswertung zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erkennung von Schwelbränden bis hin zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">offenen Bränden mit gleichmäßigem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechverhalten.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durch die Detektion über kürzere Wellen-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">längen mittels blauen Lichts, ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder in der Lage kleinste Partikel,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gleichwertig zu einem Ionisationsrauch-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">melder, jedoch ohne einem radioaktiven</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Element zu detektieren. Diese</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eigenschaft ermöglicht eine optimale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erkennung von Flüssigkeitsbränden sowie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die zuverlässige Detektion von offenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Holzbränden. Zusätzlich zu den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">europäischen Bestimmungen, ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder in der Lage das Testfeuer TF1</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(offener Zellulosebrand) zu detektieren.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Aufbau des Wärmemelders gewähr-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">leistet ein gleichmäßiges Ansprechen zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sicheren Detektion von Bränden mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">langsamen und schnellen Temperatur-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">anstiegen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Melder verfügt über eine auto-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">matische Verschmutzungserkennung. Der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Status der Verschmutzung kann über die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Programmier- und Service Software</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausgelesen und angezeigt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Betrieb mit Einzeladressierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Ringbussystemen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Leitungstrenner ist im Melder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Flache Bauweise</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Mikroprozessorgesteuerte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalverarbeitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vollständige Selbstüberwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Verschmutzungserkennung und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhewertnachführung gemäß geltender</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Normen und Richtlinien</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Falschalarmunterdrückung bei Betauung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch spezielle Oberfläche</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Trenner integriert im Melder, nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">pr EN 54-17</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zentrierte 360° Alarmanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Separate Betriebsanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vergleich von Brandkenngrößenmustern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN VDE 0833-2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-360° thermische Überwachung mit einem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sensor</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Alarm- und Betriebsdatenspeicherung,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter Betriebsstundenzähler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Möglichkeit der zeit- und ereignisge-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steuerten Sensorabschaltung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zugelassen nach DIN EN 54-7/-5 A2/-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Powered Loop fähig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Kurzschluss-/unterbrechungstolerant</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 9 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 50 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom ohne Kommunikation ca. 18 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungsfläche max. 110 m²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungshöhe max. 12 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftgeschwindigkeit 0 ... 25.4 m/s</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 43 (mit Sockel + Option)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 110 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-7/-5 A2/-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 49 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(62 mm inkl. Sockel)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 802375</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>OT-blue Multisensor Melder IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFHAAA" RNoPart="190">
            <Qty>92.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508093353844000001">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzlich zur Rauchdetektion mit dem bewährten O²T-Multisensorprinzip ist im Melder eine Blitzleuchte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.Detektion</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multisensormelder mit zwei integrierten optischen Rauchsensoren mit unterschiedlichen Streulichtwinkeln</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sowie zusätzlicher Thermomeldersensorauswertung zur Erkennung von Schwelbränden bis hin zu offenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bränden mit gleichmäßigem Ansprechverhalten. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 8 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC 75 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ BMZAkku ca. 400 µA @ 42 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom 10 mA ... 20 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastfaktor 2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzenergie ca. 3 J</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtstärke max. 15,8 cd peak/2,63 cd effektiv</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzleuchte rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungsfläche 110 m²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungshöhe 12 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftgeschwindigkeit 0 m/s ... 25,4 m/s</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 65 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x3c; 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP43 (mit Sockel + Option)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 145 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-7:2006/-5 B:2000/ -17:2005, CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 59 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbaumaß Ø: 117 mm H: 67 mm (inkl. Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20193130701</span>
                 <br/>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 802383</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>O2T/F Multisensormelder IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKFDCI" RNoPart="200">
            <Qty>225.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507501000168">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standardmeldersockel für automatische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmelder. Bei Entnahme des Melders</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wird der Ringbus autom. geschlossen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Sockel ist eine Melderentnahme-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sicherung enthalten, die bei Bedarf</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">genutzt werden kann.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 72 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen Ø 0,6 mm ... 2 mm²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 60 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 24 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(inkl. Melder 62 mm)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805590</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Meldersockel Standard für Serie IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKHCHI" RNoPart="210">
            <Qty>8.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508075507503000169">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Beschriftungsfeld kann vor oder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach der Installation der Melder in</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der seitlichen Öffnung des Melder-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sockels IQ8Quad befestigt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Kennzeichnung der Melderadresse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Meldergruppe des Brandmelders im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Objekt bei einer Deckenhöhe bis zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3 Meter.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805576</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beschriftung Meldersockel, Packung 10 VPE = 10 STÜCK Zur Beachtung:</span>
                  <br/>
                  <span>Bitte bestellen Sie diesen Artikel ausschließlich in</span>
                  <br/>
                  <span>Verpackungseinheiten - VPE&#x27;s.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKJACI" RNoPart="220">
            <Qty>3.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508075507505000170">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Montageadapter wird zur schnellen und sicheren</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung von Sockeln der Melderserien OPAL, 700, 800</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und ECO 1000 an abgehängte Deckensysteme verwendet. Er</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erspart den Einsatz spezieller Hohlraumbefestigungen,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">denn die Befestigungsschrauben des Sockels werden</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">direkt in die Schlitze des Montageadapters eingedreht.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliche Vorteile bietet der Montageadapter bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fixierung der Kabel, starrer/ flexibler Verlegerohre</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Kabelverschraubungen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LEISTUNGSMERKMALE:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kabeleinführung: uP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Farbe: weiß, ähnlich RAL 9001</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abmessungen (BxHxT): 99 x 49 x 44 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ: 805577</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805577</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montageadapter 10x für Zwischendecken VPE = 10 STÜCK Zur Beachtung:</span>
                  <br/>
                  <span>Bitte bestellen Sie diesen Artikel ausschließlich in</span>
                  <br/>
                  <span>Verpackungseinheiten - VPE&#x27;s.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKKPOI" RNoPart="230">
            <Qty>25.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507508000171">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektronikmodul zum Einbau in ein</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Handmeldergehäuse zur manuellen Auslö-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sung eines Brandalarmes bzw. einer Ge-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">fahrenmeldung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Geeignet zur Anwendung in trockenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Räumen. Ausgestattet mit einem Mikro-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">prozessor verfügt es bereits in</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Grundausführung über eine Alarm-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">speicherung, Alarmanzeige, und die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussmöglichkeit weiterer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">externer Standard-Handmelder.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Betrieb mit Einzeladressierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Ringbussystemen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Leitungstrenner ist im Melder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ohne Busanbindung arbeitet das Modul</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wie ein Standard-Handmelder.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Flache Bauform</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zulassung nach EN54 Teil 11 als</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Handfeuermelder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Steckbare Anschlussklemmen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 2 Kabeleinführungen jeweils oben,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unten und rückseitig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Testfunktion durch Handmelder-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schlüssel</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 8 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 45 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom ohne Kommunikation ca. 18 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmanzeige LED, rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeige LED, grün</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderanzahl/Gruppe 10 Melder/Gruppe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">127 Melder/Ring</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(gemäß VdS)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -30 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen max. 2,5 mm²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(AWG 26-14)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 44 (im Gehäuse),</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 55 (mit Zubehör)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse PC ASA-Kunststoff</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 236 g (mit Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-11, Typ B</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 133 mm H: 133 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 36 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 804905</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>IQ8 Handmelder Elektronikmodul m. Trenner u. ext. D-Linie, ESSER</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKNEDI" RNoPart="240">
            <Qty>25.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507511000172">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse für Handmelder mit Piktogramm nach EN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Teil 11. Im Lieferumfang enthalten sind Glasscheibe und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffschlüssel.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TECHNISCHE DATEN:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schutzart: IP 44 (mit Elektronikmodul)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gehäuse: PC ASA-Kunststoff</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Montage: aP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Farbe: rot ähnlich RAL 3020</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gewicht: ca. 83 g (ohne Elektronikmodul)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abmessungen (BxHxT): 133 x 133 x 36 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:  704900</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 704900</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Handmelder Gehäuse, rot mit Glas, rot, ähnlich RAL 3020</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJKPCPI" RNoPart="250">
            <Qty>1.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508075507516000173">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für Artikel 70490x / 7048xx große Bauform.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HINWEIS:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VPE 10 Stück</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:  704910</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 704910</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ersatzglasscheibe für Handmeldergehäuse (70490x/7048xx) große</span>
                  <br/>
                  <span>Bauform, VPE=10 Stück</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHBCHI" RNoPart="260">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507519000174">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metallschlüssel, Bauform D, für alle</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ESSER Druckknopfmelder und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Springknopfmelder, ausgenommen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ex-Melder 761698.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hinweis: VPE = 10 Stück</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 769911</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Metallschlüssel für Handmelder</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHCOLI" RNoPart="270">
            <Qty>14.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507523000175">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Adressierbarer, vollständig busversorgter und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kurzschluss-/unterbrechungstoleranter optischer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalgeber gem. EN 54?23 mit roter Blitzfarbe zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischen Alarmierung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der optische Signalgeber ist geeignet für quadratische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalisierungsbereiche W?2,4?5,0 bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W?3,6?8.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der optische Signalisierungsbereich ist in 6 Größen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">über tools 8000 konfigurierbar.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalgeber mit flachem Sockel, geeignet für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandmontage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Optional kann der IP Sockel 806202 mit seitlicher</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabeleinführung und höherem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spritzwasserschutz eingesetzt werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Vollständig busversorgter Alarmgeber</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- esserbus®-PLus-Funktionalität</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Energieeffizient</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bis zu 32 Alarmgeber pro esserbus®-PLus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Jeder Alarmgeber mit integriertem Trenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Synchrone Ansteuerung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eigenschaften Optik:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- EN 54-23 konform</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- W Kategorie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Signalisierungsbereich bis zu 8,0 m Raumbreite bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandmontage</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Raumgröße über tools 8000 einstellbar</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Optik</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastfaktor Optik 3 *1 ... 7,9</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzfrequenz ca. 0.5 Hz *1 /1 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzfarbe rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtstärke ca. 6,6 cd eff. *1 / max. 17 cd eff. @</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W-3,6-8</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalisierungsbereich W-2,4-5 / 60 m³ *1 ? W-3,6-8 /</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">230 m³</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage Wand</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spezifikation EN 54-23: 2010 / -17: 2005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Allgemeine technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 14 ... 42 V DC (über esserbus®-PLus)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 55 ?A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ BMZAkku ca. 300 ?A @ 42 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 % (ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 43 *2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 56 mit IP Sockel 806202 *3</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse Kunststoff PC (Polycarbonat)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe rot, ähnlich RAL 3020</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kalotte: transparent / teilgefrostet</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 300 g (mit Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 112 mm H: 78 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ø: 112 mm H: 93 mm (mit IP Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-21429150413</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 807214RR</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>IQ8Alarm Plus Optischer Signalgeber EN54-23, Gehäuse/Blitz: rot/rot</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHHAPI" RNoPart="280">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507530000177">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein-/ Ausgangsbaustein zur Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standard Brandmeldern und konventionel-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ler Alarmierung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Intelligente Baugruppe auf der Analog-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ringleitung zum Anschluss von nicht</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">adressierfähigen Meldern.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit 4 Meldergruppeneingängen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 30 Standardmelder ohne ESK</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 10 Standardmelder mit ESK</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 10 Nichtautomatische oder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technische Alarme pro Gruppe.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zwei Relais in verschiedenen Betriebs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">arten programmierbar.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zwei Gruppen-Abhängigkeit programmierbar</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage auf Hutschienenadapter oder im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandgehäuse möglich.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Konventionelle Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standard - Meldern / Signalgebern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Leitungsüberwachung gem. EN 54-13</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bis zu 1.000 m Leitungslänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierter Linienisolator</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Relaisausgänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Reset Relais Funktion programmierbar</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 10 ... 28 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromaufnahme max. 120 mA @12 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 12 V DC ca. 12 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC/1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -10 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 28 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spezifikation EN 54-17:2005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 82 mm H: 72 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 20 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808623</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus Alarmierungskoppler Typ 4MG2R Ab Firmware Version V</span>
                  <br/>
                  <span>03.01.R000 abwärtskompatibel zu Brandmelderzentralen System 8000</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHJDLI" RNoPart="290">
