<?xml version="1.0" encoding="UTF-8"?>
<!-- GXML Toolbox V3.3 R20230829;  http://www.gaeb-toolbox.de/ 
 gtcConverter.dll used version 2024.07.02  -->
<GAEB xmlns="http://www.gaeb.de/GAEB_DA_XML/200407">
 <GAEBInfo>
  <Version>3.1</Version>
  <VersDate>2009-12</VersDate>
  <Date>2025-12-15</Date>
  <Time>12:21:14</Time>
  <ProgSystem>/ GXML Toolbox V3.3 R20230829</ProgSystem>
  <ProgName>iTWO_64 V25.0.558</ProgName>
 </GAEBInfo>
 <PrjInfo>
  <NamePrj>1487</NamePrj>
  <LblPrj>Deutsches Theater Göttingen</LblPrj>
  <Cur>EUR</Cur>
  <CurLbl>Euro</CurLbl>
 </PrjInfo>
 <Award>
  <DP>83</DP>
  <AwardInfo>
   <Cur>EUR</Cur>
   <CurLbl>Euro</CurLbl>
  </AwardInfo>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Leistungsverzeichnis</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">L E I S T U N G S V E R Z E I C H N I S</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">BAUVORHABEN</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deutsches Theater Göttingen</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Theaterplatz 11</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">37073 Göttingen</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">GEWERK</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektroinstallation</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">AUFTRAGGEBER</span>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stadt Göttingen</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachdienst Hochbau </span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hiroshimaplatz 1-4</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm;">
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
     <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">37083 Göttingen</span>
    </p>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <page/>
    <p style="margin-left:73pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
   </DetailAddText>
  </AddText>
  <AddText>
   <OutlineAddText>
    <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span>Baubeschreibung</span>
    </p>
   </OutlineAddText>
   <DetailAddText>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Baubeschreibung</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Notstromversorgung des Deutschen Theaters in Göttingen </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">soll erneuert werden.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Rahmen der letzten Elektrosachverständigenprüfung wurde </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bemängelt, dass die Sprinklerpumpe nicht redundant vom Netz </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und dem Notstromdiesel versorgt wird. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Da die Trafostation der Liegenschaft aus einer Mittelspannungsmasche versorgt wird, bietet eine </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprinklerschaltung keine Lösungsmöglichkeit. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das im Bestand befindliche Notstromaggregat hat eine Leistung </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von 80 kVA und somit nicht ausreichend Leistung, die 75 kW </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprinklerpumpe zu versorgen.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es soll somit die NEA inkl. SV-Versorgung erneuert werden.</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In diesem Zuge ist auch die NSHV SV zu erneuern bzw. in einem neuen separaten Raum zu errichten. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Bestandskabel der baurechtlich geforderten Verbraucher befinden sich aktuell auf der NSHV-AV und müssen verlängert und umgeschwenkt werden. Für die Anbindung der</span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzersatzanlage sind neue Kabelwege zu errichten. </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die neue NSHV-SV mit den Verbindungskabeln zur neuen </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzersatzanlage sowie die Umschwenkarbeiten der </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bestandkabel und den Ausbau der Kabelwege sind Bestandteil </span>
    </p>
    <p style="text-indent:70pt;margin-right:127pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
     <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">dieses Leistungsverzeichnisses. </span>
    </p>
   </DetailAddText>
  </AddText>
  <BoQ ID="AAAAAAAAIGEMAAAA">
   <BoQInfo>
    <Name>2</Name>
    <LblBoQ>Elektro</LblBoQ>
    <Date>2025-12-15</Date>
    <OutlCompl>AllTxt</OutlCompl>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn>Bereich</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>BoQLevel</Type>
     <LblBoQBkdn>Abschnitt</LblBoQBkdn>
     <Length>2</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Item</Type>
     <Length>4</Length>
     <Num>Yes</Num>
    </BoQBkdn>
    <BoQBkdn>
     <Type>Index</Type>
     <Length>1</Length>
     <Num>No</Num>
     <Alignment>left</Alignment>
    </BoQBkdn>
    <Ctlg>
     <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
     <CtlgType>work category</CtlgType>
     <CtlgName>Leistungsbereichkatalog</CtlgName>
    </Ctlg>
   </BoQInfo>
   <BoQBody>
    <BoQCtgy ID="AAAAAAAAIGFGAAAA" RNoPart="1">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>443 Niederspannungsschaltanlagen 1 kV</span>
      </p>
     </LblTx>
     <BoQBody>
      <BoQCtgy ID="AAAAAAAAIGFGBAKA" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>443.1 Niederspannungshauptverteilung</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFGDCKI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Notstromversorgung wird künftig aus einer neuen NSHV-SV  Verteilung versorgt, welche in einem separaten und brandlastfreien Betriebsraum, separiert von der NSHV-AV, aufgestellt wird. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die NSHV-SV besteht aus einem Schaltschrankfeld mit 1100 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mm Breite. Im dem Feld befindet sich der Einspeiseschalter </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sowie die NH-Abgänge für die SV-Verbraucher, welche in zwei</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schienen aufgeteilt sind. Diese werden bei Netzwiederkehr </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mittels Leistungsschalter / Kuppelschalter versetzt zugeschaltet, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">um die Zuschaltlast auf mehrere Laststöße aufzuteilen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Umschaltung zwischen dem AV und SV-Netz findet in der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NEA Verteilung statt und nicht wie üblich in der NSHV-SV. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Einspeisung  wird  mit einem Multimessgerät gemessen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">welches in Türen der Schaltanlagenfelder verbaut ist.  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Einbringsituation</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIe Einbringung der neuen NSHV-SV kann durch den Flur </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erfolgen. Für den Transport und die Einbringung über die kurze </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Treppe durch den Seiteneingang des Theaters in den Keller ist </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">geeignetes Transportwerkzeug einzuplanen und in die </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Positionen mit einzukalkulieren. </span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFGEJPI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Für die Einbaugeräte ist eine einheitliche Bauform </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">zu wählen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kosten für anteilige Klemmen, Verdrahtungskanäle, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verdrahtung, Hilfs- und Verbindungsschienen in den </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteilungen sind mit den Einheitspreisen abgegolten.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Für die Einbaugeräte ist eine einheitliche Bauform</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFGFICA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hauptverteilung</span>
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);"> als Standverteiler</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN EN 60439-3 / DIN VDE 0660-504, DIN VDE 0603-1, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 43871, DIN 18015-2,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennisolationsspannung 1000 V, in Normschrankbauweise, aus </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">selbsttragender Schrankkonstruktion, einschl. Wandbefestigung </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Schwerlastankern.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Türen werden mit Schrankgriff-Verschluss ausgeführt.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Abdeckung der Felder aus glasfaserverstärktem Kunststoff.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Verdrahtung von den Automaten und Schaltgeräten zu </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">den Klemmen ist frei zu verlegen und mit Leitungsösen zu</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">befestigen. Die Verdrahtung ist in den VDE-gemäßen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kennfarben vorzunehmen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Querschnitte</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungspfade dem Sicherungsnennstrom entsprechend </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steuerpfade mind. 1,5 mm².</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Steuersicherungen sind farbig zu kennzeichnen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es muss eine übereinstimmende Kennzeichnung der Geräte </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und der dazugehörigen Klemmen hergestellt werden.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für gleichartige Einbaugeräte ist ein Fabrikat vorzusehen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Aufsteckgeräte sind entsprechende Montageschienen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vorzusehen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Metallteile sind in den Potentialausgleich einzubeziehen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle nicht spannungführenden Metallteile müssen galvanisch </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verzinkt oder mit einem Rostschutz-, einem Vor- und einem </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schlagfesten Fertiganstrich versehen oder mit Epoxidharz </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">beschichtet sein. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei dem Anschluss von mehrdrähtigen Adern sind Quetsch-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kabelschuhe zu verwenden. Für die Zuleitungskabel sind stabile </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zugentlastungsschellen vorzusehen. Für den Erdanschluss ist </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eine Messingschraube M10 mit Unterleg- und Bleibeilegscheibe </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vorzusehen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Leitungseinführungen haben mit Einzel-Leitungstüllen oder </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit M-Verschraubungen zu erfolgen. In jeder Unterverteilung </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">muss eine komplette Legende mit Bezeichnung der Stromkreise </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und der zugehörigen Verbraucher in einer selbstklebenden </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffplantasche DIN A 4 angebracht werden.