            <Qty>4.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507534000178">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abschlusselement EOL-I zur Montage am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">letzten Teilnehmer zur Überwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Meldergruppeneingänge bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anbindung von Standard-Brandmeldern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Erkennt zusätzlich schleichende Lei-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">tungsunterbrechungen und Kurzschlüsse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Leitungsüberwachung gemäß EN 54-13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808626</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>EOL-I Abschlusselement für 808623 Koppler Meldergruppen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHLBJI" RNoPart="300">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507537000179">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abschlusselement EOL-O zur Montage am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">letzten Teilnehmer zur Überwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Steuereingänge bei Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">konventionellen Alarmgebern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Erkennt zusätzlich schleichende Lei-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">tungsunterbrechungen und Kurzschlüsse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Leitungsüberwachung gemäß EN 54-13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808624</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>EOL-O Abschlusselement für 808623 Koppler Ausgänge</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHMPHI" RNoPart="310">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507540000180">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoff-Gehäuse zum Einbau von zwei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Platinen mit den Maßen 65 x 72 mm wie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">z.B. eine 92-polige Verteilerplatine.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich RAL 7035</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B:189 mm H:131 mm T:47 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 788600</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Gehäuse für Esserbuskoppler AP-Montage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJHONEI" RNoPart="320">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507544000181">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der IQ8FCT XS kann als FCT (fire control transponder)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Steuerung und Überwachung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzeinrichtungen wie Brandschutzklappen sowie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Technischer Alarmbaustein (TAL) zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachung eines externen Schaltkontaktes eingesetzt</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden. (*) Der Koppler IQ8FCT XS wird</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf der esserbus® / esserbus®-Plus Ringleitung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldesysteme FlexES Control,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IQ8Control und Compact angeschlossen. Der IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verfügt über einen integrierten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungstrenner, einen Kontakteingang, einen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">potentialfreien Relaisausgang und einen Anschluss</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Melderparallelanzeige. Der Koppler benötigt keine</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">separate Spannungsversorgung. In der FCT</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktionalität kann z.B. eine Brandschutzeinrichtung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">an den Relaiskontakt des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschlossen und angesteuert werden. Über den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontakteingang können die Endpositionen z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einer Brandschutzklappe unter Berücksichtigung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">programmierten Laufzeit überwacht werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In der TAL Funktionalität kann ein externer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schaltkontakt an den Eingang des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschaltet und überwacht werden. Bei der Aktivierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">des Schaltkontaktes werden die Adresse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und der programmierte Zusatztext des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angezeigt. Zur Überwachung des Kontaktes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">können das Alarm- und Überwachungsmodul (Art.-Nr.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">804870) oder eine ext.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Widerstandskombination eingesetzt werden. Max.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungslänge bis zum Kontakt beträgt 500</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meter.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur externen Anzeige des Auslösezustandes kann eine</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderparallelanzeige (Art.-Nr. 781804,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">781814 oder 801824) angeschaltet werden (max.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungslänge 100 m). Die Montage kann im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zentralen- oder Verteilergehäuse auf Hutschiene</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erfolgen oder im optionalen Aufputzgehäuse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(siehe Zubehör).</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(*) Zur Ansteuerung von Brandschutzeinrichtungen sind</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die lokalen und regionalen Anforderungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">/ Vorschriften zu beachten.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 127 Koppler je Ringleitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ein Kontakteingang und ein potenzialfreier</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Relaisausgang</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anschluss für Melderparallelanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Spannungsversorgung über den Feldbus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Impulssteuerung des Relaisausgangs</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Laufzeitüberwachung bei Ansteuerungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von Brandschutzklappen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbarer Relaisausgang NO/NC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Impulslänge der Relaisansteuerung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(für zeitbegrenzte Ansteuerungen)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Rückmeldeeingang zur Überwachung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandfallsteuerungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierter Leitungstrenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Steckbare Anschlussklemmen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Montage auf Hutschienen</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 14 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 45 ?A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC / 1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeige grüne LED</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmanzeige rote LED</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen max. 2,5 mm² (AWG 26-14)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -30 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 % (nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 30 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 50 (im Gehäuse M200SMB)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse PC / ASA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich RAL 7035</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 90 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 90 mm H: 93 mm T: 23 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20792130701</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808606</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Koppler IQ8FCT XS</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJEBLPI" RNoPart="330">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507546000182">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modul-Aufputzgehäuse</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für aP-Montage des Kopplers IQ8FCT XS 808606, besteht</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus Gehäuserückteil und Abdeckung.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 160 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 130 mm H: 143 mm T: 49 mm</span>
                 <br/>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: M200SMB</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Aufputzgehäuse für 1x Überwachungs-/ Steuermodul</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJEDEBI" RNoPart="340">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507549000183">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">esserbus®-Koppler-Standard-Schnittstelle (SST) zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschaltung von Löschanlagen an die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldeanlage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">An den esserbus®-Koppler kann eine externe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungsversorgung von 12 V DC oder 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschlossen werden. Für den 12-V-DC-Betrieb ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungskonverter (Art.-Nr. 781336)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erforderlich. Die externe Spannungsversorgung kann</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">überwacht werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 10 ... 28 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 12 V DC ca. 10 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromaufnahme max. 120 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC/1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -10 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 28 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 82 mm H: 72 mm T: 20 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20614130701</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Belegung von nur einer Adresse pro Koppler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 100 Koppler pro Zentrale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 31 Koppler je Ringleitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 32 Koppler pro Meldergruppe</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808613.30</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Koppler SST</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJEFFFI" RNoPart="350">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508075507552000184">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trennerplatine zum Aufstecken für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">alle esserbus®-Koppler als Trenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für die Ausgrenzung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungsfehlern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 788612</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ZusatztrennerPlatine für esserbus-Koppler</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJEHCDI" RNoPart="360">
            <Qty>150.000</Qty>
            <QtySplit>
             <Qty>150.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075507556000185">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderkennzeichnungsschild 60 x 20 mm, Schrifthöhen entsprechend DIN 1450</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung als Resopalschild mit weisser Gravur, mit Schrauben befestigen</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderkennzeichnungsschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJEJAEI" RNoPart="370">
            <Qty>119.000</Qty>
            <QtySplit>
             <Qty>119.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075507561000186">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliches Resopalschild </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Kennzeichnung von Meldern in der Zwischendecke oder im Doppelboden.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Zusätzliches Resopalschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Remark ID="AAAAAAAAIBJLDGPA">
            <Description ID="R20190131094749790002192">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RAS-Komponenten:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>RAS-Komponenten:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBJLECCA" RNoPart="380">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749792002193">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rauchansaugsystem mit gestufter Alarmierung zur aktiven Brandfrühesterkennung für die Raum- und Einrichtungsüberwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ansprechsensibilität des Detektormoduls einstellbar in Stufen </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  bis zu 0,005 % Lichttrübung/ Meter</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Falschalarmunterdrückung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überwachung des Rohrsystems auf Bruch und Verstopfung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- schnelle Inbetriebnahme durch automatische Initialisierung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 5 optische Statusanzeigen an der Gehäusefront für:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Betrieb&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Infoalarm&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Voralarm&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Hauptalarm&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Störung&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anschlussmöglichkeit für eine Parallelanzeige </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bargraphanzeige des aktuellen Rauchpegels</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Elektronische Auswerteeinheit für ein</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Ansaugrohrsystem mit 25 mm Außendurchmesser</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Länge des Systems bis max. 200 m (je nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Rohrtopologie)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Luftstromüberwachung des Ansaugrohrsystems</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- automatischer Abgleich der Luftstromüberwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  an die angeschlossene Ansauganleitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  (Selbstlernfunktion)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anschlussmöglichkeit für die Luftrückführung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Notalarm bei Prozessorausfall</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Versorgungsspannung 24 V DC (14- 30 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stromaufnahme 220 bis 320 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zul. Umgebungstemperatur -20 °C bis + 60 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abmessungen (BxHxT) ca. 200x 113 x 292 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gehäusematerial ABS-Kunststoff</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gehäusefarbe RAL 9018, papyrusweiss</span>
                 <br/>
                 <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                  <ComplCaption>
                   <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                  </ComplCaption>
                  <ComplBody>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                   <br/>
                   <br/>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                  </ComplBody>
                  <ComplTail>
                   <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                  </ComplTail>
                 </TextComplement>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Rauchansaugsystem</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJLFPFA" RNoPart="390">
            <Qty>20.000</Qty>
            <QU>m</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749794002194">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABS Rohr Ø 25 mm als Luftansaugleitung für einen Ansaugrauchmelder, incl. Befestigungsschellen halogenfrei.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ABS Rohr 25 mm</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJLJBNA" RNoPart="400">
            <Qty>8.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749799002196">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABS 90° Bogen D=25mm passend zum Ansaugrohr montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ABS 90° Bogen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJLKKPA" RNoPart="410">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749801002197">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABS T-Stück D=25mm passend zum Ansaugrohr montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ABS T-Stück</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJLMEAA" RNoPart="420">
            <Qty>5.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749804002198">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABS Muffe D=25mm passend zum Ansaugrohr montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ABS Muffe</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJLNNBA" RNoPart="430">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749806002199">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABS Endkappe D=25mm passend zum Ansaugrohr montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ABS Endkappe</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGAOOA" RNoPart="440">
            <Qty>5.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749811002201">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansaugschlauset für Ø 25 mm Rohr</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bestehend aus:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1xT-Stück, </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Polywellschlauch L=3m, </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1x Deckendurchführung mit Verschraubung</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ansaugschlauset für 25 mm Rohr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGCJMI" RNoPart="450">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749813002202">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kugelhahn ABS zur Durchführung von Wartungsarbeiten am vorgenannten Rohrsystem montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Kugelhahn</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGECBA" RNoPart="460">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749815002203">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftfilter für vorgenanntens Rohrsystem für das Herausfiltern von Schmutz- u. Staubpartikel aus der vom Ansaugsystem angesaugten Luft.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Filtereinsätze (1x 60 ppi, 1x 45 ppi, 1x 25ppi)</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße (BxHxT): 122x 96x 194 mm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Temperaturbereich: -30... +60 °C</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäusematerial: ABS-Kunststoff</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Filtermaterial: PUR</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Luftfilter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGFMCA" RNoPart="470">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749818002204">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PVC-Prüfadapter</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Prüfeinrichtung zur schnellen Funktionskontrolle der Detektoreinheiten in Rauchansaugsystemen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbau in Rohrsystem mit D=25 mm</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>PVC-Prüfadapter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGHFGA" RNoPart="480">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749820002205">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">19&#x22;-Stromversorgungseinschub 24 V, 7A für Rauchansaugsysteme</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Batteriegepufferte Stromversorgung im 19&#x22;-Baugruppenträger.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optische Statusanzeigen an der Gehäusefront für &#x22;Betrieb&#x22; und </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  &#x22;Störung&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- potenzialfreier Kontakt für &#x22;Netzstörung&#x22; und &#x22;Akkustörung&#x22;</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Akkusicherung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Akku-Tiefentladungsschutz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- integrierter Überspannungsschutz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Mindestanforderungen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingangsspannung: 230 V, 50 Hz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsaufnahme: 240 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsspannung: 27,8 V DC</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsstrom: 5,8 A</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akku-Ladestrom: 1,2 A</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Akkukapazität: 24 Ah</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebstemperatur: 0 bis +40°C</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung: 30 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße: 3 HE</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäusematerial: Aluminium</span>
                </p>
                <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>19&#x22;-Stromversorgung 24 V</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJGJAIA" RNoPart="490">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749823002206">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akku 12 V, 24 Ah</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsfreier  Bleiakkumulator für die Integration in Notstromversorgungen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kapazität: 12 V DC/ 24 Ah</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße: (LxBxH) ca. 165x 175x 155 mm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht: ca. 8,2 kg</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in vorgenannten 19&#x22;-Wandschrank einbauen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Akku 12 V, 24 Ah</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Remark ID="AAAAAAAAIBJGKKKA">
            <Description ID="R20190131094749825002207">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sonstiges:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Sonstiges:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBGGAFJA" RNoPart="500">
            <Qty>10.000</Qty>
            <QtySplit>
             <Qty>10.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749838002211">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder-Montagesatz zur Montage an waagerechten, schrägen sowie abgehängten Decken bzw. Dächern und senkrechten Wänden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Neigungswinkel-Ausgleich: 0 bis 75 Grad stufenlos</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melder-Montage-Satz D/W</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGGBOFA" RNoPart="510">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094749844002213">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehrleiter mit beiseitig breiten Stufen, Höhe max. 3,5m (Festlegung auf Grundlage der finalen minimalen Deckenhöhen) einschließlich Feuerwehrleiterhalter mit Einbaumöglichkeit eines Halbprofilzylinders der Feuerwehr </span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Feuerwehrleiter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFLAAA" RNoPart="520">
            <Qty>92.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508095652158000005">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderabdeckkappe m. Signalgeb</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderabdeckkappe m. Signalgeb</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFMAAA" RNoPart="530">
            <Qty>133.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508095652381000006">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderabdeckkappe o.Signalgeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderabdeckkappe o.Signalgeber</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
        <BoQCtgy ID="AAAAAAAAIBGGDPMI" RNoPart="2">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Stundenlohnarbeiten</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBGGEJAA">
            <PerfNo>8000</PerfNo>
            <PerfLbl>Ausführungsbeschreibung Stundenlohnarbeiten</PerfLbl>
            <Description ID="R20190131094750315002353">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend angegebenen Kosten für von der Bauleitung angeordnete Stundenlohnarbeiten sind als feste Stundenverrechnungssätze(€/Arbeitsstunden) gem. § 15 Ziff. 1 VOB/B anzubieten. In ihnen sind unaufgegliedert die Lohn- und Gehaltsnebenkosten und Gemeinkostenanteile einschl. der Sozialkassenbeiträge und Vermögenswirksamenleistungen sowie Lohn- und Gehaltsnebenkosten enthalten. Zuschläge für Nacht-, Sonnabend-, Sonntag- und Feiertagsarbeit sind nicht in die Verrechnungssätze einzubeziehen, sondern ggf. gesondert anzuweisen</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>nachfolgend angegebenen Kosten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20190131094750318002354">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Stundenlohnarbeiten dürfen nur nach ausdrücklicher Aufforderung der Bauüberwachung ausgeführt werden.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Sämtliche Stundenlohnarbeiten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20190131094750320002355">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sie sind auf einem Stundennachweiszetteln detailliert mit Namensangabe und Berufsgruppe sowie der im einzelnen verbrauchten Materialien zu erfassen. Die Stundennachweiszettel sind der Bauleitung täglich jeweils vom vorhergehenden Tage zur Anerkennung vorzulegen.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Stundennachweiszetteln</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20190131094750322002356">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Bieter erklärt durch seine Unterschrift unter dem Angebot, dass die Verrechnungssätze unter Beachtung der preisrechtlichen Vorschriften ermittelt wurden und unabhängig von der Anzahl der abzurechnenden Stunden gelten. </span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bieter erklärt durch seine Unterschrift</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Item ID="AAAAAAAAIBGGIDPI" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>h</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094750324002357">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stunden eines System-Technikers auf besondere Anordnung der örtlichen Bauüberwachung zum täglichen Nachweis</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Stunden eines System-Technikers</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
        <BoQCtgy ID="AAAAAAAAIBJELAAA" RNoPart="3">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Inspektion und Wartung</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBJELPMI">
            <PerfNo>1000</PerfNo>
            <PerfLbl>Inspektion und Wartung</PerfLbl>
            <Description ID="R20260508075537245000189">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Kalkulation ist die Beistellung einer qualifizierten Fachkraft durch den Auftraggeber zu berücksichtigen. Durch diese Beistellung wird die Verantwortung des Auftragnehmers nicht beeinflußt.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Inspektions- und Wartungsvertrag wird abgeschlossen für die:</span>
                </p>
                <page/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellung einer qualifizierten Fachkraft bei der Kalkulation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Remark ID="AAAAAAAAIBJENNNI">
            <Description ID="R20260508075537247000190">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsvertrag für die Dauer der Verjährungsfrist zur Mängelbeseitigung [4 Jahre] gemäß VOB/B § 13:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für alle Komponenten der Brandmeldeanlage.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend beschriebenen Wartungsleistungen sind für die in diesem Leistungsverzeichnis ausgeschriebenen betriebstechnischen Anlagen bestimmt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein ausgefülltes und unterschriebenes Exemplar dieses Wartungsvertrages wird erst zur Abnahme in dreifacher Ausfertigung vorgelegt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Störungsdienst wird im Vertrag geregelt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragsumfang umfasst alle gelieferten Anlagen und Anlagenteile des Auftragnehmers ( AN ). Sie sind in der vom AN als Bestandteil der Bedienungs- und Wartungsanleitung mitzuliefernden Bestandsliste zu erfassen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Wartungsumfang ergibt sich aus den Wartungs- und Inspektionsanweisungen und den Arbeitskarten [AMEV] die der AN gemäß Ausschreibung als Bestandteil der Bedienungs- und Wartungsanleitung ausgefüllt mitzuliefern hat. Anlagen und Komponenten die nicht in den Arbeitskarten nach AMEV enthalten sind, werden vom AN sinngemäß ergänzt. Grundlage sind entsprechende DIN-,VdS- und VDE- Regelwerke.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der noch abzuschließende Wartungsvertrag gilt für den Zeitraum der vereinbarten Verjährungsfrist.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verjährungsfrist für Mängelansprüche beträgt 4 Jahre. Die Frist beginnt mit der Abnahme der gesamten Leistung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die v.g. Festlegungen sind Bestandteil des abzuschließenden Wartungsvertrages.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist der Einheitspreis pro Jahr  anzugeben.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Auszahlung der Jahrespauschale erfolgt nach Durchführung der Wartung, aufgrund der jährlichen Rechnungslegung und der Vorlage der Wartungsprotokolle.</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wartungsvertrag</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBJEPDIA" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075537250000191">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 1. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 1. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFBBKI" RNoPart="20">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075537252000192">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 2. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 2. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFCPOI" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075537253000193">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 3. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 3. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBJFEOCI" RNoPart="40">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508075537255000194">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 4. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018 Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 4. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
      <Remark ID="AAAAAAAAIBGGKMDI">
       <Description ID="R20190607093338973000029">
        <CompleteText>
         <DetailTxt>
          <Text>
           <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
            <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">KG 490 Sonstige Maßnahmen für technische Anlagen</span>
           </p>
          </Text>
         </DetailTxt>
         <OutlineText>
          <OutlTxt>
           <TextOutlTxt>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span>KG 490 Sonstige Maßnahmen für technische Anlagen</span>
            </p>
           </TextOutlTxt>
          </OutlTxt>
         </OutlineText>
        </CompleteText>
       </Description>
      </Remark>
      <BoQCtgy ID="AAAAAAAAIBGGLHII" RNoPart="3">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 492 Gerüste</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>492</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>492</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <PerfDescr ID="AAAAAAAAIBGGMAMA">
         <PerfNo>8013</PerfNo>
         <PerfLbl>Technische Forderungen</PerfLbl>
         <Description ID="R20230126092244923000030">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei den in diesem Titel ausgeschriebenen Gerüsten handelt es sich um Elektro-Montagegerüste und/oder Elektro-Montagebühnen für den zeitlich begrenzten Einsatz, deren Arbeitshöhen höher als 2,0 m sind.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>ausgeschriebenen Gerüsten</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20230126092344931000031">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es handelt sich um Regelausführungen nach DIN 4420 bzw. 4422 für mind. 2 Personen mit Werkzeug und Material (je Gerüst bzw. Bühne).</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gerüste müssen mind. Gruppe 3 (200 kg/m2) entsprechen - bei den Bühnen wird die Belastung mit dem Positionstext gefordert.</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die angebotene jeweilige Ausführung ist im Auftragsfall zu bescheinigen - eine statische Berechnung kann dann entfallen bzw. ist bei Nichtbescheinigung durch den AN beizubringen. Ungeachtet dessen, muss im Auftragsfall durch den AN jeweils ein Brauchbarkeitsnachweis nach DIN 4420-1 oder eine Bauartenzulassung (DIB-Berlin) erbracht werden. Die Kosten hierfür sind mit den Einheitspreisen abgegolten.</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Wahl des geeigneten Gerüstes (Systemgerüst, Kupplungsgerüst, Leitergerät aus verz. Stahlrohr oder Aluminium) wird innerhalb der mit diesem LV aufgestellten Forderungen dem Bieter/Auftragnehmer überlassen. </span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Regelausführungen nach DIN 4420 bzw. 4422</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20230126092423652000032">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Neben der Kennzeichnung nach DIN 4420 (ZH 1/534-0) sowie VBG 14 muss zusätzlich eine während der gesamten Vorhaltezeit gut lesbare und eindeutige Identifikation (Name, lfd. Gerüstnummer und Abrechnungsposition des Auftragnehmers) an jedem Gerüst angebracht und gegen Diebstahl und Verfälschung gesichert sein (z.B. abschließbar oder nieten oder schweißen).</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Kennzeichnung nach DIN 4420 (ZH 1/534-0) sowie VBG 14</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20230126092518542000033">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Berechnung der Vorhaltezeit beginnt ab dem Tag der fertigen Gerüstmontage in Wochen. Am Ende der Vorhaltezeit ist jedes Gerüst komplett einschl. aller Hilfseinrichtungen und Verankerungen von der Baustelle zu entfernen. Notwendige Bau-Ausbesserungen hat der Bieter/Auftragnehmer mit den betroffenen Fachfirmen selbst zu regeln. Eine besondere Vergütung dafür erfolgt nicht.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Berechnung Vorhaltezeit</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20230126092606901000034">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montageübliche Gerüstverschmutzungen, wie sie durch die Beschreibungen des LVs auftreten können, hat der Bieter/Auftragnehmer auf seine Kosten zu beseitigen.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Montageübliche Gerüstverschmutzungen</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20230126092651878000035">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verwendung der Gerüste/Bühnen ist vorgesehen:</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im inneren des Baukörpers</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im Baustellenbereich</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im öffentlichen Bereich, der direkt an den die </span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Baustelle angrenzt (Gehweg, Radweg, </span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fahrstreifen eine Straße)</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Verwendung Gerüste/Bühnen</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
        </PerfDescr>
        <BoQCtgy ID="AAAAAAAAIBFKBGEI" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 492 Gerüste</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>492</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>492</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <Item ID="AAAAAAAAIBFKBPHI" RNoPart="10">
            <Qty>2.000</Qty>
            <QtySplit>
             <Qty>2.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>449</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <Description ID="R20190131094751532002759">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montagegerüst gemäß den technischen Forderungen, als fahrbares Gerüst, mit Seitenschutz,</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Plattformhöhe: 3,0 m bis 7,0 m</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Plattformgröße: ca. 2,8 m x 1,8 m (ca. 4,2 m2)</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplett an Verwendungsstellen mehrfach auf- und abbauen, sowie 4 Wochen vorhalten.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montagegerüst, fahrbar, H: 3 - 7 m</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="AAAAAAAAIBFLAAAA" RNoPart="2">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>Bauteil F (Neubau)</span>
      </p>
     </LblTx>
     <BoQBody>
      <Remark ID="AAAAAAAAIBFLAJDI">
       <Description ID="R20251104134315447000005">
        <CompleteText>
         <DetailTxt>
          <Text>
           <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
            <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">KG 450 Kommunikations-, sicherheits- und informationstechnische Anlagen</span>
           </p>
          </Text>
         </DetailTxt>
         <OutlineText>
          <OutlTxt>
           <TextOutlTxt>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span>KG 450 Kommunikations-, sicherheits- und informationstechnische Anlagen</span>
            </p>
           </TextOutlTxt>
          </OutlTxt>
         </OutlineText>
        </CompleteText>
       </Description>
      </Remark>
      <BoQCtgy ID="AAAAAAAAIBFLBFBI" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 453 Zeitdienstanlagen</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>453</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>453</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <BoQCtgy ID="AAAAAAAAIBFLBOEI" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 453 Uhren Innenraum</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>453</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>453</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <Item ID="AAAAAAAAIBFLCHIA" RNoPart="10">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>453</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>453</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>453</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315443000004">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenraum Uhr, rund, doppelseitig, flaches Gehäuse aus weißem, hochwertigem ABS-Kunststoff, Aufgestetzte Acrylglashaube, Durchmesser ca. 30 cm</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit schwarzen Std./Min.-Zeiger mit schwarzen Stunden-/Minutenmarken,  mit DCF Empfänger 230VAC</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Montage-Set zur seitlichen Wandbesfestigung oder Deckenabhängung.</span>
                </p>
                <TextComplement MarkLbl="64" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Innenraum Uhr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIBFLFCBI" RNoPart="2">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 454 Elektroakustische Anlagen</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>454</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>454</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <BoQCtgy ID="AAAAAAAAIBFLFLFA" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 454 Sprachalarmierungsanlage (DIN VDE 0833-4)</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBFLGEII">
            <PerfNo>7416</PerfNo>
            <PerfLbl>Technische Forderungen</PerfLbl>
            <Description ID="R20251104134315451000009">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">A) Vorbemerkungen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für das o.a. Projekt ist eine Anlage zur Sprachalarmierung im Brandfall vorgesehen, die dem neuesten Stand der Technik entsprechen muss. Diese Neuanlage ist mit der bestehenden SAA-Anlage zu vernetzen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">B) Allgemeine Forderungen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es sind in jedem Fall nur voll funktionsfähige Modul-Einrichtungen eines Herstellers anzubieten, auch dann, wenn der Text der Ausschreibung in Bezug auf die unterschiedlichen Systeme der Bieter Anpassungen erfordert. Alle Einbauten müssen mit Gleitschienen im Schrank abgefangen werden, so dass ein einfacher Austausch gewährleistet ist.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Unter Berücksichtigung der Qualitätsanforderungen und der schwierigen akustischen Problematik sind nur werksgefertigte Geräte und Zentraleinrichtungen der Systemanbieter der Leistungsgemeinschaft Beschallungstechnik im ZVEI zugelassen. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Insbesondere hat die Anlage die Richtlinien der Systemnorm DIN VDE 0833 Teil 4 zu entsprechen und soll optional über Fernwartungseinrichtungen verfügen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Komponenten für eine Sprachalarmanlage die automatisch von einer Brandmeldeanlage angesteuert wird muss den gültigen Normen der Reihe EN 54 entsprechen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Sprachalarmzentrale EN54-16, für die Notstromversorgung die EN54-4 und für die Lautsprecher gilt die EN 54-24.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativangebote von Mitgliedern der Leistungsgemeinschaft sind zugelassen, werden aber nur dann gewertet, wenn dem Angebot eine detaillierte fachtechnische Beschreibung mit ausführlichen Unterlagen und Datenblätter beigefügt ist, in der sämtliche zur Beurteilung der Gleichwertigkeit in Qualität und Dimensionierung erforderlichen Fakten erkenntlich sind.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit der Schlussrechnung sind die Bedienungsanleitungen mit Schaltbildern, die genauen Revisionspläne der Leitungsverlegung und die Verteilerbelegungspläne der Anlage in zweifacher Ausfertigung einzureichen. Vom Hersteller der elektroakustischen Geräte ist eine Bescheinigung über die Einheitlichkeit des Systems und die Werksfertigung der Zentraleinrichtungen, sowie eine Bedienungsanleitung beizulegen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">C) Funktionale Forderungen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Sprachalarmzentrale hat in der ersten Ausbaustufe folgende Kennwerte zu erbringen:</span>
                </p>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">60 auf Impedanz, Kurzschluss und Erdschluss überwachte Lautsprecherstromkreise</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">per Glasfaser vernetzbar mit bis zu 253 weiteren Gebäuden</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">freie Konfiguration der Pegel und Frequenzen der Impedanzüberwachung</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">freie Konfiguration der zulässigen Toleranz je Lautsprecherstromkreis</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">32 auf Kurzschluß, Erdschluß und Unterbrechung überwachte Eingänge zur Anschaltung von BMZ Ausgängen oder Hausalarmmeldern</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Digitale 11x4 Audiomatrix</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gleichzeitige Wiedergabe von mindestens 2 Texte in beliebige Bereiche</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3900 W Arbeitsleistung (Dauerleistung, zeitlich unbegrenzt, auch bei Notstrombetrieb)</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachung aller Signalwege, Busverbindungen und Sicherungen innerhalb und außerhalb der Zentrale</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachung der Signalleitung zur BMZ auf Kurzschluss, Erdschluss und Unterbrechung, Fehler auf der Leitung dürfen keinen Alarm auslösen, sondern müssen sofort als Störung gemeldet werden.</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In der Zentrale integrierte Notstromversorgung, die einen unbeaufsichtigten Betrieb von 30 Stunden Betriebsbereitschaft und anschließenden Alarm für 30 Minuten ohne manuelles Eingreifen zur Verfügung stellt. Der Einsatz einer Wandler-USV ist nicht zulässig.</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die internen Verbindungen zwischen den Komponenten und der Notstromversorgung einschließlich Masseleitungen müssen dauerhaft überwacht werden.</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die internen Audiowege vom Systemprozessor / Matrixmischer zu den Verstärkern und Havarieverstärkern müssen dauerhaft überwacht sein.</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anbindung der Sprechstellen bis zu einer Leitungslänge von 1000m in Funktionserhalt muss möglich sein. Die Stromversorgung der Sprechstellen muss notstromgestützt von der Zentrale erfolgen.</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:36pt;font-family:Times New Roman;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der A- und B-Kreis in einem Lautsprecherbereich muss jeweils von einem anderen Verstärker versorgt werden.</span>
                 </li>
                </ul>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anlage ist ausgelegt für bis zu 11176 Lautsprecherstromkreise. Sämtliche Kreise sind beliebig wählbaren Gruppen- und Sammelrufen zuteilbar. Eine Änderung kann nachträglich durch Umprogrammieren (optional auch per Fernwartung) erfolgen. Das anzubietende System ist mit einer Ethernet Schnittstelle  versehen und muss Steuersignale mit externen Systemen über das entsprechende Protokoll austauschen können. Alle Funktionen des Systems müssen per Ethernet steuerbar sein, ebenfalls müssen alle Betriebsstatus und Fehlermeldungen per Ethernet ausgegeben werden. Die im Leistungsverzeichnis beschriebene Anlage ist mit allen erforderlichen Bauteilen und Softwarepaketen bestückt, die zur Funktion der Zentrale einschließlich der Sprechstellen erforderlich sind.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Sprachalarmzentrale muss über ein Konzept zur Wärmeabfuhr verfügen, dass ohne Lüfter in den Schränken auskommt, so dass bei Ausfall eines Lüfters oder dessen Netzversorgung nicht die Betriebssicherheit mehrerer Verstärker oder des Gesamtsystems gefährdet wird.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das komplette System inklusive der Sprechstellen und Tasten sowie Telefoninterface muss über eine einheitliche PC-Software einfach und ohne umstecken von Kabeln zu konfigurieren sein. Die Impedanzen der Lautsprecherlinien müssen in der Software ablesbar und in andere Software exportierbar sein. Diese Funktionen müssen auch per Fernwartung gegeben sein.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das System darf keine frontseitigen Bedienelemente aufweisen, mit denen sich Funktionen ändern oder einstellen lassen. Alle sicherheitsrelevanten Parameter dürfen nur passwortgeschützt über die PC-Software änderbar sein. Alle Einstellungen sind auf dem Bildschirm graphisch darstellbar und müssen in Echtzeit kontrollierbar sein.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Bedienung des Systems inklusive der Programmzuteilung und Lautstärkeregelung muss ausschließlich über die Sprechstellen funktionieren, die zu jedem Zeitpunkt alle Informationen zum Zustand des Systems in Klartext anzeigen müssen. Die angeschlossenen Sprechstellen müssen prozessorgesteuert und mit einer eigenen Watchdog-Überwachungsfunktion ausgestattet sein. Die Funktion aller Tasten ist frei programmierbar, so dass die Sprechstellen auch als Bedieneinheiten für allgemeine Steueraufgaben konfigurierbar sind. Allen Ereignissen muss ihrer Wichtigkeit nach eine Prioritätsstufe durch Programmierung frei zuteilbar sein. Die Zuleitung (8-pol.) ist permanent auf Leitungsunterbrechung und Kurzschluss zu überwachen. Die Mikrofonkapsel ist permanent zu überwachen. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Fehlermeldungen des Systems müssen an allen Sprechstellen in Klartext angezeigt werden. Die Texte der Fehlermeldungen müssen über die PC-Software frei programmierbar sein. Eine Fehleranzeige ausschließlich per LED / Lampe ist nicht zugelassen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">D) Schallpegel und Sprachverständlichkeit</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Beschallungsanlage muss die geforderte Sprachverständlichkeit von mindestens 0,5 STI auf allen Hörflächen erreichen. Ebenfalls ist sicherzustellen dass der Alarmierungspegel auf allen Hörflächen mindestens 75 dB(A) SPL beträgt bzw. mindestens 10 dB über dem jeweiligen Störschallpegel liegt. </span>
                </p>
                <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Falls andere als von der Planung vorgesehene Lautsprechertypen angeboten werden, so ist dem Angebot zwingend eine akustische Simulation beizulegen, aus der zu erkennen ist, dass die erforderlichen Schallpegel und Sprachverständlichkeiten auf allen Hörflächen erreicht werden. Andernfalls kann das Angebot nicht gewertet werden. </span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Hinweise</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315451000010">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle vorgenannten Technischen Forderungen sind, falls nicht anders in den Texten beschrieben, vom Bieter in den Positionen einzukalkulieren und werden somit nicht separat vergütet.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>vorgenannte Technische Forderungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Item ID="AAAAAAAAIBFLJGAI" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104135603435000127">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-indent:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprachalarmzentrale als &#x22;All in One Lösung&#x22;, EN 54-4 und EN 54-16 zertifiziert</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">8xAB (16 Lautsprecher Linien), Leistungsverstärker 3x500W (mit Havarieverstärker), 1xAudio, LCD, Glasfaser-Netzwerkkarte, Feuerwehr Mikrofon, Ladegerät, ohne Akku.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Digitaler Audiobus mit 45 Kanälen und interner Auflösung in 48 kHz /16 bit  4,5&#x22;-LCD-Touchscreen  Impedanz, EOL (End of Line) und Loop Überwachungsverfahren. Bis zu 254 Netzwerkteilnehmer mittels CAT oder LWL Verkabelung vernetzbar, 1 abspielbarer Audio Nachricht, 1 Audio Eingang , 1 Audio Ausgang,  9-fach Eingangsmodul,  5-fach Ausgangs-/Relaismodul, DC Ausgänge 24V/48V,Anschluss für Akku und Temperaturfühler, Feuerwehr Mikrofon, Ladegerät, Alarmmodus-Aktivierungstaste, 3x Frei konfigurierbare Funktionstasten mit LED.                                                                                                                                                             Netzwerkkarte - 2x SFP 1 Gbit, 1x LAN 1 Gbit, 100 Mbit, POE 1x 1 Gbit, 100 Mbit, 1x LAN/WAN 100 Mbit und RS485 Schnittstelle. CPU-Bypass/Notfallmodus (mit gelbe LED), LED-Kontrollanzeigen  Einfache Konfiguration des Gesamtsystems incl. Sprechstellen mittels SELECTOR Software.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecherlinien:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">16</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecherlinien A/B:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">8 </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steuerkontakteingänge:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">9</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steuerkontaktausgänge:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maximale Gesamtleistung:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1000W</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Verstärker:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3 (1x Havarie)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Simultane Nachrichten:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse Schutzklasse:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 30, Wandmontage</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-5 bis + 45°C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nettogewicht:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">31 kg</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen (BxHxT):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">440 x 525 x 350 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwarz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Audioeingänge:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Audioausgänge:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkkarte:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x SFP 1 Gbit, 1x LAN 1 Gbit, 100 Mbit, POE 1x 1 Gbit, 100 Mbit, 1x LAN/WAN 100 Mbit und RS485 Schnittstelle</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GUI:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4,5&#x22; - LCD-Touchscreen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DSP:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">parametrischer 3-Band-Equalizer an jedem Audioeingang, parametrischer 8-Band-Equalizer, Rückkopplungsunterdrücker, Audiobegrenzer und Verzögerungsfunktion an jedem Audioausgang</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akkumulatoren:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nicht enthalten, für 30 Stunden Betriebsbereitschaft und 30 Minuten Betrieb sind 4 Stück 12V / 45Ah erforderlich</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">midiVES 8003 LN</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Sprachalarmzentrale als &#x22;All in One Lösung&#x22;</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFLLDOA" RNoPart="20">
            <Qty>4.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104135603276000126">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Batterie-Modul 12 V/45 Ah</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">VDS zugelassenen Akkumulatoren, entsprechend den geltenden Normen nach DIN 57 510, DIN 43 534, DIN 43 539 Teil 5 und VDE 0510.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Absolut wartungsfreie, lageunabhängige Bleiakkumulatoren in Gitterplatten- und Vliestechnologie mit in Spezialseparatoren befindlichem Elektrolyt.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">M-Akustik oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BATT 45/12</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Batterie-Modul 12 V/45 Ah</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFLMNEA" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104135603093000125">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ethernet Switch mit 8 PoE Ports und 2 SFP Ports</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EN54-16 zertifizierter managed Switch für Hutschienenmontage mit 8 Gbit PoE Ports, max. 120W sowie  SFP Ports für Glasfaser-Module.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IPv6 Ready</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DHCP-Option 82 für IP-Adresszuweisung mit verschiedenen Policies</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x22;</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bandbreitenmanagement verhindert einen unvorhersehbaren Netzwerkstatus.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik  </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GS110TP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ethernet Switch mit 8 PoE Ports und 2 SFP Ports</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFLOGPA" RNoPart="40">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104135602929000124">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SFP LWL-Modul</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SFP Slot-in-Modul für Sprachalarmcontroller, 1 Port 1000BaseSX MultiMode</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SF-MM31002D-GP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>SFP LWL-Modul</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPAAAA" RNoPart="50">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140225006000128">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Voll überwachte Feuerwehr-Sprechstelle zertifiziert nach EN 54-16</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                </p>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tastendesign gem. DIN 14664</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frei programmierbare Tasten</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bis zu 5 Tastenerweiterungen anschließbar</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingebauter Lautsprecher und Intercom-Funktion</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Black-Box Funktion</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CPU - off Alarm Funktion möglich</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkteilnehmer (Kupfer oder LWL)</span>