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Klemmen:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In den Verteilungen sind bis zu einem Querschnitt von 16 mm² </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Reihenklemmen entsprechend der notwendigen Querschnitte </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einzubauen. Die Klemmen sind in der Reihenfolge L1, N, PE, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bzw. L1, L2, L3, N, PE anzuordnen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Schaltgeräte:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle anzubauenden Schaltgeräte müssen der VDE entsprechen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bis 63 A werden aufschnappbare Geräte verwendet. </span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hauptverteilung als Standverteiler</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFGHFKI" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">NSHV-SV</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteiler als Energie-Schaltgerätekombination (PSC) </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN EN 61439 Teil1 und 2 (Bauartzulassung), gefertigt und geprüft, anschlussfertig liefern als 5-poliger TN-S-Verteiler.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HV für Innenraumaufstellung.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">HV u.a. gemäß v.g. Titel-Beschreibung und v.g. Technischen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmalen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit EMV-freundlicher Anordnung der Sammelschienen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NSHV in Schrankbauweise, bestehend aus geschotteten </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anreih-Einzelfeldern aus Stahlblech, zur Aufnahme eines</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einspeiseschaltern und Trennsicherungslastschaltleisten </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vertikale Bauform).</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufstellung und Fertigung der NSHV gemäss beigefügter </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zeichnung: kbi-Verteilerplan im System Hensel ABB Triline.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabeleinführung von oben, mit eigenen Vollblechtüren.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit allen erforderlichen Blechausschnitten in den Türen für </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalt-, Meß- und Befehlsgeräte.</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stangenschloss für bauseitigen Profilzylinder, Plantasche in Tür.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Vorbereitet für bauseitigen Halbprofilschließzylinder.</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Leistungsmerkmale:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umgebungsbedingungen:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-10 bis +40°C</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verschmutzungsgrad:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gering</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Symbol;font-size:10pt;Color:rgb(0,0,0);">I</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart:       </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP54</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nagetierschutz:       </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bodenblech</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">               </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nicht erforderlich</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feldaufstellung:       </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einreihig, Wandaufstellung </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fußboden:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufstellung auf Rohboden</span>
               <br/>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelanschlüsse:</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schalter &#x3e; 100 A:       </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bolzenanschluss; direkt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NH-Schaltleisten:      </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bolzenanschluss; direkt</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einspeisungen:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von oben, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelabgang:   </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">           </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach oben</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Gehäuse:         </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                    RAL 7035, grau</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbe Sockel:   </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">           </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">RAL 7005, mausgrau</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Elektrische Kennwerte:</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Reihenspannung:   </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">      </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 kV</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsbetriebsspannung:   </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">400 V AC</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TN-S</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsstrom in der</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hauptsammelschiene </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SV:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">min 800 A</span>
              </p>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">               </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb.</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="61" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> A</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
              <br/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungskurzzeitstrom</span>
              <br/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">lcw 1,0 sec:     </span>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">min 65 kA</span>
              <br/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb.</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> kA</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsstromfestigkeit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">lpk 0,1 sec:     </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb.</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="63" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> kA</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sammelschienensysteme:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5 Leiter, PE reduziert</span>
              </p>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb.</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="64" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm 39.80mm 59.70mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Felder: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feld 1</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">      </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einspeisung </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">               +NH-Leistenabgänge</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: 1.100 mm</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">               </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-----------------------</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite geplant:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">             </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite:  1.100 mm   </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gesamtbreite angeboten:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="65" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">        (vom Bieter einzutragen)</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Zusatzvorhaltungen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit dem Angebot ist eine Zeichnung einzureichen, aus der vom Bieter den gewählten Aufbau und die Abmessungen eindeutig hervorgehen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anlage ist dabei entsprechend dem vorgegebenen Aufbau anzubieten.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aus der Zeichnung müssen erkennbar sein:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Felder mit Abmessungen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Frontansicht</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- dievertikale Anordnung der Trenn-NH-Schaltleisten</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- die Funktionsräume</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- die Hauptsammelschienensysteme.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Hersteller/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="67" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NSHV-SV</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFGKBII" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kompaktleistungsschalter für Anlagenschutz </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß EN 60947-2 bzw. DIN VDE 0660, Teil 101 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit doppelter Isolierung.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsbetriebsspannung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">690 V AC</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsdauerstrom: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">800 A</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsgrenzkurzschlussausschaltverm.: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">65kA bei 415V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Festeinbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4-polig</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit selektivem elektronischem Überstromauslöser mit einstellbaren LS/I nach Werten aus nachfolgend ausgeschriebener Netzberechnung </span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überlastauslöser L</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,4 bis 1x In</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Trägheit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 3 bis 18s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Selektiver Kurzschlussausl. S</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,6bis 10 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 50 bis 500 Ms</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Unverzög. Kurzschlussausl. I</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 1,5.bis 12 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erdschlussschutz G</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,2 bis 1x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,1bis 0,8 s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- wählbarer Neutralleiterschutz </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: (50/100%)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- mit Möglichkeit zur elektronischen Feinparametrierung durch    </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  ein Prüfgerät</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- überprüfbar durch externes Testgerät</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- anbaubarer Fehlerstomauslöser (bis 500 A)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitsstromauslöser (steckbar)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fernantrieb mittels Federkraftspeicher und Motorantrieb</span>