                 </li>
                 <li>
                  <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                 </li>
                </ul>
                <p style="text-indent:-18pt;margin-left:-34pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                </p>
                <table cellpadding="6">
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungsversorgung</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LAN PoE oder ein EN 54-4 konformes lokales Netzteil, 48 V, 2-Pin-Schraubanschluss</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromaufnahme</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. 266 mA für 48 V / 5 Tasturerweiterungen</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerk</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LWL, UTP Kat.5e</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl Eingänge</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Relaisausgänge</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtleitermodul - Typ des Steckverbinders</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SFP-Modul, SC/LC-Stecker, Multimode-/ Monomodefasern OM2/OM3</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsleistung Monitorlautsprecher</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,5 W</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruckpegel</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">78 dBA (@1m, 1W)</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzgang Feuerwehr- Mikrofon</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">400 Hz - 6 kHz (@3 dB)</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Impedanz</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial Greek;font-size:10pt;Color:rgb(0,0,0);">500 Ù</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge und Typ der Anschlussleitung</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">≥ 1,5 m, spiral</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stecker Feuerwehr-Handmikrofon</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5-polig DIN</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Tasten</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliche 3 Leuchten</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Versorgung, Ausfall, Alarm</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CPU-OFF-Schalter</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schiebeschalter, zweipolig, Signalisierung mit Diode: grün</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebstemperatur</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0°C bis 60°C</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">150x55x210 mm (BxHxT)</span>
                   </p>
                  </td>
                 </tr>
                </table>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">/M-Akustik oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Voll überwachte Feuerwehr-Sprechstelle</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPCFLI" RNoPart="60">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140225596000129">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachte, mikroprozessorgesteuerte Systemsprechstelle</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                </p>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4,5&#x22; - Touch-Screen Display</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frei programmierbare Funktions-Tasten</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Audio-Eingänge für den Anschluss von externen Audio-Quellen</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bis zu 5 Tastenerweiterungen anschließbar</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingebauter Lautsprecher und Intercom-Funktion</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussbuchse für Headset</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-34pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PoE</span>
                 </li>
                 <li>
                  <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                 </li>
                </ul>
                <p style="text-indent:-18pt;margin-left:-34pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                </p>
                <table cellpadding="6">
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungsversorgung</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PoE (RJ45), oder über zusätzlichen Netzteil-Eingang 48 VDC / 15 W</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LCD-Anzeige</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auflösung 272 x 480, 4,5rdquo; Touchscreen</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Audioausgänge</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Kanäle (Monitorlautsprecher, Headset)</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Audioeingänge</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4 Kanäle / 2x Klinkenstecker 3,5 mm</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsleistung Monitorlautsprecher</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,5 W</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruckpegel</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">78 dBA (@1m, 1 W)</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kopfhörerausgang (Headset)</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Klinkenstecker 3,5 mm</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mikrofon</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektret, Schwanenhals</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Tasten</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5 + PushToTalk, zusätzlich drei Kontrollleuchten</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebstemperatur</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-8°C bis 60°C</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">150x55x210 mm (BxHxT)</span>
                   </p>
                  </td>
                 </tr>
                 <tr align="left" valign="top">
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:1;border-right-style:solid;border-right-width:0.50mm;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht</span>
                   </p>
                  </td>
                  <td align="left" valign="top" style="border-left-style:solid;border-left-width:0.50mm;border-right-style:solid;border-right-width:1;border-top-style:solid;border-top-width:1;border-bottom-style:solid;border-bottom-width:1;width:189;">
                   <p style="text-align:left;line-height:13pt;margin-top:0pt;margin-bottom:0pt;">
                    <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1,4 kg</span>
                   </p>
                  </td>
                 </tr>
                </table>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABT-DMS-LCD</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Überwachte, mikroprozessorgesteuerte Systemsprechstelle</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPEIMI" RNoPart="70">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140225768000130">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tastaturerweiterung 20 Tasten</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">jede Erweiterung bietet 20 zusätzliche programmierbare Funktionstasten. Maximal fünf Erweiterungen lassen sich an eine Feuerwehrsprechstelle bzw. Systemsprechstelle anschließen. Eine der Tasten lässt sich gemäß DIN EN 54-16, für einen Dioden Test programmieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Versorgungsquelle RJ45 über DFMS/DMS/DMS-LCD oder 10-Pin-Stiftanschluss</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 31</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tastatur und Kontrollleuchten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Tasten 20</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzahl der Dioden 20 RGB-Dioden + 2- grüne Dioden</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebstemperatur 0°C bis 60°C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuchtigkeit der Umgebung bei der Arbeit 15% bis 80%</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht 1,4 kg</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen 150 (Breite) x 55 (Höhe) x 210 (Tiefe) mm</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ambient SYSTEM/M-Akustik oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ABT-EKB-20M</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Tastaturerweiterung 20 Tasten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPGEEA" RNoPart="80">
            <Qty>3.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140225986000131">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2-Weg Fullrange-Spezialsystem</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit quadratischem Abstrahlverhalten und gleichmäßiger Pegelverteilung innerhalb dieses Areals. EN54-24 zertifiziert, mit zertifizierter Ballwurfsicherheit.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                </p>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">305mm (12&#x22;) Konus-Mid-Bass in einem ventilierten Gehäuse (Bassreflex)</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hochleistungs-Treiber mit 1.3&#x22; Titan-Diaphragma montiert auf einem VI-Horn mit 1&#x22;-Eintrittsöffnung</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch das spezielle VI-Horn wird eine quadratische Fläche mit dem 2-fachen der Montagehöhe in der Breite und dem 3-fachen der Montagehöhe in die Tiefe beschallt, außerdem ergibt sich ein akustischer Frontschatten vom 0,6-fachen der Montagehöhe der Rückkopplungen unterhalb der Box wesentlich reduziert</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierte Frequenzweiche mit einer akustischen Übernahmefrequenz von 1.600 Hz</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">passive Schutzschaltung zum Schutz des HF-Treibers vor Überlastung</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für den Betrieb über einen digitalen System-Controller zur individuellen Anpassung auf den jeweiligen  Montageort vorgesehen</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mehrwinkliges Gehäuse in kompakter Bauweise aus 7-lagigem, 19mm starkem Birkemehrschichtholz</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Strukturlackierung</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die gesamte Frontfläche ist durch ein in Gehäusefarbe lackiertes Stahlgitter in robuster Ausführung geschützt</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">fünf 3/8&#x22;-16-Flugpunkte und zwei Gewinde zur Aufnahme eines schwenkbaren Deckenmontagewinkels</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zertifizierte Ballwurfsicherheit gemäß DIN 18 032, Teil 3, Ausgabe April 1997</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zertifziert nach EN54-24</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-49pt;font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schraubanschlussterminal für Kabelquerschnitte bis 4 mm²</span>
                 </li>
                 <li>
                  <span style="font-family:Arial;Color:rgb(0,0,0);"> </span>
                 </li>
                </ul>
                <p style="text-indent:-18pt;margin-left:-49pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übertragungsbereich (-3dB):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">70 Hz bis 20 kHz</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">300W</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Empfindlichkeit /1W/1m:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">95 dB</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximaler SPL /1m (calc.):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">126 dB</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nominalimpedanz:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">8 Ohm</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">100V-Betrieb:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">150W, 75W mit vorinstalliertem TK-150</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße (BxHxT):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. 411 x 528 x 648 mm</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. 21,8 kg</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:22.50mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwarz oder weiß</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Electro-Voice/M-Akustik oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">EVC-1122-VIBTEN54</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>2-Weg Fullrange-Spezialsystem</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPIDEA" RNoPart="90">
            <Qty>21.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140226129000132">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metall-Deckeneinbau-Lautsprecher für AB-Verkabelung, 2x6W,100V, zertifiziert gemäß EN 54-24</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x6W Alarmierungs- Lautsprecher- System, redundante Beschallung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hochwertiges, montagefreundliches kunststoffbeschichtetes Metallgehäuse mit weißem Metalleinbaurahmen, für mechanisch sicheren Halt in der Decke, 3 Federschnappverschlüsse für schnelle Montage und Anschluss, geeignet für Wiedergabe von Sprache und Musik, hochschalldurchlässige Frontabdeckung mit feiner Perforation, 2 Stück leistungsstarke und feuchtigkeitsimprägnierte 6&#x22; Oval- Breitbandchassis mit Hochtonkegel eingebaut, 2 Stück hochwertige 100V-Anpassungs-Übertrager mit je:1/1-1/2-1/4 Leistungsanpassung, sowie 2 integrierte  Keramikklemmen und 2 Thermosicherungen. Mit Feuertopf zur Erhöhung der passiven Sicherheit.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metall- Gehäuse ist mit weißer Kunststoffbeschichtung versehen, sowie nachträglich </span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in allen RAL- Farben lackierbar, geeignet für Wand- und Deckenmontage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RoHS-Konform.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten :</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit (Musik):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 (12)W</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen 100V:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 x 6 -3 -1,5 W</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzgang:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">120 - 23.500 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übertragungsbereich (-10dB IEC 268-5):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">159 - 16.000 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck 1W/1m IEC 268-5:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">104,8 dB</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck 1W/4m IEC 268-6:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">92,8 dB</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck Pmax/4m IEC 268-7:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">100,5 dB</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Empfindlichkeit 1W/4m EN54-24:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">80,8 dB</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecher:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 6&#x22; Oval-Breitbandchassis mit Hochtonkegel</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz (Chassis):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x 8 Ohm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deckenausschnitt:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">238mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Gehäuse/Lochblech:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">weiß RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ø 268 x  217 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2,1 kg</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CSM 125-6ABEN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Deckeneinbaulautsprecher A/B 2x6W</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGNLEKA" RNoPart="100">
            <Qty>4.000</Qty>
            <QtySplit>
             <Qty>4.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>454</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508063413126000006">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Druckkammerlautsprecher 15 Watt, 100V</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UV-beständiges 15W Druckkammer-System, integrierte Keramikklemme und Thermosicherung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse aus schlagfestem ABS-Kunststoff.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP66 zertifiziert und wetterfest.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wand- und Deckenmontage durch U-förmige, rostfreie V2A-Universalhalterung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluß erfolgt über ein 1 Meter langes herausgeführtes Anschlußkabel.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RoHS-Konform.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">15 W</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">670 Ohm/100 V</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">15/7,5/3,75/1,9 Watt</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übertragungsbereich:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">330 - 8000 Hz</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:40.00mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck (1 W/1 m):</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">108 dB</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HSP 15E EN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Druckkammerlautsprecher 15 Watt</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPKAAI" RNoPart="110">
            <Qty>7.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140226438000133">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wand- und Deckenaufbaulautsprecher für AB-Verkabelung,2x6W,100V, zertifiziert gemäß EN 54-24, ballwurfsicher</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2x6W Alarmierungs- Lautsprecher- System, redundante Beschallung. Hochwertiges, montagefreundliches, sowie resonanzarmes Gehäuse, ballwurfsichere Ausführung, Gehäuse wird mit der Rückwand verschraubt, dadurch auch Deckenmontage möglich, geeignet für Wiedergabe von Sprache und Musik,</span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> hochschalldurchlässige Frontabdeckung mit feiner Perforation, geeignet für horizontale und vertikale Wand oder Deckenmontage.2 Stück leistungsstarke und feuchtigkeitsimprägnierte 5“ Oval- Beitbandchassis mit Hochtonkegel eingebaut, 2 Stück hochwertige 100V-Anpassungs-Übertrager mit je:1/1-1/2-1/4 Leistungsanpassung, sowie 2 integrierte Keramikklemmen und 2 Thermosicherungen. </span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RoHS-Konform.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Technische Daten :</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbelastbarkeit (Musik)....................................................................2 x 6 (15)W</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anpassungen 100V........................................................................2 x 6 3 1,5 W</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzbereich...........................................................................230  18.379 Hz</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruck 1W/1m/max.................................................................... 97,8/112,8dB</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lautsprecher.................................2x 5“ Oval- Breitbandchassis mit Hochtonkegel </span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennimpedanz(Chassis)..........................................................................2x 8 Ohm</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Gehäuse/Lochblech.................................. ..           ..weiß, ähnlich RAL 9016 </span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen.....................................................................L 252 x B192 x H 82mm</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht.........................................................................................................2,30 kg</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">WSW 125-6ABEN54 BWS</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wand- und Deckenaufbaulautsprecher</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPLMOI" RNoPart="120">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140645572000134">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3-Kanal Einbau-Mischvorverstärker</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Mischvorverstärker ist ein universell einsetzbarer UP-AP Mono-Vorverstärker mit zwei Mikrofon- und einem LINE-Eingang (mischbar), eingebautem MP3-Player (SD-Card), einem USB-Interface und BT-Empfänger. Er ist bedienbar durch eine im Lieferumfang enthaltene IR-Fernbedienung. Universelle Anwendung, einfachste Bedienung und eine hohe Übersteuerungsfestigkeit zeichnen den Mischvorverstärker aus. Auf der Frontseite befindet sich das USB-Interface zum Anschluss an den PC (Laptop), ein Slot für die SD-Speicherkarte, ein Display und die Bedienungselemente (PREV-NEXT, START-STOP, PAUSE und REPEAT-Tasten). Mit der IR-Fernbedienung lassen sich alle Funktionen fernsteuern, außerdem kann man zwischen der SD-Card-Schnittstelle und dem USB-Eingang umschalten. Lautstärke und Entzerrung werden mit VOL-LINE und LOW/HIGH-EQ auf der Frontseite des Mischvorverstärker geregelt. Ein Mischbetrieb der RCA-Eingänge (LINE) und USB/SD-Ports ist möglich. Der Mischvorverstärker ist z.B. bestens geeignet für Sportstätten, wo mitgebrachten MP3-Files (auf dem USB-Stick, einer SD-Card oder einer direkten Verbindung über Bluetooth-fähige Geräte) abgespielt werden sollen. Weitere Einsatzmöglichkeiten z.B. in Gaststätten, Multimedia-Räumen, Schulen uvm. Ein weiterer Vorteil des Mischvorverstärker: Er besitzt keine mechanischen Verschleißteile wie es z.B. bei CD-Playern der Fall ist.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-indent:-14pt;margin-left:-56pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                </p>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mik.-Eingänge: symm. 2 x Mik.-Eingänge (0,5 - 5 mV / 1 kOhm), XLR-Norm</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Line-Eingänge: unsymm. 1 x Line-Eingänge 0 dB, 0.775 V / 10 kOhm, CINCH</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Klirrfaktor: unter 0,3 %</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Klangregelung: +/- 12 dB</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Frequenzgang: 40 Hz - 20.000 Hz</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Display: 99 Titel Anzeige mit max. 9:59:59 Zeit-Angabe</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgänge: 1 x symm. 0 dB bzw. +6 dB</span>
                 </li>
                </ul>
                <ul style="text-indent:0pt;margin-left:-56pt;font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">
                 <li>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Phantomspeisung: 18 V</span>
                 </li>
                </ul>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UMX 3-MP3</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>3-Kanal Einbau-Mischvorverstärker</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPNKFA" RNoPart="130">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140645743000135">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UP-Gehäuse für Mischvorverstärker</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur UP Montage des UMX 3-MP3, ohne Abdeckung.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UNIelectronic oder gleichwertig</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">UMX 3-MP3-UP</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und betriebsfertig montieren.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Angebotenes Fabrikat:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:12.50mm 14.90mm 34.90mm 54.90mm 74.90mm 94.90mm 114.90mm 134.90mm 154.90mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Type:</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">............................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>UP-Gehäuse für Mischvorverstärker</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAICAPPDNA" RNoPart="140">
            <LumpSumItem>Yes</LumpSumItem>
            <Qty>1.000</Qty>
            <QU>psch</QU>
            <Description ID="R20251104140645928000136">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inbetriebnahme</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einmessung und Einweisung in die Funktion und Bedienung der Ela- Anlage durch Herstellerfirma.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einschl. Hersteller-Zertifikat über die Werksfertigung der Zentraleinheit, sowie eine Einheitlichkeitsbescheinigung des Herstellers des gesamten Beschallungssystems.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erstellung eines Inbetriebnahmeprotokolls sowie eines Messprotokolls mit mindestens folgenden Angaben:</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ruhestromaufnahme im Netzbetrieb</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stromaufnahme im Netzbetrieb im Alarmfall</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> Ruhestromaufnahme im Batteriebetrieb</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stromaufnahme im Batteriebetrieb im Alarmfall</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Impedanzen und Leistungen der Lautsprecherlinien</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Impedanzen und Last in W je Arbeitsverstärker </span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Funktionsprüfung der Überwachung gem. DIN VDE 0833-4</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die verwendeten Messgeräte für akustische Messungen müssen der Klasse 1 entsprechen.</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Typen der verwendeten Messgeräte für akustische Messungen, Impedanzen und Batteriestrommessungen sind hier anzugeben:</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">akustisches Messsystem</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller:......................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:...............................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Impedanzmessgerät</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller:......................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:...............................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Messgerät Batteriestromaufnahme</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller:.......................................</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:................................................</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inbetriebnahme</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIAOLA" RNoPart="150">