               <br/>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wie vorab beschrieben in bestehende Verteilung betriebsfertig einbauen und anschließen inkl. aller Zubehörkomponenten inkl.:</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Drehantriebe, Verlängerungswelle</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abschließvorrichtung (mit Vorhängeschloss)</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Hilfsstromschalter 1S / 1Ö / 1W</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Leistungschalter mit Motorantrieb 800A 63KA,3P,400V</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFGMDKI" RNoPart="30">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kompaktleistungsschalter für Anlagenschutz </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß EN 60947-2 bzw. DIN VDE 0660, Teil 101 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit doppelter Isolierung.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsbetriebsspannung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">690 V AC</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsdauerstrom: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">400 A</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsgrenzkurzschlussausschaltverm.: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">65kA bei 415V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Festeinbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3-polig</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit selektivem elektronischem Überstromauslöser mit einstellbaren LS/I nach Werten aus nachfolgend ausgeschriebener Netzberechnung </span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überlastauslöser L</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,4 bis 1x In</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Trägheit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 3 bis 18s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Selektiver Kurzschlussausl. S</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,6 bis 10 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 50 bis 500 Ms</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Unverzög. Kurzschlussausl. I</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 1,5bis 12 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erdschlussschutz G</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,2 bis 1x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,1bis 0,8 s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- wählbarer Neutralleiterschutz </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: (50/100%)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- mit Möglichkeit zur elektronischen Feinparametrierung durch </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  ein Prüfgerät</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- überprüfbar durch externes Testgerät</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- anbaubarer Fehlerstomauslöser (bis 500 A)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitsstromauslöser (steckbar)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fernantrieb mittels Federkraftspeicher und Motorantrieb</span>
               <br/>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wie vorab beschrieben in bestehende Verteilung betriebsfertig einbauen und anschließen inkl. aller Zubehörkomponenten inkl.:</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Drehantriebe, Verlängerungswelle</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abschließvorrichtung (mit Vorhängeschloss)</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Hilfsstromschalter 1S / 1Ö / 1W</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Leistungschalter mit Motorantrieb 400A 63KA,3P,400V</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFGOFFI" RNoPart="40">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kompaktleistungsschalter für Anlagenschutz </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß EN 60947-2 bzw. DIN VDE 0660, Teil 101 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit doppelter Isolierung.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsbetriebsspannung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">690 V AC</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsdauerstrom: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">250 A</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bemessungsgrenzkurzschlussausschaltverm.: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">55kA bei 415V</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Festeinbau</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3-polig</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit selektivem elektronischem Überstromauslöser mit einstellbaren LS/I nach Werten aus nachfolgend ausgeschriebener Netzberechnung </span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Überlastauslöser L</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,4 bis 1x In</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Trägheit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 3 bis 18s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Selektiver Kurzschlussausl. S</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,6 bis 10 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 50 bis 500 Ms</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Unverzög. Kurzschlussausl. I</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 1,5 bis 12 x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Erdschlussschutz G</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,2 bis 1x In</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  Verzögerungszeit einstellbar</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 0,1 bis 0,8 s</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- wählbarer Neutralleiterschutz </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: (50/100%)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- mit Möglichkeit zur elektronischen Feinparametrierung durch </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  ein Prüfgerät</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- überprüfbar durch externes Testgerät</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- anbaubarer Fehlerstomauslöser (bis 500 A)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitsstromauslöser (steckbar)</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Fernantrieb mittels Federkraftspeicher und Motorantrieb</span>
               <br/>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wie vorab beschrieben in bestehende Verteilung betriebsfertig einbauen und anschließen inkl. aller Zubehörkomponenten inkl.:</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Drehantriebe, Verlängerungswelle</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abschließvorrichtung (mit Vorhängeschloss)</span>
              </p>
              <p style="margin-right:5pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Hilfsstromschalter 1S / 1Ö / 1W</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Leistungschalter mit Motorantrieb 250A 55KA,3P,400V</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFHAIEA" RNoPart="50">
          <Qty>12.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NH00-Reiterlasttrenngehäuse </span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Leistenform (bis 160A) IP 65</span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3-pol. 160 A, mit transparentem Deckel, 3 Reiterlasttrenner, </span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">70 mm2, Abgang oben, mit Anschlussklemmen 70 mm2 </span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und PE- und N-Abgangsklemmen bis 35 mm2, 3 x NH 0 </span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf Sammelschiene, 3-polig 250 A</span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. NH Sicherungen bis max. 160 A.</span>
              </p>
              <p style="margin-right:5pt;text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Fabrikat/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NH00-Reiterlasttrennleiste</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFHCENI" RNoPart="60">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Multimeter, Fronteinbau 96/96 mm, 4-polig</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Messung für:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 4-polige Strommessung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- bis 63, Harmonische</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Spannung, Strom, Leistung als Min/Max-Anzeige</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Messfunktionen: U, I, F, P, Q, S, cosPhi</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verzerrungsfaktor (THD)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wirkenergie kWh / Blindenergie kvarh/</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Scheinenergie kVAh</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Min/Max-Wert Speicher</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsstundenzähler</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Grenzwertüberwachung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Lastgangaufzeichnung mit zeitstempel</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Phasenwinkel / Phasendiagramm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Messgenauigkeit (%): Strom/Spannung = 1 , Leistung = 1</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 digitale Ausgänge als Alarm- oder Steuerausgang</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(24 V d.c. max. 50 mA)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 digitale Eingänge (24V d.c.)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Display</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnittstelle serielle Ports mit Modbus 1 Stück</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Schnittstelle Ethernet-Port mit Modbus-TCP, 2 Stück</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Fabrikat/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Multimeter, Fronteinbau 96/96 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFHEEEI" RNoPart="70">
          <Qty>4.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stromwandler 1-polig, 1.000 / 5A</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Stromwandler 1-polig, 1.000 5A</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFHFOMI" RNoPart="80">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überspannungsschutzeinrichtung Typ 1+2</span>