            <Qty>35.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140646099000137">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SPL-Messung</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalldruckpegelmessung des Alarmsignals gem. DIN VDE 0833-4 incl. Protokoll, Preis je Messpunkt</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>SPL-Messung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNICHDA" RNoPart="160">
            <Qty>35.000</Qty>
            <QU>St</QU>
            <Description ID="R20251104140646988000138">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">STI-Messung</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprachverständlichkeitsmessung gem. DIN VDE 0833-4 incl. Protokoll, Preis je Messpunkt</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>STI-Messung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIEAHA" RNoPart="170">
            <LumpSumItem>Yes</LumpSumItem>
            <Qty>1.000</Qty>
            <QU>psch</QU>
            <Description ID="R20251104140647699000139">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einweisung in die Funktion und Bedienung der Sprachalarmanlage durch Herstellerfirma.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Einweisung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIFIEI" RNoPart="180">
            <LumpSumItem>Yes</LumpSumItem>
            <Qty>1.000</Qty>
            <QU>psch</QU>
            <Description ID="R20251104140731367000140">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung der Anlagendokumentation</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anfertigung der Bestandspläne mit Darstellung der Positionen im Grundriss</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung der Blockschaltbilder, Stromlaufpläne</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Dokumentation der Gerätehersteller</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bedienungsanleitung des Systems sowie der Komponenten</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ausführung 3-fach gebunden sowie als CD mit allen Unterlagen</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betriebshandbuch für die Sprachalarmzentrale</span>
                </p>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="margin-left:-70pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betriebs- und Wartungsbuch für die Sprachalarmanlage</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Dokumentation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIHBLI" RNoPart="190">
            <Qty>35.000</Qty>
            <QtySplit>
             <Qty>35.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>454</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315469000019">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennzeichnungsschild mind. 60 x 20 mm zur dauerhaften Kennzeichnung von Lautsprecher, Verstärker etc. Ausführung als Resopalschild mit weisser Gravur.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschriftung Verstärker: Verstärker-Nr.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beschriftung Lautsprecher: Verstärker-Nr.-Lautsprecherkreis-laufende Nummer (Bsp.: V1-K12-06) mit Schrauben montieren.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Kennzeichnungsschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIILNA" RNoPart="200">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315471000020">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kompakter Kombi-Ableiter für elektroakustische Anlagen Kompakter Kombi-Ableiter der Ableiterklasse Type 1 / P2, geprüft nach EN 61643-21 und energetisch koordiniert nach IEC 61643-22</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Schutz von elektroakustischen Anlagen (z.B. Sprachalarmierung, Lautsprechersysteme) zum Schutz von einer Doppelader mit galvanischer Trennung zur direkten oder indirekten Schirmerdung, schnelle und werkzeuglos Montage durch Direkt-Stecktechnik (die Anschlussblöcke können entriegelt und aus dem Gehäuse entnommen werden).</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit Fernmeldekontakt 1 Öffner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Montage auf 35 mm Hutschiene 2TE</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung AC: 100 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung DC: 150 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung AC: 110 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom bei 70 °C: 10 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom bei 80 °C: 7 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">D1 Blitzstoßstrom (10/350 µs) pro Ader: 2,5 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">D1 Blitzstoßstrom (10/350 µs) gesamt: 9 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">C2 Nennableitstoßstrom (8/20 µs) pro Ader: 7,5 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">C2 Nennableitstoßstrom (8/20 µs) gesamt: 22,5 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Grenzfrequenz Ad-Ad: 1,4 MHz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: IP 20</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Kompakter Kombi-Ableiter für 1 DA</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNIKHDA" RNoPart="210">
            <LumpSumItem>Yes</LumpSumItem>
            <Qty>1.000</Qty>
            <QU>psch</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315473000021">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vernetzung der bestehenden SAA mit der neu zu errichtenden SAA-Anlage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Arbeiten erfolgen in enger Abstimmung und Zusammenarbeit mit der Wartungsfirma der bestehenden Anlage, um eine einwandfreie Funktion und Kommunikation beider Systeme sicherzustellen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsumfang:</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abstimmung der technischen Schnittstellen mit der Wartungsfirma und dem Anlagenhersteller</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Prüfung der bestehenden Anlage auf Anschluss- und Kommunikationsmöglichkeiten</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktions- und Kommunikationsprüfung der Gesamtsysteme nach Hersteller- und Normvorgaben</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation der Vernetzung und Aktualisierung der Anlagenschemata</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Übergabe der Prüfergebnisse und Abstimmungsprotokolle an den Auftraggeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Vernetzung bestehender und neuer SAA-Anlage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOLAAA" RNoPart="220">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20260508072714675000133">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beistellen von Personal für die Sachverständigenabnahme der Sprachalarmierungsanlage , Vergütung des Sachverständigen durch den AG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellen Personal Sachverständigenabn.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
        <BoQCtgy ID="AAAAAAAAIBNIODFI" RNoPart="2">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 454 Inspektion und Wartung</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>454</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBNIOMII">
            <PerfNo>12</PerfNo>
            <PerfLbl>Inspektion und Wartung</PerfLbl>
            <Description ID="R20251104134315482000027">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Kalkulation ist die Beistellung einer qualifizierten Fachkraft durch den Auftraggeber zu berücksichtigen. Durch diese Beistellung wird die Verantwortung des Auftragnehmers nicht beeinflußt.</span>
                 <br/>
                </p>
                <page/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellung einer qualifizierten Fachkraft bei der Kalkulation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315483000028">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsvertrag für die Dauer der Verjährungsfrist zur Mängelbeseitigung [4 Jahre] gemäß VOB/B § 13:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für alle Komponenten der Sprachalarmierungsanlage.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend beschriebenen Wartungsleistungen sind für die in diesem Leistungsverzeichnis ausgeschriebenen betriebstechnischen Anlagen bestimmt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Wartungsvertrag für die Sprachalarmierungsanlage wird separat abgeschlossen. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein ausgefülltes und unterschriebenes Exemplar dieses Wartungsvertrages wird erst zur Abnahme in dreifacher Ausfertigung vorgelegt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Störungsdienst wird im Vertrag geregelt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragsumfang umfasst alle gelieferten Anlagen und Anlagenteile des Auftragnehmers ( AN ). Sie sind in der vom AN als Bestandteil der Bedienungs- und Wartungsanleitung mitzuliefernden Bestandsliste zu erfassen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Wartungsumfang ergibt sich aus den Wartungs- und Inspektionsanweisungen und den Arbeitskarten [AMEV] die der AN gemäß Ausschreibung als Bestandteil der Bedienungs- und Wartungsanleitung ausgefüllt mitzuliefern hat. Anlagen und Komponenten die nicht in den Arbeitskarten nach AMEV enthalten sind, werden vom AN sinngemäß ergänzt. Grundlage sind entsprechende DIN-,VdS- und VDE- Regelwerke.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der noch abzuschließende Wartungsvertrag gilt für den Zeitraum der vereinbarten Gewährleistungsfrist.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist der Einheitspreis pro Jahr anzugeben.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Auszahlung der Jahrespauschale erfolgt nach Durchführung der Wartung, aufgrund der jährlichen Rechnungslegung und der Vorlage der Wartungsprotokolle.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wartungsvertrag</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Item ID="AAAAAAAAIBGKBDKI" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315486000029">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 1. Jahr</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inspektion und Wartung der Sprachalarmierungsanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2005. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung SAA komplett 1. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGKCMOA" RNoPart="20">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315488000030">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 2. Jahr</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inspektion und Wartung der Sprachalarmierungsanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2005. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung SAA komplett 2. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGKEGDA" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315490000031">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 3. Jahr</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inspektion und Wartung der Sprachalarmierungsanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2005. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung SAA komplett 3. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGKFPOA" RNoPart="40">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>454</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315492000032">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 4. Jahr</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inspektion und Wartung der Sprachalarmierungsanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2005. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung SAA komplett 4. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIBGKIILI" RNoPart="3">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 456 Gefahren- und Alarmanlagen</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>456</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>456</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <BoQCtgy ID="AAAAAAAAIBGKJBPA" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Brandmeldeanlage</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBGKJLCI">
            <PerfNo>248</PerfNo>
            <PerfLbl>Technische Vorbemerkungen</PerfLbl>
            <Description ID="R20251104134315503000036">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nachfolgend ist eine Brandmeldeanlage mit Zentrale nach VDE 0833, DIN 14675, DIN EN 54 und VdS-Richtlinien ausgeschrieben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Brandmeldeanlage mit Zentrale</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315504000037">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anzubieten ist ein Ringleitungssystem mit erhöhter Kurzschluss- und Unterbrechungstoleranz durch beidseitige Überwachung jeder Ringleitung (Loop). Für eine maximale Betriebssicherheit sind alle Ringbusteilnehmer mit Kurzschlussisolatoren und Leitungstrenner auszustatten. Bei Drahtbruch, Erdschluss oder anderen Störungen in der Brandmeldeanlage muss die Auslösung des Hauptmelders bzw. der Übertragungseinrichtung (X31) verhindert sein.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ringleitungssystem mit erhöhter Kurzschluss- und Unterbrechungstoleranz</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315505000038">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Brandfrüherkennung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- örtliche Alarmierung</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Alarmierung erfolgt durch von der Zentrale abgesetzte akustische Signalgeber.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Weiterleitung der Gefahrenmeldungen und Störmeldungen erfolgt auf die Feuerwehr-Leitstelle des Landkreises. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Überwachung erfolgt in Ringbus- Technologie.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es erfolgt z.Teil eine Vollüberwachung in festgelegten Bereichen und  z.T  Teilüberwachuneng in restlichen Bauabschnitten mit einer generellen flächendeckender Alarmierung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Standort der Brandmelderzentrale ist vorgesehen im tagsüber besetzten Hausmeisterraum EG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Die Funktion der Zentrale ist wie folgt festgelegt:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315506000039">
             <CompleteText>
              <ComplTSB>Yes</ComplTSB>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anlage ist von einem nach DIN 14675 zertifizierten Errichter aufzubauen und in Betrieb zu setzen, inkl. Inbetriebsetzungs- protokoll.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dies setzt eine Zertifizierung nach DIN 14675 voraus. Der Errichter ist bei Angebotsabgabe zu benennen!</span>
                </p>
                <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Errichterfirma:</span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zertifikat DIN 14675:</span>
                </p>
                <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Registrier-Nr.:</span>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <TextComplement MarkLbl="63" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gültig bis: </span>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eine Kopie der Zulassungsurkunde ist dem Angebot beizufügen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingesetzt werden.</span>
                </p>
                <TextComplement MarkLbl="66" Kind="Bidder" Empty="Yes">
                 <ComplCaption>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hersteller und Typ </span>
                 </ComplCaption>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
                  <br/>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
                 </ComplBody>
                 <ComplTail>
                  <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom Bieter einzutragen</span>
                 </ComplTail>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>DIN 14675 zertifizierten Errichter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315507000040">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bezeichnungen und Beschriftungen müssen mit denen in den Zeichnungsunterlagen und Bedienungs- und Wartungsunterlagen übereinstimmen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meldergruppen-Nummern müssen mit Klartextergänzungen im Hinblick auf die bauliche Lage der Gruppen versehen sein (Ortsangaben).</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bezeichnungen und Beschriftungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315508000041">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1. Der Antrag für die Aufschaltung einer Übertragungs-   einrichtung für Brandmeldungen an die Brandmelde- auswerteanlage der Berufsfeuerwehr ist rechtzeitig schriftlich bei der </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzstelle:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Konzzessionär:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu stellen. In Ausnahmefällen ist auch eine telefonische Terminabsprache möglich.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2. Bei Antragstellung für die Aufschaltung der BMZ an die Brandmeldeauswerteanlage sind einzureichen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">a) Fertigstellungsanzeige</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">b) Linienbelegungsverzeichnis</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">c) Prinzipschaltbild (Blockschaltbild)</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">d) Eine schriftliche Erklärung der Fachfirma (Anlage 2), dass die Brandmeldeanlagen den unter Punkt 2.1</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    genannten Bestimmungen sowie den Richtlinien für automatische Brandmeldeanlagen (Form 2095) des </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Verbandes der Schadenversicherer e.V. entspricht. Sind mehrere Firmen an der Errichtung der </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Brandmeldeanlage beteiligt, so hat der Betreiber die Teilbestätigungen vorzulegen. Hierzu ist das Form-</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    blatt der Anlage 2 zu verwenden.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">e) Bei erstmaliger Antragstellung ist der Nachweis zu erbringen, dass die errichtende Fachfirma den </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Anforderungen des Punktes 1.4 genügt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">f) Der Nachweis eines Wartungsvertrages im Sinne des Punktes 2.3 ist zu erbringen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">g) Ein Nachweis im Sinne des Punktes 2.10 ist zu erbringen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3.</span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Kontrolle der Brandmeldeanlage am Tag der Inbetriebnahme und Aufschaltung sind ferner der örtlichen Feuerwehr vorzulegen:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">a) Wartungsbuch</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">b) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rufnummern und Anschriften von mindestens drei Personen, die nach Auslösung der Brandmeldeanlage </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    telefonisch benachrichtigt werden können.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">c) Linien-Belegungsplan für alle Meldelinien</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">d) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein Einsatz- und Feuerwehrplan nach DIN 14095. Hierfür steht bei der Berufsfeuerwehr, Abt. 37.40 </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Vorbeugender Brandschutz, eine Musterakte zur Verfügung. Die Pläne für die Alarmakte der Feuerwehr </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    sind in der Größe von max. DIN A3 anzufertigen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:right 139.20mm;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">e) </span>
                 <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist ein (oder wenn notwendig mehrere) Schlüssel für das Objekt bereitzuhalten, der in dem Feuerwehr-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    schlüsselkasten (FSK) hinterlegt werden soll.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4. Bei der Abnahme der Brandmeldeanlage müssen folgende Personen anwesend sein:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">    Jeweils ein Vertreter des Auftraggebers, der Errichterfirma , des Konzessionärs und der Berufsfeuerwehr</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inbetriebnahme</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315509000042">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vom AN sind nach Beendigung des Abnahmeverfahrens komplette Bestandsunterlagen anzufertigen sowie Prüfprotokolle, Bedienungs- und Wartungsanleitungen und Ersatzteillisten zusammenzustellen und dem Fachingenieur zur Prüfung und Weiterleitung an den AG innerhalb der vertraglich vereinbarten Frist zu übergeben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bestandsunterlagen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315510000043">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle vorgenannten Technischen Forderungen sind, falls nicht anders in den Texten beschrieben, vom Bieter in den Positionen einzukalkulieren und werden somit nicht separat vergütet.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>vorgenannte Technische Forderungen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315511000044">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Brandmeldeanlage muss gemäß VDE 0833, Teil 1, Abs. 5.3.2 und 5.3.4 für Gefahrenmeldeanlagen sowie der Musterbauordnung und den Herstellerrichtlinien durch einen autorisierten Fachbetrieb gewartet werden.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einreichung der Wartungsverträge wie in den zusätzlichen Technischen Vorbemerkungen gefordert !</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wartung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <PerfDescr ID="AAAAAAAAIBNJBNDI">
            <PerfNo>8074</PerfNo>
            <PerfLbl>Hinweis</PerfLbl>
            <Description ID="R20251104134315516000046">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Zuge des Projekts soll die bestehende Brandmeldeanlage erweitert werden. Die Anlage wurde gemäß DIN 14675 errichtet und entspricht den aktuellen sicherheitstechnischen Anforderungen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Sicherstellung der Funktionsfähigkeit sowie zur Wahrung von Garantie- und Gewährleistungsansprüchen darf die Erweiterung ausschließlich mit Produkten des Herstellers </span>
                 <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Esser (FlexES)</span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> erfolgen. Eine Kombination mit Produkten anderer Hersteller ist ausgeschlossen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Erweiterung muss vollständig in das vorhandene System integriert werden, das auf Technik von Esser basiert. Nur so kann der durchgängige Betrieb im einheitlichen Systemverbund gewährleistet werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragnehmer hat dies bei der Angebotserstellung zu berücksichtigen und die uneingeschränkte Systemkompatibilität der eingesetzten Komponenten sicherzustellen. Entsprechende Nachweise über die Herstellerkonformität sind mit dem Angebot einzureichen.</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Im Zuge des Projekts soll die bestehende</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Remark ID="AAAAAAAAIBNJDDKI">