               <br/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Niederspannungsanlagen (Innenanlagen),nach VDE 675</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">§ 6/89, gemäß Anforderungsklasse C, Typ 1+2, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zum Einbau in Verteiler mit Schnappbefestigung, 4-polig, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit optischer Defektanzeige und potentialfreiem Ausgang </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Defektmeldung.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Leiter gegen Erde )</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(255,255,255);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 230 V</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Betriebsspannung </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 275V/50 Hz.</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(255,255,255);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Restspannung</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(255,255,255);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">             </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 1,3 kV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Fabrikat/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Überspannungsschutzeinrichtung Typ 1+2</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="AAAAAAAAIGFKAAAA" RNoPart="2">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>444 Niederspannungsinstallation</span>
      </p>
     </LblTx>
     <BoQBody>
      <BoQCtgy ID="AAAAAAAAIGFKBAGA" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>444.1 Steigekabel</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFPBAAA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Technische Leistungsmerkmale</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel und Leitungen, Anschlüsse</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Einleiterkabel</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Verlegung von Einleiterkabeln im MS- und NS-Bereich </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sind die Vorschriften für eine ordnungsgemäße Verdrillung und </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für erforderliche Lagerarretierungen anteilmäßig wie folgt vom </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">AN mit einzukalkulieren.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Freiverlegte Einleiterkabel sind in der Lage zu arretieren, das </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gilt auch bei einer Verlegung auf Rinnen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Befestigungsabstände 1 M.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der AN hat dafür zu sorgen, dass die erforderlichen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelbefestigungen mindestens den zu erwartenden </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maximalkräften im Kurzschlussfall zu genügen haben, max. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungsabstände 1 M.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Kabelanschlüsse</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Im Rahmen der separat zu vergütenden Leistungen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Anschlüsse werden auch die Anschlüsse sämtlicher</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel und Leitungen an Rangierverteiler (Abzweigdosen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit mehr als einem Stromkreis) und Verteilungsanlagen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Unterverteilung, Steuerleitungsverteiler u. ä.) erfaßt.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Leistungsumfang für Anschlüsse von Kabeln gehört</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">das Absetzen, Ausbinden und Abisolieren der Leiterenden</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sowie das Liefern und Montieren von Kabelschuhen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Anschließen von sonstigen Anlageteilen hat nach</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anweisung des jeweiligen Herstellers oder Lieferanten</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu erfolgen und schließt grundsätzlich das Überprüfen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Leitung, bei Drehstrom auch des Drehfeldes, mit</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ein.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Geräteanschlüsse</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">unter  vorhandenen Geräten sind solche Bauteile zu</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verstehen, die nicht vom Auftragnehmer der Elektro-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anlagen in Form einer Hauptleistung geliefert und</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">montiert werden. Sie gelten für den AN als beigestellte</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anlagenteile, die den Anforderungen entsprechend an</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die elektrischen Anlagen anzuschließen sind.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Endverschlüsse</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beim Herstellen von Endenabschlüssen sind</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">folgende Leistungen durchzuführen und in den</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">entsprechenden Einheitspreisen zu kalkulieren:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.1</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fachgerechtes Absetzen der Kabelenden.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.2</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Prüfung der Adern auf Durchgang, Berührung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Vertauschen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.3</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Prüfung der beiden Kabelenden  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf gleichen Drehsinn der Lagen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.4</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Spleißung der Kabelenden und Spitzenver-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">lötungen bei den Adernverbindungen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">.5</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Isolieren der Beidrähte von Kunststoffkabeln</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Lötverbindung (für Betriebserde) bzw.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verbindung der Bleimäntel mit flexiblen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kupferleitern bei Bleikabeln.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Entsprechend den Angaben im Leistungsumfang sind</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Muffen von Bleikabeln mit oder ohne zusätzliche </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzmuffe aus Gußeisen auszuführen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Beim Auflegen der Kabelenden auf Verteiler o. ä.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sind die blanken Bleidrähte ebenfalls zu isolieren</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und entweder auf isolierte Erdklemmen oder auf</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">freie Lötstifte von Leisten aufzulöten.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Auflegen der Kabelenden gehört auch das ggf.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erforderliche Ausbinden der Adern oder, falls aufgrund</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Platzverhältnisse möglich, das Führen in mitzu-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:4.90mm 7.00mm 11.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefernden Verdrahtungskanälen aus Kunststoff. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Kabelarten</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss eines Kunststoffkabel der Typen: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM, NYY, NYCWY und Funktionserhaltkabel bis E90 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bis 1 KV an vorhandene Verteilungen, Rangierverteiler, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tableaus.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Erfaßt werden in diesem Titel alle Anschlussarbeiten</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ab Stationsverteiler 1 KV Ausgang.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationsendgeräte, wie Schalter, Steckdosen und Leuchten, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden anschlussmäßig nicht separat vergütet, da diese </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussleistung mit zu v. g. Verbrauchern gehören.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgend aufgeführten  Anschlüsse beinhalten:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Prüfaufwand</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Absetzarbeiten</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- evtl. Kabelschuhe</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Begriffserklärung:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">System - dreipolige Anwendung, ggf. eine Zusammenfassung </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von drei Einleitereinheiten.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Kalkulation:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Verbrauchsmaterialien wie:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Rohre</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Abstandsschellen </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Dübel</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Kabelbinder</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Zubehöre</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Prüfaufwendungen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Freischaltungen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sind anteilig mit in die Hauptpositionen einzukalkulieren.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Leistungen gemäß separater LV-Position:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1. Rinnen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2. C-Profilschienen</span>
              </p>
              <page/>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Technische Leistungsmerkmale</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFPDFEA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Befestigungsschellen (Nagelschellen, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abstandschellen, Kabelschnellverleger, Sammelbefestigung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und -halter, Dübel usw.) einschließlich der erforderlichen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zubehörteile sind anteilig und komplett mit den nachfolgenden </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hauptpositionen einzukalkulieren</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">V.g. gilt nicht, sofern entsprechende Verlegesysteme oder </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungselemente (Rinnen, Steigeleitern, Ankerschienen, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kanäle, Rohre oder auch Schlitzarbeiten) ausdrücklich im Leistungsverzeichnis als separate Positionen aufgeführt sind.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFKDDJI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kabel 0,6 / 1 KV in Wa. Ro. Ka</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Als Kunststoffkabel nach DIN 570271, VDE 0271 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verlegen in Teillängen als Mischverlegung:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * in Wannen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * in Rohren,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * auf und in Kanälen.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabel 0,6 / 1 KV in Wa. Ro. Ka</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFKEEDI" RNoPart="10">
          <Qty>90.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 12 x 2,5mm², E90 Cu-Zahl 288</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 12 x 2,5 mm² E90, Cu-Zahl 288</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFKFOII" RNoPart="20">