            <Description ID="R20251104134315517000047">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zentrale und Zubehör:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>erweiterung Zentrale und Zubehör:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBNLKAJA" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064044316000061">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modularer mikroprozessorgesteuerter Brandmelder-Computer. Geprüft und zugelassen entsprechend folgenden Richtlinien und Normen:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VDE 0100 - Allgemeine Bestimmungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VDE 0833 - Gefahrenmeldeanlagen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- DIN 14675 - Aufbau von Brandmeldeanlagen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VdS-Richtlinien</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- EN54 Teil 2,4 und 13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Basisvariante zum Aufbau einer Brandmelderzentrale mit senkrechtem Ausbau für max. 18 Modulsteckplätze für z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">esserbus-Module.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausbau inkl. Energieversorgungsmodul, EV-Anschlußmodul, Gehäuserückwand 2 für senkrechten Einbau, Steuerungs-Modul, Gehäuserahmen, Basis-Modulträger.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Softwareunterstützung für max. 5 Ringleitungen esserbus/esserbus-PLus</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kombinierbare Ring-/Stichleitungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technik mit dezentraler Intelligenz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Frei konfigurierbare Funktionalität</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der eingesetzten Module</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erhöhte Verfügbarkeit durch Not-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">redundanzfunktion der Ringmodule</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrale Notredundanz für Über-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wachungsflächen bis 48.000m² oder mehr</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als 512 Brandmelder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- vernetzbar über Systembus essernet</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bedienfeld mit 5,7&#x22; TFT-Display</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kapazitive Tastatur zur berührungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sensitiven und intuitiven Bedienung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmgesteuertes Nachtdesign mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">interaktivem Tastaturmenü</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnittstellen: essernet, USB,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ethernet, RS 485, TTY</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von ringbusversorgten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischen-, akustischen- und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprachalarmgebern in versch.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierungsber. via esserbus-PLus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kaskadierbare Energieversorgung bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">450 Watt gem.EN54-4</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Länge der Ringleitung (esserbus) bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu 3,5 km</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von verschiedenen Eingangs-/</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangs-Buskopplern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierte Schnittstellen zum Betrieb</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der erforderlichen Feuerwehrperipherie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">z. B. Feuerwehranzeigetableau,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehrbedienfeld</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ereignisspeicher mit 10.000 Einträgen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Betrieb von VdS-anerkannten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funkkomponenten mit komfortabler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feldstärkemessung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Parametrierung, Kalibrierung und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Programmierung via USB direkt</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Galvanische Trennung der Analogringe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">möglich</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung 230 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennfrequenz 50...60 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom 0,8 A (pro Netzteil)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausgangsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom: 192 mA (ohne Bedienteil)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">348 mA (mit Bedienteil)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Strom f. ext. Verbraucher 3 x 24 VDC/3 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamt-Ausgangsstrom max. 6A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akkukapazität 2 x 24 V / 24 Ah</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse IP 30</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse ABS, 10% glasfaserverstärkt,V-0</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich Pantone 538</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen (BxHxT) 450x960x185 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808395</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Brandmeldezentrale</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNMMCII" RNoPart="20">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213024000077">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bedienteil (Human Machine Interface HMI)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit farbfähigem 5,7&#x22; TFT-Display.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eingebaut in Frontrahmen des Brandmelde-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Computer inkl. Gehäuseschloß, Scharnier-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einheit und Befestigungsmaterial.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmekmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kapazitive Tastatur zur berührungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sensitiven und intuitiven Bedienung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmgesteuertes Nachtdesign mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">interaktivem Tastaturmenü</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionaler Anschluss einer Gruppen-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einzelanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionale Nutzung als abgesetztes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bedienteil</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- grafikfähig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionale farbliche Darstellung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zugangsebenen über Accesscode</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steuerbar</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- optionaler Anschluß eines Protokoll-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">druckers</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom ca. 156 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -5 °C ... 45 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe schwarz, ähnlich RAL9005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 1 kg</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B:450 mm H:320 mm T:30 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808324</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Anzeige- und Bedienteil FlexES 5,7&#x22; Anzeige QVGA</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNMOCII" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213026000078">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modulträger in Kunststoff-Montagewanne</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Brandmelder-Computer zur Aufnahme</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von bis zu 4 frei wählbaren Modulen mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steckbaren Anschlussklemmen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 175 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 170 mm H: 120 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 25 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808322</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Erweiterungs-Modulträger 1 (EM1) mit 4 freien Steckplätzen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGAADJI" RNoPart="40">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213027000079">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1-fach Ringlinien-Modul für max. 127</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Busteilnehmer mit intergrierter Energie-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">versorgung für Prozeßanalogmelder,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein-/Ausgangs-Koppler oder optional für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">busversorgte Signalgeber.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktionserweiterung für busversorgte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierung durch Softwareupgrade</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optional möglich.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- bis zu 3500 m Ringleitungslänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kombinierbare Ring-/Stichleitungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technik</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verknüpfungen sind über Baugruppen u.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkzentralen hinaus möglich</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Verwaltung von Funkkomponenten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- permanente Überwachung aller</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschalteten Melder, Koppler und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmierungseinrichtungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überwachung der Ringleitungen auf</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kurzschluss, Drahtbruch und Störung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnelle Reaktivierung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">busversorgten Signalgeber nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kurzschluss</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kunststoffschutzgehäuse mit LED-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeigen zur schnellen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Indikation des Betriebszustandes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierte Leitungsisolatoren für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">beidseitigen Leitungsschutz</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">17 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom ca. 17 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 110 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 27 mm H: 93 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 112 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808331</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Modul (ebM) esserbus-Modul (ebM)</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGACCPI" RNoPart="50">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213029000080">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerk-Interface-Modul für max. 16</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzwerkteilnehmer. Protokoll ähnlich</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 19245 Teil 1 (Profibus)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Topologie: Ringstruktur, Unterbrechungs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Kurzschlusstoleranz.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffschutzgehäuse mit LED-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeigen zur schnellen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Indikation des Betriebszustandes</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel IY(St)Y n x 2 x 0,8 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabellänge max. 1000 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(zwischen 2 Teilnehmern)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808340</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>essernet-Modul 62,5 kBd (enM) 62.5kBd</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGAFPPA" RNoPart="60">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213031000082">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Komplettes Kunststoffgehäuse zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufnahme von 2 Akkumulatoren 12V/24Ah.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Befestigungsmaterial, ohne</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Akkumulatoren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808313</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Akku-Erweiterungsgehäuse für 2 x 12 V/24 Ah</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGAHMOI" RNoPart="70">
            <Qty>4.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213032000083">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 018006</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">VdS-Nr.: G104071</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Akku SUN Batterie SB12-24 V0,12 VDC / 24</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGAJJCI" RNoPart="80">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213033000084">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragschienen für Wandmontage</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage- und Tragegestell für die Wandmontage von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmelderzentralen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IQ8Control, ES Line, Compact und FlexES Control mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">jeweils drei Gehäuseteilen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einfaches Ausrichten und Befestigen an einer Tragwand</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch horizontale Abstandsstreben, die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach der Montage entfernt werden können, um die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelführung hinter den Gehäusen zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vereinfachen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durch zusätzliche Kabeleinführungen können Leitungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">seitlich aus Kabel- und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationskanälen hinter die BMZ geführt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die BMZ-Gehäuse werden mit metrischen Schrauben am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gestell untereinander befestigt.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anordnung der Käfigmuttern entspricht den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungspunkten für IQ8Control, ES Line,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Compact und FlexES Control.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 744444</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Tragschienen für Wandmontage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGALIII" RNoPart="90">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213034000085">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zweipoliger Ableiter bestehend aus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Basiselement und gestecktem Schutzmodul,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit potentialfreiem Fernmeldekontakt zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unabhängigen Störungsweiterleitung.</span>
                 <br/>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung: 230 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung AC: 255 V AC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höchste Dauerspannung DC: 255 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennlaststrom AC: 25 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamtableitstoßstrom (80/20)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">[L+N-PE] 5 kA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kombinierter Stoß: 6 kV</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kombinierter Stoß [L+N-PE]: 10 kV</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzpegel [L/N-PE]: max. 1500 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzpegel [L-N]: max. 1250 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechzeit [L/N-PE]: max. 100 ns</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechzeit [L-N]: max. 25 ns</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: IP 20</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maße: B x H x T (mm) 90 x 66 x 18</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 764732</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Überspannungs-Schutzmodul für Netzanschluß 230V</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBGANGOI" RNoPart="100">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213036000086">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verbinden Sie das Stromversorgungsmodul mit vier</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mitgelieferten Abstandshaltern und nutzen Sie den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Platz für den Einbau weiterer Komponenten.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: FX808333</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montageplatte für Koppler auf Netzteil Montageplatte für Koppler auf</span>
                  <br/>
                  <span>Netzteil</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNNIEBI" RNoPart="110">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508064213044000092">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multimode LWL Konverter ST für essernet</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der LWL-Konverter setzt elektrische in optische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signale zur störsicheren Datenübertragung unter</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwierigen Umgebungsbedingungen um, bei denen z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Einsatz von Kupferleitungen nicht möglich ist. Der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mischbetrieb von LWL (Lichtwellen-Leiter) und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">konventioneller Verdrahtung innerhalb eines Netzwerkes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ist zulässig.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 784768</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Multimode LWL Konverter ST für essernet Um eine funktionstüchtige</span>
                  <br/>
                  <span>Übertragung der Daten sicherzustellen, müssen an beiden Enden des</span>
                  <br/>
                  <span>Übertragungsweges einheitliche LWL Konverter betrieben werden.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNJLPKA" RNoPart="120">
            <Qty>10.000</Qty>
            <QtySplit>
             <Qty>10.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIBJOBHOI</CtlgID>
             <CtlgCode>063</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315537000052">
             <STLBBau>
              <STLBBauCtlg>
               <CtlgName>STLB-Bau</CtlgName>
               <VersDate>2023-04</VersDate>
               <WCtg>063</WCtg>
               <Group>5042</Group>
              </STLBBauCtlg>
              <STLBBauID>
               <ArtChrIdent>12652</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>90</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>12648</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>5</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>16394</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>1</ChVIdent>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>16393</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>2</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>10164</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>1</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>2136</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>15</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
              <STLBBauID>
               <ArtChrIdent>24262</ArtChrIdent>
               <ArtChIdx>0</ArtChIdx>
               <ChVIdent>0</ChVIdent>
               <OutlTextPart>Yes</OutlTextPart>
              </STLBBauID>
             </STLBBau>
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehr-Laufkarte DIN 14675, Format DIN A3, aus Karton in geschützter Folie,</span>
                 <br/>
                 <TextComplement MarkLbl="1" Kind="Owner">
                  <ComplCaption>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mindestdicke der Karte </span>
                  </ComplCaption>
                  <ComplBody>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;190&#x27;</span>
                  </ComplBody>
                  <ComplTail>
                   <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> mym, </span>
                  </ComplTail>
                 </TextComplement>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Grundrisspläne werden im DXF-Format auf Datenträger zur Verfügung gestellt.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Feuerwehr-Laufkarte DIN A3</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNJNMEA" RNoPart="130">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315540000053">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hinweisschild nach DIN 4066, mit der Beschriftung &#x22;Brandmelderzentrale&#x22; oder &#x22;BMZ&#x22; oder DIN-gerechtem Symbol</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen: ca. 148 x 420 mm</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Hinweisschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOMAAA" RNoPart="140">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508072744032000134">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beistellen von Personal für die Sachverständigenabnahme der Brandmeldanlage, Vergütung des Sachverständigen durch den AG.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellen Personal Sachverständigenabn.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNKCMKI" RNoPart="150">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315548000056">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abnahme der Brandmeldeanlage mit dem Betreiber und der Feuerwehr, einschl. Beistellung von Personal und Werkzeugen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einweisung des Betreibers in Funktion und Bedienung der BMA..</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anlegen eines Betriebshandbuches entsprechend den DIN- und DIN-VDE-Normen, bzw. wenn VDS-Anlage gefordert nach den VDS Richtlinien.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Abnahme/ Einweisung</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNKEGIA" RNoPart="160">
            <Qty>1.000</Qty>
            <QtySplit>
             <Qty>1.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315550000057">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation/ Pläne</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung 3-fach, 2-fach auf Datenträger (CD) Zusammenstellen von Anlagenbeschreibung, Bedienungs- und Wartungsanleitungen, Ersatzteilliste mit Fabrikat + Bestellnummer, Schalt- u. Klemmenpläne der eingebauten Geräte, Installationspläne mit Angaben der Haupttrassen, Prinzipschaltpläne, Betriebshandbuch, Meldegruppenverzeichnis entsprechend den gesetzlichen Vorgaben.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Dokumentation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOHCJA" RNoPart="170">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508071732094000131">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die vorhandene Brandmeldeanlage wird mit der neu zu installierenden BMA vernetzt. Sämtliche Arbeiten erfolgen in enger Abstimmung mit der zuständigen Wartungsfirma sowie dem Hersteller der Bestandsanlage, um eine normgerechte Funktion und eine sichere Kommunikation beider Systeme zu gewährleisten.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsumfang:</span>
                 <br/>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abstimmung und Festlegung der technischen Schnittstellen mit Wartungsfirma und Hersteller</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überprüfung der bestehenden BMA hinsichtlich Anschlussfähigkeit und Kommunikationsschnittstellen</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Durchführung von Funktions- und Kommunikationsprüfungen gemäß geltenden Normen und Herstellervorgaben</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erstellung und Aktualisierung der Anlagendokumentation einschließlich Schemata</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Übergabe der Prüfprotokolle sowie aller Abstimmungsunterlagen an den Auftraggeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Vernetzung der bestehenden Brandmeldeanlage (BMA) mit der neu zu errichtenden Anlage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Remark ID="AAAAAAAAIBNKGBBA">
            <Description ID="R20251104134315551000058">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder und Signalgeber:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melder und Signalgeber:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBFPEAAA" RNoPart="180">
            <Qty>30.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119276000113">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multisensormelder mit integriertem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischem Rauchsensor sowie zusätzlicher</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Thermomeldersensor-Auswertung zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erkennung von Schwelbränden bis hin zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">offenen Bränden mit gleichmäßigem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ansprechverhalten.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durch die Detektion über kürzere Wellen-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">längen mittels blauen Lichts, ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder in der Lage kleinste Partikel,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gleichwertig zu einem Ionisationsrauch-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">melder, jedoch ohne einem radioaktiven</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Element zu detektieren. Diese</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eigenschaft ermöglicht eine optimale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erkennung von Flüssigkeitsbränden sowie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die zuverlässige Detektion von offenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Holzbränden. Zusätzlich zu den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">europäischen Bestimmungen, ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melder in der Lage das Testfeuer TF1</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(offener Zellulosebrand) zu detektieren.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Aufbau des Wärmemelders gewähr-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">leistet ein gleichmäßiges Ansprechen zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sicheren Detektion von Bränden mit</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">langsamen und schnellen Temperatur-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">anstiegen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Melder verfügt über eine auto-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">matische Verschmutzungserkennung. Der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Status der Verschmutzung kann über die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Programmier- und Service Software</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausgelesen und angezeigt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Betrieb mit Einzeladressierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Ringbussystemen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Leitungstrenner ist im Melder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Flache Bauweise</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Mikroprozessorgesteuerte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalverarbeitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vollständige Selbstüberwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Verschmutzungserkennung und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhewertnachführung gemäß geltender</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Normen und Richtlinien</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Falschalarmunterdrückung bei Betauung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">durch spezielle Oberfläche</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Trenner integriert im Melder, nach</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">pr EN 54-17</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zentrierte 360° Alarmanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Separate Betriebsanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Vergleich von Brandkenngrößenmustern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN VDE 0833-2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-360° thermische Überwachung mit einem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sensor</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Alarm- und Betriebsdatenspeicherung,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integrierter Betriebsstundenzähler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Möglichkeit der zeit- und ereignisge-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">steuerten Sensorabschaltung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Zugelassen nach DIN EN 54-7/-5 A2/-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Powered Loop fähig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Kurzschluss-/unterbrechungstolerant</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 9 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 50 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom ohne Kommunikation ca. 18 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungsfläche max. 110 m²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungshöhe max. 12 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftgeschwindigkeit 0 ... 25.4 m/s</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 43 (mit Sockel + Option)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 110 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-7/-5 A2/-17,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 49 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(62 mm inkl. Sockel)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 802375</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>OT-blue Multisensor Melder IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOPAAA" RNoPart="190">
            <Qty>50.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508093657404000002">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzlich zur Rauchdetektion mit dem bewährten O²T-Multisensorprinzip ist im Melder eine Blitzleuchte</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.Detektion</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multisensormelder mit zwei integrierten optischen Rauchsensoren mit unterschiedlichen Streulichtwinkeln</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sowie zusätzlicher Thermomeldersensorauswertung zur Erkennung von Schwelbränden bis hin zu offenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bränden mit gleichmäßigem Ansprechverhalten. </span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 8 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC 75 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ BMZAkku ca. 400 µA @ 42 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom 10 mA ... 20 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastfaktor 2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzenergie ca. 3 J</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtstärke max. 15,8 cd peak/2,63 cd effektiv</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzleuchte rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungsfläche 110 m²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachungshöhe 12 m</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Luftgeschwindigkeit 0 m/s ... 25,4 m/s</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 65 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x3c; 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP43 (mit Sockel + Option)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 145 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-7:2006/-5 B:2000/ -17:2005, CEA 4021</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 59 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einbaumaß Ø: 117 mm H: 67 mm (inkl. Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20193130701</span>
                 <br/>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 802383</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>O2T/F Multisensormelder IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPFPOA" RNoPart="200">
            <Qty>80.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119277000114">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standardmeldersockel für automatische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmelder. Bei Entnahme des Melders</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wird der Ringbus autom. geschlossen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Sockel ist eine Melderentnahme-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sicherung enthalten, die bei Bedarf</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">genutzt werden kann.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 72 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen Ø 0,6 mm ... 2 mm²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe weiß, ähnlich RAL 9010</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 60 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 117 mm H: 24 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(inkl. Melder 62 mm)</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805590</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Meldersockel Standard für Serie IQ8Quad</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPHGMI" RNoPart="210">
            <Qty>8.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508070119279000115">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Beschriftungsfeld kann vor oder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach der Installation der Melder in</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der seitlichen Öffnung des Melder-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sockels IQ8Quad befestigt werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Kennzeichnung der Melderadresse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Meldergruppe des Brandmelders im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Objekt bei einer Deckenhöhe bis zu</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3 Meter.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805576</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beschriftung Meldersockel, Packung 10 VPE = 10 STÜCK Zur Beachtung:</span>
                  <br/>
                  <span>Bitte bestellen Sie diesen Artikel ausschließlich in</span>
                  <br/>
                  <span>Verpackungseinheiten - VPE&#x27;s.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPJJGI" RNoPart="220">
            <Qty>3.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508070119281000116">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Montageadapter wird zur schnellen und sicheren</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung von Sockeln der Melderserien OPAL, 700, 800</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und ECO 1000 an abgehängte Deckensysteme verwendet. Er</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erspart den Einsatz spezieller Hohlraumbefestigungen,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">denn die Befestigungsschrauben des Sockels werden</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">direkt in die Schlitze des Montageadapters eingedreht.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliche Vorteile bietet der Montageadapter bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fixierung der Kabel, starrer/ flexibler Verlegerohre</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Kabelverschraubungen.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">LEISTUNGSMERKMALE:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kabeleinführung: uP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Farbe: weiß, ähnlich RAL 9001</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abmessungen (BxHxT): 99 x 49 x 44 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ: 805577</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 805577</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montageadapter 10x für Zwischendecken VPE = 10 STÜCK Zur Beachtung:</span>
                  <br/>
                  <span>Bitte bestellen Sie diesen Artikel ausschließlich in</span>
                  <br/>
                  <span>Verpackungseinheiten - VPE&#x27;s.</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPLEPI" RNoPart="230">
            <Qty>5.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119282000117">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektronikmodul zum Einbau in ein</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Handmeldergehäuse zur manuellen Auslö-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sung eines Brandalarmes bzw. einer Ge-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">fahrenmeldung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Geeignet zur Anwendung in trockenen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Räumen. Ausgestattet mit einem Mikro-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">prozessor verfügt es bereits in</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Grundausführung über eine Alarm-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">speicherung, Alarmanzeige, und die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussmöglichkeit weiterer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">externer Standard-Handmelder.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Betrieb mit Einzeladressierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Ringbussystemen.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Leitungstrenner ist im Melder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">integriert.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ohne Busanbindung arbeitet das Modul</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wie ein Standard-Handmelder.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Flache Bauform</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zulassung nach EN54 Teil 11 als</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Handfeuermelder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Steckbare Anschlussklemmen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 2 Kabeleinführungen jeweils oben,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unten und rückseitig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Testfunktion durch Handmelder-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schlüssel</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 8 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 45 µA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmstrom ohne Kommunikation ca. 18 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmanzeige LED, rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeige LED, grün</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderanzahl/Gruppe 10 Melder/Gruppe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">127 Melder/Ring</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(gemäß VdS)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anwendungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -30 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen max. 2,5 mm²</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(AWG 26-14)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 44 (im Gehäuse),</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 55 (mit Zubehör)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse PC ASA-Kunststoff</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 236 g (mit Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderspezifikation EN 54-11, Typ B</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 133 mm H: 133 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 36 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 804905</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>IQ8 Handmelder Elektronikmodul m. Trenner u. ext. D-Linie, ESSER</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPNHDI" RNoPart="240">
            <Qty>5.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119283000118">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse für Handmelder mit Piktogramm nach EN54</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Teil 11. Im Lieferumfang enthalten sind Glasscheibe und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffschlüssel.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TECHNISCHE DATEN:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schutzart: IP 44 (mit Elektronikmodul)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gehäuse: PC ASA-Kunststoff</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Montage: aP</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Farbe: rot ähnlich RAL 3020</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Gewicht: ca. 83 g (ohne Elektronikmodul)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abmessungen (BxHxT): 133 x 133 x 36 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:  704900</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 704900</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Handmelder Gehäuse, rot mit Glas, rot, ähnlich RAL 3020</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFPPFKI" RNoPart="250">
            <Qty>1.000</Qty>
            <QU>PAC</QU>
            <Description ID="R20260508070119285000119">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für Artikel 70490x / 7048xx große Bauform.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HINWEIS:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- VPE 10 Stück</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: HONEYWELL oder gleichwertig</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Typ:  704910</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 704910</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ersatzglasscheibe für Handmeldergehäuse (70490x/7048xx) große</span>
                  <br/>
                  <span>Bauform, VPE=10 Stück</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOBCLI" RNoPart="260">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119286000120">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metallschlüssel, Bauform D, für alle</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ESSER Druckknopfmelder und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Springknopfmelder, ausgenommen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ex-Melder 761698.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hinweis: VPE = 10 Stück</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 769911</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Metallschlüssel für Handmelder</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOCPLI" RNoPart="270">
            <Qty>14.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119287000121">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Adressierbarer, vollständig busversorgter und</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kurzschluss-/unterbrechungstoleranter optischer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalgeber gem. EN 54?23 mit roter Blitzfarbe zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">optischen Alarmierung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der optische Signalgeber ist geeignet für quadratische</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalisierungsbereiche W?2,4?5,0 bis</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W?3,6?8.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der optische Signalisierungsbereich ist in 6 Größen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">über tools 8000 konfigurierbar.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalgeber mit flachem Sockel, geeignet für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandmontage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Optional kann der IP Sockel 806202 mit seitlicher</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabeleinführung und höherem</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spritzwasserschutz eingesetzt werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Vollständig busversorgter Alarmgeber</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- esserbus®-PLus-Funktionalität</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Energieeffizient</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bis zu 32 Alarmgeber pro esserbus®-PLus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Jeder Alarmgeber mit integriertem Trenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Synchrone Ansteuerung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Eigenschaften Optik:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- EN 54-23 konform</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- W Kategorie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Signalisierungsbereich bis zu 8,0 m Raumbreite bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandmontage</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Raumgröße über tools 8000 einstellbar</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Optik</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastfaktor Optik 3 *1 ... 7,9</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzfrequenz ca. 0.5 Hz *1 /1 Hz</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blitzfarbe rot</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lichtstärke ca. 6,6 cd eff. *1 / max. 17 cd eff. @</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W-3,6-8</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Signalisierungsbereich W-2,4-5 / 60 m³ *1 ? W-3,6-8 /</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">230 m³</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage Wand</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spezifikation EN 54-23: 2010 / -17: 2005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Allgemeine technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 14 ... 42 V DC (über esserbus®-PLus)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 55 ?A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ BMZAkku ca. 300 ?A @ 42 V</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 % (ohne Betauung)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 43 *2</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 56 mit IP Sockel 806202 *3</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse Kunststoff PC (Polycarbonat)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe rot, ähnlich RAL 3020</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kalotte: transparent / teilgefrostet</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 300 g (mit Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen Ø: 112 mm H: 78 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ø: 112 mm H: 93 mm (mit IP Sockel)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-21429150413</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 807214RR</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>IQ8Alarm Plus Optischer Signalgeber EN54-23, Gehäuse/Blitz: rot/rot</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOFDOI" RNoPart="280">
            <Qty>14.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119289000122">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stahlkorb zum Schutz vor Beschädigung und gegen unbefugtes Entfernen des Gerätes. Auf Ballwurfsicherheit geprüft nach DIN 18032-3:2023-12.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 781551</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Ballwurfsicherer Schutzkorb</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOGPOI" RNoPart="290">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119290000123">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein-/ Ausgangsbaustein zur Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standard Brandmeldern und konventionel-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ler Alarmierung.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Intelligente Baugruppe auf der Analog-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ringleitung zum Anschluss von nicht</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">adressierfähigen Meldern.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit 4 Meldergruppeneingängen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 30 Standardmelder ohne ESK</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 10 Standardmelder mit ESK</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- max. 10 Nichtautomatische oder</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technische Alarme pro Gruppe.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zwei Relais in verschiedenen Betriebs-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">arten programmierbar.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zwei Gruppen-Abhängigkeit programmierbar</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montage auf Hutschienenadapter oder im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandgehäuse möglich.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Konventionelle Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Standard - Meldern / Signalgebern</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Leitungsüberwachung gem. EN 54-13</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Bis zu 1.000 m Leitungslänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierter Linienisolator</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Relaisausgänge</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Reset Relais Funktion programmierbar</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 10 ... 28 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromaufnahme max. 120 mA @12 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 12 V DC ca. 12 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC/1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -10 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte max. 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 28 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spezifikation EN 54-17:2005</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 82 mm H: 72 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">T: 20 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808623</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus Alarmierungskoppler Typ 4MG2R Ab Firmware Version V</span>
                  <br/>
                  <span>03.01.R000 abwärtskompatibel zu Brandmelderzentralen System 8000</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOJBII" RNoPart="300">
            <Qty>4.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119291000124">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abschlusselement EOL-I zur Montage am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">letzten Teilnehmer zur Überwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Meldergruppeneingänge bei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anbindung von Standard-Brandmeldern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Erkennt zusätzlich schleichende Lei-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">tungsunterbrechungen und Kurzschlüsse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Leitungsüberwachung gemäß EN 54-13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808626</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>EOL-I Abschlusselement für 808623 Koppler Meldergruppen</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOKPEI" RNoPart="310">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119293000125">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abschlusselement EOL-O zur Montage am</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">letzten Teilnehmer zur Überwachung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Steuereingänge bei Anbindung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">konventionellen Alarmgebern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Erkennt zusätzlich schleichende Lei-</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">tungsunterbrechungen und Kurzschlüsse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-Leitungsüberwachung gemäß EN 54-13</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808624</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>EOL-O Abschlusselement für 808623 Koppler Ausgänge</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOMNAI" RNoPart="320">