          <Qty>15.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFIHII" RNoPart="30">
          <Qty>8.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFKDCI" RNoPart="40">
          <Qty>90.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 7 x 2,5 mm² E90, Cu-Zahl 168</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 7 x 2,5 mm² E90, Cu-Zahl 168</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFKHIMI" RNoPart="50">
          <Qty>80.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-J 3 x 2,5 mm² E90, Cu-Zahl 72</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 3 x 2,5 mm² E90, Cu-Zahl 72</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFBAAA" RNoPart="60">
          <Qty>8.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 3 x 4 mm² E90, Cu-Zahl 115</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 3 x 4 mm² E90, Cu-Zahl 115</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGBPBDI" RNoPart="70">
          <Qty>16.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 4 x 4mm² E90, Cu-Zahl 154</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 4 x 4 mm² E90, Cu-Zahl 154</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFMAAA" RNoPart="80">
          <Qty>40.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5x 4mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 4 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFKJDAI" RNoPart="90">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5 x  6mm² E90, Cu-Zahl  192</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 6 mm² E90, Cu-Zahl 192</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGIFEI" RNoPart="100">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH  E90 4x70/35mm², Cu-Zahl 3082</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 4x70/35mm², Cu-Zahl 3082</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGGAAA" RNoPart="110">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH  E90 4x240/120mm², Cu-Zahl 10546</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 4x240/120mm², Cu-Zahl 10546</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFKOEOA" RNoPart="120">
          <Qty>50.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(N)HXH  E90 1 x 240, Cu-Zahl 2304</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 1 x 240, Cu-Zahl 2304</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGHAAAA" RNoPart="130">
          <Qty>20.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldekbel 12x2x0,5 mm²</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Brandmeldekbel 12x2x0,5 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFCFJI" RNoPart="140">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x6 mm², Cu-Zahl  288</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 5 x6 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFHAAA" RNoPart="150">
          <Qty>30.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x10 mm², Cu-Zahl 480</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 5 x10 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFFCKA" RNoPart="160">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 4x50 mm², Cu-Zahl 1920</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 4 x50 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGHBLGI" RNoPart="170">
          <Qty>400.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 1 x 240 mm², </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu-Zahl  2304</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 1 x 240 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGHDFNI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kabel 0,6 / 1 KV mit Sch. &#x26; UP</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Kunststoffkabel nach DIN 570271, VDE 0271 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verlegen in Teillängen als Mischverlegung:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * mit Abstandsschellen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * mit Bügelschellen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * auf und unter Putz</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * auf Wand und Decke</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> * in Schlitzen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabel 0,6 / 1 KV mit Sch. &#x26; UP</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGIFAAA" RNoPart="180">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 12 x 2,5mm², E90 Cu-Zahl 288</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 12 x 2,5 mm² E90, Cu-Zahl 288</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIGKFI" RNoPart="190">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIIAAA" RNoPart="200">
          <Qty>2.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIJKFI" RNoPart="210">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 7 x 2,5 mm² E90, Cu-Zahl 168</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 7 x 2,5 mm² E90, Cu-Zahl 168</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIKPNI" RNoPart="220">
          <Qty>20.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-J 3 x 2,5 mm² E90, Cu-Zahl 72</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 3 x 2,5 mm² E90, Cu-Zahl 72</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIMKEI" RNoPart="230">
          <Qty>3.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 3 x 4 mm² E90, Cu-Zahl 115</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 3 x 4 mm² E90, Cu-Zahl 115</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGIODDI" RNoPart="240">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 4 x 4 mm² E90, Cu-Zahl 154</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 4 x 4 mm² E90, Cu-Zahl 154</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJAAAA" RNoPart="250">
          <Qty>20.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5 x 4mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 4 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJBHOI" RNoPart="260">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5 x  6mm² E90, Cu-Zahl  192</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXH-J 5 x 6 mm² E90, Cu-Zahl 192</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGJGOI" RNoPart="270">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH  E90 4x70/35 mm², Cu-Zahl 3082</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 4x70/35mm², Cu-Zahl 3082</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGEFII" RNoPart="280">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH  E90 4x240/120 mm², Cu-Zahl 10546</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 4x240/120mm², Cu-Zahl 10546</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJDCDI" RNoPart="290">
          <Qty>200.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(N)HXH  E90 1 x 240, Cu-Zahl 2304</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH  E90 1 x 240, Cu-Zahl 2304</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJENLI" RNoPart="300">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandmeldekbel 12x2x0,5 mm²</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Brandmeldekbel 12x2x0,5 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJGJCI" RNoPart="310">
          <Qty>5.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x6 mm², Cu-Zahl  288</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 5 x6mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJIDCI" RNoPart="320">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x10 mm², Cu-Zahl 480</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 5 x10mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJJNGI" RNoPart="330">
          <Qty>3.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 4x50 mm², Cu-Zahl 1920</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 4 x50mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGJLHKI" RNoPart="340">
          <Qty>100.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 1 x 240 mm², </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu-Zahl  2304</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NYY-J 1 x 240 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGKEJGI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Anschließen von Kunststoff-Kabeln / -Leitungen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">An Anschlusseinrichtungen, inkl. Absetzen, mit allen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erforderlichen Verbindungsmaterialien.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Anschluss aller Kabel und Leitungen unter 5x10mm² </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ist bei den Installationsgeräten bzw. Reihenklemmen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Unterverteilungen oder entsprechend anderen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlusseinrichtungen einzukalkulieren.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschließen von Kunststoff-Kabeln / -Leitungen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGKFLGI" RNoPart="350">
          <Qty>22.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Mehraderkabel bis 25 mm²</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Mehraderkabel bis 25 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGKHFEI" RNoPart="360">
          <Qty>2.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Mehraderkabel bis 50 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Mehraderkabel bis 50 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGKJKJA" RNoPart="370">
          <Qty>4.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Mehraderkabel bis 95 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Mehraderkabel bis 95 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGKLGKI" RNoPart="380">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Mehraderkabel bis 150 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Mehraderkabel bis 150 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGCBMI" RNoPart="390">
          <Qty>2.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Mehraderkabel bis 240 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Mehraderkabel bis 240 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGKNBAI" RNoPart="400">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Einzeladerkabel bis 120 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Einzeladerkabel bis 120 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGKOLII" RNoPart="410">
          <Qty>30.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschluss Einzeladerkabel bis 240 mm²</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschluss Einzeladerkabel bis 240 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGDHCKI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffen für Kunststoff-Kabeln / -Leitungen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffen für Kunststoff-Kabeln / -Leitungen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGDJOHI" RNoPart="420">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 7 x 1,5 mm² E90, Cu-Zahl 101</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGDLIGI" RNoPart="430">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 5 x 2,5 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLAHEI" RNoPart="440">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 3 x 4 mm² E90, Cu-Zahl 115</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 3 x 4 mm² E90, Cu-Zahl 115</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLCBJI" RNoPart="450">
          <Qty>3.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 4 x 4 mm² E90, Cu-Zahl 154</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 4 x 4 mm² E90, Cu-Zahl 154</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLDLOI" RNoPart="460">
          <Qty>2.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5 x 4 mm² E90, Cu-Zahl 120</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 5 x 4 mm² E90, Cu-Zahl 120</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLFFNI" RNoPart="470">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYM-J 5 x  6 mm² E90, Cu-Zahl  192</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXH-J 5 x 6 mm² E90, Cu-Zahl 192</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGGLCJI" RNoPart="480">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe NHXMH  E90 4x70/35 mm², Cu-Zahl 3082</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXMH  E90 4x70/35mm², Cu-Zahl 3082</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLHACI" RNoPart="490">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe (N)HXH  E90 1 x 240, Cu-Zahl 2304</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NHXMH  E90 4x240/120mm², Cu-Zahl 10546</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLILKI" RNoPart="500">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe Brandmeldekbel 12x2x0,5 mm²</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe Brandmeldekbel 12x2x0,5 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLKHBI" RNoPart="510">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x6 mm², Cu-Zahl  288</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NYY-J 5 x6mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLMBFI" RNoPart="520">
          <Qty>3.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 5x10 mm², Cu-Zahl 480</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>GießharzmuffeNYY-J 5 x10mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGLNLJI" RNoPart="530">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="margin-right:2pt;text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gießharzmuffe </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NYY-J 4x50 mm², Cu-Zahl 1920</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gießharzmuffe NYY-J 4 x50mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFMEBPA" RNoPart="2">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>444.2 Installationsleitungen</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGGBGAPI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">F</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ür den neuen NSHV-Raum ist eine Rauminstallation </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Feuchtraumwannenleuchte und Schaltersteckdosen- </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kombination in Aufputzinstallation herzustellen,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die Verkabelung erfolgt halogenfrei in:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 3 x 2,5 mm² Steckdosenstromkreise</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 5 x 1,5 mm² Beleuchtungsstromkreise</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für sämtliche Kabel und Leitungen sind Einzelbohrungen </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in Beton/Mauerwerk/Leichtbauwand einzukalkulieren. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einzelbohrungen sind mit einem A1 Baustoff </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">brandschutztechnisch und schalldicht zu verschließen. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Selbiges gilt für die Verlegung auf und unter Putz.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Anwendung von allen Kabel und Leitungen sind </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">folgende Normen einzuhalten:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN VDE 0298 in ihren Teilen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN 57250</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN VDE 0250 in ihren Teilen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN VDE 0271</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN VDE 0220 in ihren Teilen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* DIN VDE 0228 in ihren Teilen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGGBHELI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kunststoff-Mantelleitung in Wa. Ro. Ka</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nach DIN 57250/VDE 0250, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verlegen in Teillängen,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als Mischverlegung:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* in Wannen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* in Rohren,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* auf und in Kanälen.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kunststoff-Mantelleitung in Wa. Ro. Ka</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGBJOJI" RNoPart="10">
          <Qty>50.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH-J 5 x 1,5 mm², Cu-Zahl 72</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH-J 5 x 1,5mm², Cu-Zahl 72</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGBLINI" RNoPart="20">
          <Qty>50.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXMH-J 3 x 2,5 mm², Cu-Zahl 72</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>NHXMH-J 3 x 2,5mm², Cu-Zahl 72</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFNBOGI" RNoPart="3">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>444.3 Verteilungen</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFNCOMI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Als Übergabekasten sowohl für die Leistungskabel </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">als auch die Steuerkabel der NEA am Gebäudeintritt</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sind Verteilerkästen mit Überspannungsachutzmodulen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">des Typs 1+2 anzubieten </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Aufnahme und Übegabe folgender Leitung mit einem</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überspannungschutz am Gebäudeeintrit sind die </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nachfolgenden Verteilungen anzubieten:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Leistungskabel:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-  2 x (5x1x 240mm NYY)     </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">AV-Netz</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-  1 x (5x1x 240mm NHXH)  </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NSHV-SV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Steuer- und Meldekabel:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-  1 x 12x2,5mm² NYY     </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fernauslösung Netzausfalltest</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-  1 x  7x1,5mm² NHXH   </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">             </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Störmeldeweiterleitung</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-  1 x  3x2,5mm² NHXH    </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">            </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meldeleitung Sprinklerbetrieb</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFNEDGI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Einbaugeräte ist eine einheitliche Bauform </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu wählen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kosten für anteilige Klemmen, Verdrahtungskanäle, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verdrahtung, Hilfs- und Verbindungsschienen in den </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteilungen sind mit den Einheitspreisen abgegolten.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Für die Einbaugeräte ist eine einheitliche Bauform</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFNHBGI" RNoPart="10">
          <Qty>2.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis zu Übergabekasten Leistungkabel</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussfertige Kombination aus Verteiler Stahlblech </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Pulverbeschichtung mit der Schutzklasse IP 65 </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Wandmontage.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Raumaufstellung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">außen   </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteilerkasten aus Stahlblech </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Reihenspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 kV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,4 kV, AC</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TN-S</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom Sammelschiene:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu, 800 A, 5-polig</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 65</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                             </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandverteilerkästen Stahlblech/Pulverbeschichtung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Schrankabmessungen und Ausstattung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">80 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">80 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                                                         </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tiefe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">60 mm</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kupferschiene min 800 A für Kabelanschluss </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Rohrkabelschuh und Schrauben: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationsmöglichkeit für einen ÜSS Typ 1+2 </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schrankeinführungen von oben und unten</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Aufnahme und Übergabe folgender Leitungen mit einem </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überspannungschutz Typ 1+2 am Gebäudeeintritt: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Schrank 1</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 1x (5x1x240mm² NHXCH E90 )</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Schrank 2 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 2x (5x1x 240mm² NYY)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabelübergabekasten Leistungskabel</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFNJOHI" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis zu Übergabekasten Stuerleitungen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Übergabefeld für die mobile Netzersatzanlage </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ist wie folgt  auszuführen:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschlussfertige Kombination aus Verteiler Stahlblech </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Pulverbeschichtung oder Kunstoff </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit der Schutzklasse IP 65 </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Wandmontage.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Raumaufstellung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">außen   </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteilerkasten aus Stahlblech oder aus Kunstoff </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Reihenspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 kV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,4 kV, AC</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TN-S</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennstrom Sammelschiene:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu 100A</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 65</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                             </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandverteilerkästen Stahlblech/Pulverbeschichtung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                                                      o. Kunstoff</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Schrankabmessungen und Ausstattung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">60 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                                                         </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tiefe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">30 mm</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Aufnahme und Übergabe folgender Leitungen mit einem </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Überspannungschutz Typ 1+2 am Gebäudeeintritt: </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 1x (7x1,5mm² NHXCH E90 )</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 1x (12 x 2,5mm² NHXMH E90)</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 1x (3x2,5mm² NHXMH E90)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabelübergabekasten Steuerleitung</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFNMADI" RNoPart="30">