            <Qty>2.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119294000126">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoff-Gehäuse zum Einbau von zwei</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Platinen mit den Maßen 65 x 72 mm wie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">z.B. eine 92-polige Verteilerplatine.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten:</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material ABS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich RAL 7035</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B:189 mm H:131 mm T:47 mm</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 788600</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Gehäuse für Esserbuskoppler AP-Montage</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNOOKKI" RNoPart="330">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119296000127">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der IQ8FCT XS kann als FCT (fire control transponder)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Steuerung und Überwachung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzeinrichtungen wie Brandschutzklappen sowie</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Technischer Alarmbaustein (TAL) zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überwachung eines externen Schaltkontaktes eingesetzt</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden. (*) Der Koppler IQ8FCT XS wird</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf der esserbus® / esserbus®-Plus Ringleitung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldesysteme FlexES Control,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IQ8Control und Compact angeschlossen. Der IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verfügt über einen integrierten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungstrenner, einen Kontakteingang, einen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">potentialfreien Relaisausgang und einen Anschluss</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Melderparallelanzeige. Der Koppler benötigt keine</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">separate Spannungsversorgung. In der FCT</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Funktionalität kann z.B. eine Brandschutzeinrichtung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">an den Relaiskontakt des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschlossen und angesteuert werden. Über den</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontakteingang können die Endpositionen z.B.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einer Brandschutzklappe unter Berücksichtigung der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">programmierten Laufzeit überwacht werden.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In der TAL Funktionalität kann ein externer</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schaltkontakt an den Eingang des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschaltet und überwacht werden. Bei der Aktivierung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">des Schaltkontaktes werden die Adresse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und der programmierte Zusatztext des IQ8FCT XS</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angezeigt. Zur Überwachung des Kontaktes</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">können das Alarm- und Überwachungsmodul (Art.-Nr.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">804870) oder eine ext.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Widerstandskombination eingesetzt werden. Max.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungslänge bis zum Kontakt beträgt 500</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meter.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur externen Anzeige des Auslösezustandes kann eine</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderparallelanzeige (Art.-Nr. 781804,</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">781814 oder 801824) angeschaltet werden (max.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungslänge 100 m). Die Montage kann im</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zentralen- oder Verteilergehäuse auf Hutschiene</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erfolgen oder im optionalen Aufputzgehäuse</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(siehe Zubehör).</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(*) Zur Ansteuerung von Brandschutzeinrichtungen sind</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die lokalen und regionalen Anforderungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">/ Vorschriften zu beachten.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 127 Koppler je Ringleitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Ein Kontakteingang und ein potenzialfreier</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Relaisausgang</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Anschluss für Melderparallelanzeige</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Spannungsversorgung über den Feldbus</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Impulssteuerung des Relaisausgangs</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Laufzeitüberwachung bei Ansteuerungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von Brandschutzklappen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbarer Relaisausgang NO/NC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Programmierbare Impulslänge der Relaisansteuerung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(für zeitbegrenzte Ansteuerungen)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Rückmeldeeingang zur Überwachung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandfallsteuerungen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Integrierter Leitungstrenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Steckbare Anschlussklemmen</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Montage auf Hutschienen</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 14 ... 42 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 19 V DC ca. 45 ?A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC / 1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsanzeige grüne LED</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alarmanzeige rote LED</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussklemmen max. 2,5 mm² (AWG 26-14)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -20 °C ... 70 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -30 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 % (nicht kondensierend)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 30 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 50 (im Gehäuse M200SMB)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gehäuse PC / ASA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe grau, ähnlich RAL 7035</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 90 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 90 mm H: 93 mm T: 23 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20792130701</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808606</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Koppler IQ8FCT XS</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOBCJI" RNoPart="340">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119297000128">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Modul-Aufputzgehäuse</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für aP-Montage des Kopplers IQ8FCT XS 808606, besteht</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus Gehäuserückteil und Abdeckung.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 160 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 130 mm H: 143 mm T: 49 mm</span>
                 <br/>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: M200SMB</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Aufputzgehäuse für 1x Überwachungs-/ Steuermodul</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOCPOI" RNoPart="350">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119299000129">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">esserbus®-Koppler-Standard-Schnittstelle (SST) zur</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschaltung von Löschanlagen an die</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldeanlage.</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">An den esserbus®-Koppler kann eine externe</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungsversorgung von 12 V DC oder 24 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeschlossen werden. Für den 12-V-DC-Betrieb ist der</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spannungskonverter (Art.-Nr. 781336)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erforderlich. Die externe Spannungsversorgung kann</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">überwacht werden.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Technische Daten</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung 10 ... 28 V DC</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ruhestrom @ 12 V DC ca. 10 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromaufnahme max. 120 mA</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kontaktbelastung Relais 30 V DC/1 A</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungstemperatur -10 °C ... 50 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lagertemperatur -25 °C ... 75 °C</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rel. Luftfeuchte &#x26;lt; 95 %</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart IP 40 (im Gehäuse)</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewicht ca. 28 g</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abmessungen B: 82 mm H: 72 mm T: 20 mm</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungserklärung DoP-20614130701</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Belegung von nur einer Adresse pro Koppler</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 100 Koppler pro Zentrale</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 31 Koppler je Ringleitung</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Max. 32 Koppler pro Meldergruppe</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 808613.30</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>esserbus-Koppler SST</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFOFAPI" RNoPart="360">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508070119300000130">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trennerplatine zum Aufstecken für</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">alle esserbus®-Koppler als Trenner</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für die Ausgrenzung von</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungsfehlern.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fabrikat: ESSER</span>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Artikel: 788612</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alternativ:________________________________</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und montieren:</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>ZusatztrennerPlatine für esserbus-Koppler</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNPFFCA" RNoPart="370">
            <Qty>70.000</Qty>
            <QtySplit>
             <Qty>70.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315583000067">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderkennzeichnungsschild 60 x 20 mm, Schrifthöhen entsprechend DIN 1450</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung als Resopalschild mit weisser Gravur, mit Schrauben befestigen</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderkennzeichnungsschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBNPHABI" RNoPart="380">
            <Qty>30.000</Qty>
            <QtySplit>
             <Qty>30.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>456</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315585000068">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zusätzliches Resopalschild </span>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Kennzeichnung von Meldern in der Zwischendecke oder im Doppelboden.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Zusätzliches Resopalschild</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Remark ID="AAAAAAAAIBGJAAAA">
            <Description ID="R20251104134315622000084">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sonstiges:</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Sonstiges:</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBGJHADA" RNoPart="390">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315635000089">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuerwehrleiter mit beiseitig breiten Stufen, Höhe max. 3,5m (Festlegung auf Grundlage der finalen minimalen Deckenhöhen) einschließlich Feuerwehrleiterhalter mit Einbaumöglichkeit eines Halbprofilzylinders der Feuerwehr </span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Feuerwehrleiter</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBODBAAA" RNoPart="400">
            <Qty>50.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508095856989000007">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderabdeckkappe m. Signalgeb</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderabdeckkappe m. Signalgeb</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBODCAAA" RNoPart="410">
            <Qty>30.000</Qty>
            <QU>St</QU>
            <Description ID="R20260508095856992000008">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Melderabdeckkappe o.Signalgeber</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Melderabdeckkappe o.Signalgeber</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
        <BoQCtgy ID="AAAAAAAAIBGJJBJI" RNoPart="2">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Stundenlohnarbeiten</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBGJJKNA">
            <PerfNo>8047</PerfNo>
            <PerfLbl>Ausführungsbeschreibung Stundenlohnarbeiten</PerfLbl>
            <Description ID="R20251104134315641000092">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend angegebenen Kosten für von der Bauleitung angeordnete Stundenlohnarbeiten sind als feste Stundenverrechnungssätze(€/Arbeitsstunden) gem. § 15 Ziff. 1 VOB/B anzubieten. In ihnen sind unaufgegliedert die Lohn- und Gehaltsnebenkosten und Gemeinkostenanteile einschl. der Sozialkassenbeiträge und Vermögenswirksamenleistungen sowie Lohn- und Gehaltsnebenkosten enthalten. Zuschläge für Nacht-, Sonnabend-, Sonntag- und Feiertagsarbeit sind nicht in die Verrechnungssätze einzubeziehen, sondern ggf. gesondert anzuweisen</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>nachfolgend angegebenen Kosten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315643000093">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Stundenlohnarbeiten dürfen nur nach ausdrücklicher Aufforderung der Bauüberwachung ausgeführt werden.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Sämtliche Stundenlohnarbeiten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315643000094">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sie sind auf einem Stundennachweiszetteln detailliert mit Namensangabe und Berufsgruppe sowie der im einzelnen verbrauchten Materialien zu erfassen. Die Stundennachweiszettel sind der Bauleitung täglich jeweils vom vorhergehenden Tage zur Anerkennung vorzulegen.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Stundennachweiszetteln</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
            <Description ID="R20251104134315644000095">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Bieter erklärt durch seine Unterschrift unter dem Angebot, dass die Verrechnungssätze unter Beachtung der preisrechtlichen Vorschriften ermittelt wurden und unabhängig von der Anzahl der abzurechnenden Stunden gelten. </span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Bieter erklärt durch seine Unterschrift</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Item ID="AAAAAAAAIBGJNGFI" RNoPart="10">
            <Qty>40.000</Qty>
            <QU>h</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315647000096">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stunden eines System-Technikers auf besondere Anordnung der örtlichen Bauüberwachung zum täglichen Nachweis</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Stunden eines System-Technikers</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
        <BoQCtgy ID="AAAAAAAAIBGJPHCI" RNoPart="3">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 456 Inspektion und Wartung</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>456</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <PerfDescr ID="AAAAAAAAIBFNAAJA">
            <PerfNo>950</PerfNo>
            <PerfLbl>Inspektion und Wartung</PerfLbl>
            <Description ID="R20251104134315651000099">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Kalkulation ist die Beistellung einer qualifizierten Fachkraft durch den Auftraggeber zu berücksichtigen. Durch diese Beistellung wird die Verantwortung des Auftragnehmers nicht beeinflußt.</span>
                 <br/>
                 <br/>
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Inspektions- und Wartungsvertrag wird abgeschlossen für die:</span>
                </p>
                <page/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Beistellung einer qualifizierten Fachkraft bei der Kalkulation</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </PerfDescr>
           <Remark ID="AAAAAAAAIBFNBIII">
            <Description ID="R20251104134315651000100">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsvertrag für die Dauer der Verjährungsfrist zur Mängelbeseitigung [4 Jahre] gemäß VOB/B § 13:</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für alle Komponenten der Brandmeldeanlage.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend beschriebenen Wartungsleistungen sind für die in diesem Leistungsverzeichnis ausgeschriebenen betriebstechnischen Anlagen bestimmt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ein ausgefülltes und unterschriebenes Exemplar dieses Wartungsvertrages wird erst zur Abnahme in dreifacher Ausfertigung vorgelegt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Störungsdienst wird im Vertrag geregelt.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Auftragsumfang umfasst alle gelieferten Anlagen und Anlagenteile des Auftragnehmers ( AN ). Sie sind in der vom AN als Bestandteil der Bedienungs- und Wartungsanleitung mitzuliefernden Bestandsliste zu erfassen.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Wartungsumfang ergibt sich aus den Wartungs- und Inspektionsanweisungen und den Arbeitskarten [AMEV] die der AN gemäß Ausschreibung als Bestandteil der Bedienungs- und Wartungsanleitung ausgefüllt mitzuliefern hat. Anlagen und Komponenten die nicht in den Arbeitskarten nach AMEV enthalten sind, werden vom AN sinngemäß ergänzt. Grundlage sind entsprechende DIN-,VdS- und VDE- Regelwerke.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der noch abzuschließende Wartungsvertrag gilt für den Zeitraum der vereinbarten Verjährungsfrist.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verjährungsfrist für Mängelansprüche beträgt 4 Jahre. Die Frist beginnt mit der Abnahme der gesamten Leistung.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die v.g. Festlegungen sind Bestandteil des abzuschließenden Wartungsvertrages.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es ist der Einheitspreis pro Jahr  anzugeben.</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Auszahlung der Jahrespauschale erfolgt nach Durchführung der Wartung, aufgrund der jährlichen Rechnungslegung und der Vorlage der Wartungsprotokolle.</span>
                 <br/>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Wartungsvertrag</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Remark>
           <Item ID="AAAAAAAAIBFNCHII" RNoPart="10">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315654000101">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 1. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 1. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFNEBDA" RNoPart="20">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315656000102">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 2. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 2. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFNFLBA" RNoPart="30">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315658000103">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 3. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018. Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 3. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFNHEPA" RNoPart="40">
            <Qty>1.000</Qty>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>456</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315661000104">
             <CompleteText>
              <ComplTSA>Yes</ComplTSA>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wartungsjahrespauschale für 4. Jahr Inspektion und Wartung der Brandmeldeanlage pro Jahr.</span>
                </p>
                <TextComplement MarkLbl="11" Kind="Owner">
                 <ComplCaption/>
                 <ComplBody>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;Vertragsmuster für Inspektion und Wartung von</span>
                  <br/>
                  <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">technischen Anlagen und Einrichtungen - nach AMEV-Vertrag-Instand GMA 2018 Zu den Leistungen gehören die Wartung und die Inspektion der gesamten Anlage.&#x27;</span>
                 </ComplBody>
                 <ComplTail/>
                </TextComplement>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Inspektion und Wartung BMA komplett 4. Jahr</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
      <Remark ID="AAAAAAAAIBFNJOBI">
       <Description ID="R20251104134315691000119">
        <CompleteText>
         <DetailTxt>
          <Text>
           <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
            <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">KG 490 Sonstige Maßnahmen für technische Anlagen</span>
           </p>
          </Text>
         </DetailTxt>
         <OutlineText>
          <OutlTxt>
           <TextOutlTxt>
            <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
             <span>KG 490 Sonstige Maßnahmen für technische Anlagen</span>
            </p>
           </TextOutlTxt>
          </OutlTxt>
         </OutlineText>
        </CompleteText>
       </Description>
      </Remark>
      <BoQCtgy ID="AAAAAAAAIBFNKJGI" RNoPart="4">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>KG 492 Gerüste</span>
        </p>
       </LblTx>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
        <CtlgCode>492</CtlgCode>
       </CtlgAssign>
       <CtlgAssign>
        <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
        <CtlgCode>492</CtlgCode>
       </CtlgAssign>
       <BoQBody>
        <PerfDescr ID="AAAAAAAAIBFNLCKA">
         <PerfNo>8083</PerfNo>
         <PerfLbl>Technische Forderungen</PerfLbl>
         <Description ID="R20251104134315669000107">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei den in diesem Titel ausgeschriebenen Gerüsten handelt es sich um Elektro-Montagegerüste und/oder Elektro-Montagebühnen für den zeitlich begrenzten Einsatz, deren Arbeitshöhen höher als 2,0 m sind.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>ausgeschriebenen Gerüsten</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20251104134315670000108">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es handelt sich um Regelausführungen nach DIN 4420 bzw. 4422 für mind. 2 Personen mit Werkzeug und Material (je Gerüst bzw. Bühne).</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gerüste müssen mind. Gruppe 3 (200 kg/m2) entsprechen - bei den Bühnen wird die Belastung mit dem Positionstext gefordert.</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die angebotene jeweilige Ausführung ist im Auftragsfall zu bescheinigen - eine statische Berechnung kann dann entfallen bzw. ist bei Nichtbescheinigung durch den AN beizubringen. Ungeachtet dessen, muss im Auftragsfall durch den AN jeweils ein Brauchbarkeitsnachweis nach DIN 4420-1 oder eine Bauartenzulassung (DIB-Berlin) erbracht werden. Die Kosten hierfür sind mit den Einheitspreisen abgegolten.</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Wahl des geeigneten Gerüstes (Systemgerüst, Kupplungsgerüst, Leitergerät aus verz. Stahlrohr oder Aluminium) wird innerhalb der mit diesem LV aufgestellten Forderungen dem Bieter/Auftragnehmer überlassen. </span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Regelausführungen nach DIN 4420 bzw. 4422</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20251104134315671000109">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Neben der Kennzeichnung nach DIN 4420 (ZH 1/534-0) sowie VBG 14 muss zusätzlich eine während der gesamten Vorhaltezeit gut lesbare und eindeutige Identifikation (Name, lfd. Gerüstnummer und Abrechnungsposition des Auftragnehmers) an jedem Gerüst angebracht und gegen Diebstahl und Verfälschung gesichert sein (z.B. abschließbar oder nieten oder schweißen).</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Kennzeichnung nach DIN 4420 (ZH 1/534-0) sowie VBG 14</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20251104134315672000110">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Berechnung der Vorhaltezeit beginnt ab dem Tag der fertigen Gerüstmontage in Wochen. Am Ende der Vorhaltezeit ist jedes Gerüst komplett einschl. aller Hilfseinrichtungen und Verankerungen von der Baustelle zu entfernen. Notwendige Bau-Ausbesserungen hat der Bieter/Auftragnehmer mit den betroffenen Fachfirmen selbst zu regeln. Eine besondere Vergütung dafür erfolgt nicht.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Berechnung Vorhaltezeit</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20251104134315672000111">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montageübliche Gerüstverschmutzungen, wie sie durch die Beschreibungen des LVs auftreten können, hat der Bieter/Auftragnehmer auf seine Kosten zu beseitigen.</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Montageübliche Gerüstverschmutzungen</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
         <Description ID="R20251104134315673000112">
          <CompleteText>
           <DetailTxt>
            <Text>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verwendung der Gerüste/Bühnen ist vorgesehen:</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im inneren des Baukörpers</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im Baustellenbereich</span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- im öffentlichen Bereich, der direkt an den die </span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Baustelle angrenzt (Gehweg, Radweg, </span>
             </p>
             <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fahrstreifen eine Straße)</span>
             </p>
            </Text>
           </DetailTxt>
           <OutlineText>
            <OutlTxt>
             <TextOutlTxt>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span>Verwendung Gerüste/Bühnen</span>
              </p>
             </TextOutlTxt>
            </OutlTxt>
           </OutlineText>
          </CompleteText>
         </Description>
        </PerfDescr>
        <BoQCtgy ID="AAAAAAAAIBFMAJLI" RNoPart="1">
         <LblTx>
          <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
           <span>KG 492 Gerüste</span>
          </p>
         </LblTx>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
          <CtlgCode>492</CtlgCode>
         </CtlgAssign>
         <CtlgAssign>
          <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
          <CtlgCode>492</CtlgCode>
         </CtlgAssign>
         <BoQBody>
          <Itemlist>
           <Item ID="AAAAAAAAIBFMBCPA" RNoPart="10">
            <Qty>2.000</Qty>
            <QtySplit>
             <Qty>2.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>449</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>St</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315680000115">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Montagegerüst gemäß den technischen Forderungen, als fahrbares Gerüst, mit Seitenschutz,</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Plattformhöhe: 3,0 m bis 7,0 m</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Plattformgröße: ca. 2,8 m x 1,8 m (ca. 4,2 m2)</span>
                </p>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplett an Verwendungsstellen mehrfach auf- und abbauen, sowie 4 Wochen vorhalten.</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Montagegerüst, fahrbar, H: 3 - 7 m</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
           <Item ID="AAAAAAAAIBFMCMLI" RNoPart="20">
            <Qty>10.000</Qty>
            <QtySplit>
             <Qty>10.000</Qty>
             <CtlgAssign>
              <CtlgID>AAAAAAAAIAGIBAAA</CtlgID>
              <CtlgCode>449</CtlgCode>
             </CtlgAssign>
            </QtySplit>
            <QU>m²</QU>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIDFBA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <CtlgAssign>
             <CtlgID>AAAAAAAAIAGIAAIA</CtlgID>
             <CtlgCode>492</CtlgCode>
            </CtlgAssign>
            <Description ID="R20251104134315688000118">
             <CompleteText>
              <DetailTxt>
               <Text>
                <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                 <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hartfaserplatten zum Schutz des Hallenbodens, inkl. mehrfaches Umverlegen in den Hallen</span>
                </p>
               </Text>
              </DetailTxt>
              <OutlineText>
               <OutlTxt>
                <TextOutlTxt>
                 <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                  <span>Hartfaserplatten</span>
                 </p>
                </TextOutlTxt>
               </OutlTxt>
              </OutlineText>
             </CompleteText>
            </Description>
           </Item>
          </Itemlist>
         </BoQBody>
        </BoQCtgy>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
   </BoQBody>
  </BoQ>
 </Award>
</GAEB>