          <Qty>11.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ÜSS Modul Typ 1+2</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> 5-polig</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>ÜSS Typ 1+2 (5- polig)</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGGAJOAI" RNoPart="4">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>444.4 Verlegesysteme, Trassen</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGGCNKBA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Vorbemerkungen Verlegesysteme</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kabelrinnen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die nachfolgenden Ausführungsbestimmungen gelten sinnge</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mäß für Kabelrinnen, Kabelpritschen und Steigtrassen, auch </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">wenn im Text nur &#x22;Kabelrinnen&#x22; steht. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Mindestabstand der Befestigungen (Hängestiele, Ausleger) </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">beträgt 1,5 m; zusätzliche Befestigungen bei Richtungs-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">änderungen und vor Brandschotts gemäß Bauartzulassung. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kabelrinnen einschließlich des Montagezubehörs sind im </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Normalfall für ein Kabelgewicht von 10 kg/m je 100 mm </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rinnenbreite zu dimensionieren. Die Durchbiegung der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinnen darf hierbei bei einer Stützenweite von 1,5 m </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximal 2 mm betragen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für höhere Belastungen sind in separaten Positionen Bauteile in </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwerer Ausführung beschrieben.</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Angaben der Tragfähigkeiten gelten immer einschließlich </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungen.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinnen sind in stabiler Bauart mit seitlicher Aufkantung </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zum Kantenschutz oben rund abgebogen zu verwenden </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Höhe der Aufkantung 60 mm, Materialstärke 1,5 mm). </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das Bodenblech ist gelocht mit Lochprägung zur Erhöhung der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stabilität. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Kabelrinnen sind untereinander so zu verschrauben, dass </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eine sichere elektrisch leitfähige Verbindung besteht. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bögen, Abzweige, Kreuzungen, Etagen usw. sind unter </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verwendung der vom Hersteller empfohlenen Werkzeuge, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Formstücke und Verbindungsteile herzustellen. Ausschneiden </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Biegen von Kabelrinnen für Etagen, Bögen, Abzweige usw. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ist nicht zulässig. Kabelrinnenenden sind mit Endblechen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu versehen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle Kabelrinnen einschließlich Montagezubehör mindestens </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sendzimir-bandverzinkt nach DIN 17162, Schnittflächen sind mit </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">kalt nachzuverzinken. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Leitungen und Kabel sind in die Rinnen parallel einzulegen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungen mit Kabelbindern oder dergleichen sind nach </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abschluss der Verlegearbeiten zu entfernen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Auf den maximalen Füllfaktor und die Wärmeableitung ist zu </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">achten. Beim Einziehen der Kabel/Leitungen ist darauf zu </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">achten, dass der Schutzmantel unbeschädigt bleibt. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bedingt durch die hohe Belastung an den Aufhängepunkten, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">darf die Befestigung von Kabelpritschen und Kabelrinnen nur </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit zugelassenen Metalldübeln entsprechend der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Baumusterzulassung des Instituts für Bautechnik, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Berlin erfolgen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hängestiele und Kabelpritschenenden sind mit Schutzkappen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus PVC zu versehen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinnen, Kabelpritschen und Steigtrassen mit Funktions-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">erhalt bis 90 Minuten im Brandfall nach DIN 4102. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Ausführung ist zu beachten: </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Brandschutzkabelanlagen sind immer als oberste Lage</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu montieren. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die angebotenen Ausführung muss für einen Stützabstand </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von 1,5 m geeignet sein. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Befestigung von Steigtrassen muss der obere </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungspunkt die Steigtrasse tragen (hängend lagern), </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">um ein Abknicken zu verhindern. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Gesamtanlage ist eine Kennzeichnung mit </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dokumentation nach DIN 4102, Teil 12, zu liefern. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Das angebotene Fabrikat muss für das Fabrikat und die</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung der angebotenen Kabel mit Funktionserhalt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zugelassen sein. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei über den Kabeltrassen liegenden Installationen sind die </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinnen so abzudecken, dass eine Beschädigung der </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel durch im Brandfall herabfallende Installationsteile </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausgeschlossen ist. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"> </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel mit Funktionserhalt dürfen nicht gemeinsam mit </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">   Kabeln </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Leitungen ohne Funktionserhalt auf </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">   Kabelrinnen verlegt werden. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei senkrechter Trassenführung über 3,5 m Höhe ohne </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">dazwischenliegende Brandabschottungen muss die </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:2.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verlegung nach DIN 4102, Teil 12, Bild 5 erfolgen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Rohre </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Stahlpanzer- und Alurohren müssen alle Rohrenden (auch </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einführungen in Dosen und Gehäuse) mit Endtüllen versehen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für die Rohrbefestigung sind geschlossene Abstandsschellen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">oder Bügelschellen zu verwenden, Schellen für Stahlpanzer-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">rohre aus Stahl verzinkt. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abstand der Rohrschellen maximal 100 cm, im Handbereich </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">maximal 60 cm, zusätzlich Rohrschellen an den Enden. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kanäle </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abzweige einzelner Leitungen aus Installationskanälen sind mit </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffwürgenippeln herzustellen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationskanäle sind mit Kabelhaltestegen bzw. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelhalteklammern auszurüsten; beim Abnehmen der Kanal-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">deckel dürfen keine Leitungen herausfallen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Richtungsänderungen der Installationskanäle sind unter </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verwendung der standardmäßigen Formstücke herzustellen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Installationskanäle dürfen nur bis maximal 70 % mit Leitungen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gefüllt werden. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Inbeton-Leerrohrinstallation</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verlegt werden dürfen nur Kunststoffpanzerrohre für schwere </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mechanische und thermische Beanspruchung. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Es dürfen grundsätzlich nur durchgehende Rohre verlegt </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">werden. Muffen innerhalb des Betons sind nicht zulässig. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei der Verlegung der Rohre ist zu beachten, dass ein </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausreichender Biegeradius eingehalten und ein ausreichender </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abstand der Rohre untereinander eingehalten wird, sodass </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eine sichere &#x22;Bindung&#x22; des Betons gewährleistet ist.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Vorbemerkungen Verlegesysteme</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFPAAAA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kabelkanal zur Leitungsführung</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN VDE 0604, Stahlblech, reinweiß, RAL 9010.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Unterteil mit übergreifendem Oberteil und Halteklammern </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Formteilen, ohne Trennwand </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl. Befestigungsmaterial</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabelkanal zur Leitungsführung</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGGAKOGI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Folgende Kabeltragsysteme sind eingeplant:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">NSHV AV Raum / SV Raum</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ELT-Trasse 400/60 m mit Wandausleger </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">400 mm Steigleiter für Kabelführung aus dem Doppelboden</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Trasse im Deckenbereich</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Gebäudeaustritt TG bis NEA-Container</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelleiter 2 x 400/110 mm mit Deckel Befesttigung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Kabel mit Schellen. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Rauminstallation:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Installationsrohr starr mit Schellen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Steuerleitungen Sprinklerzentrale / GLT:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Sammelhalter</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Kabeldurchführung Gebäudeaustritt </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Stahlblechelement pulverveschichtet  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  mit Rohrrahmen und Kabeldurchführungen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGAMPNI" RNoPart="10">
          <Qty>10.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewindestange M8</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Zuschnitte, zur Aufnahme von Tragsystemen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinne, Befestigung mit Metalldübel </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">im Beton bzw. Mauerwerk. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Befestigung und Verbindungsmaterial.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 1.200 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gewindestange M8</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGAOKCI" RNoPart="20">
          <Qty>10.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewindestange M10</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Zuschnitte, zur Aufnahme von Tragsystemen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinne, Befestigung mit Metalldübel</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">im Beton bzw. Mauerwerk. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Befestigung und Verbindungsmaterial.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 1.200 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Gewindestange M10</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOAEII" RNoPart="30">
          <Qty>10.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">C-Profil-Schiene 200 mm</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Zuschnitte, zur Aufnahme von Bügelschellen,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung mit Metalldübel an Beton bzw. Mauerwerk.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlitzweite: 18 mm - 22 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 200 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material: Stahlblech </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(feuerverzinkt nach DIN EN ISO 1461)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>C-Profil-Schiene 200 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOBPII" RNoPart="40">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">C-Profil-Schiene Konstruktion</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. Zuschnitte, zur Konstruktion von Befestigungsgerüsten </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vor Dämmungen und Isolierungen zur Aufnahme </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von Schränken und Kabeltragsystemen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung mit Metalldübel an Beton bzw. Mauerwerk.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inkl. Verbindungsmaterialien.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlitzweite: 18 mm - 22 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material: Stahlblech </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(feuerverzinkt nach DIN EN ISO 1461)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>C-Profil-Schiene Konstruktion</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGODLGI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Befestigung zu verlegender Kabel und Leitungen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf C-Profil-Schienen und Steigleitern, als Führung </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und Befestigung von Kabeln, Leitungen und Leerohren.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schlitzweite: 18 mm - 22 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material: Stahlblech</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Feuerverzinkt nach DIN EN ISO 1461)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Druckwanne: Stahl (sendzimirverzinkt)</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive: maximal eine Gegen- und zwei Doppelwannen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGOENII" RNoPart="50">
          <Qty>50.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle 12-16 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle 12-16 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOGIJA" RNoPart="60">
          <Qty>50.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle 16-22 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle 16-22 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOICOI" RNoPart="70">
          <Qty>50.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle 22-28 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle 22-28 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOJNII" RNoPart="80">
          <Qty>50.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle 28-34 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle 28-34 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGOLGPI" RNoPart="90">
          <Qty>50.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bügelschelle 34-40 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bügelschelle 34-40 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGCBEOI" RNoPart="100">
          <Qty>100.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel Sammelhalter Größe 15</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus Metall für Sammelverlegung von Kabeln </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">an Wänden oder Decken. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In flammwidriger Ausführung,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Größe: 15</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabel-Sammelhalter 15</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGCDAJI" RNoPart="110">
          <Qty>25.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabel Sammelhalter Größe 30</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus Metall für Sammelverlegung von Kabeln </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">an Wänden oder Decken.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In flammwidriger Ausführung,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Größe: 30</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabel-Sammelhalter 30</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGCEMEI" RNoPart="120">
          <Qty>100.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sammelbefestigung  15 E90</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Deckenmontage, aus Stahlblech, verzinkt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit abgerundeten Kanten,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für ca. 15 Leitungen 3x2,5 mm²</span>
              </p>
              <br/>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Fabrikat/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Sammelbefestigung 15 E90</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGCGICI" RNoPart="130">
          <Qty>25.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <ComplTSB>Yes</ComplTSB>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sammelbefestigung  30 E90</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Deckenmontage, aus Stahlblech, verzinkt</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit abgerundeten Kanten,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für ca. 30 Leitungen 3x2,5 mm²</span>
               <br/>
              </p>
              <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">angeb. Fabrikat/Typ:</span>
              <br/>
             </Text>
             <TextComplement MarkLbl="62" Kind="Bidder" Empty="Yes">
              <ComplCaption/>
              <ComplBody>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">&#x27;</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">....................................................&#x27;</span>
              </ComplBody>
              <ComplTail/>
             </TextComplement>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:19.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:33.00mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Vom Bieter einzutragen)</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Sammelbefestigung 30 E90</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGEEGIA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Kabelrinne, Kabelbahn</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit gesickter Bodenlochung und Seitenlochung, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">eingerollte Kante im Seitenholm zur Verstärkung</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">und als Kantenschutz, inclusive Verbinder-Set.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korrosionsschutz: bandverzinkt </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN EN 10327</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blechstärke: 0,75 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitenhöhe: 60 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragfähigkeit: 1,1 kN/m </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bei Stützabstand 1,5m</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabelrinne, Kabelbahn</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGCMAAA" RNoPart="140">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kabelrinne 400 mm E90 Funktionserhalt</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kabelrinne 400 mm E90 Funktionserhalt</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGEKGLI" RNoPart="150">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trennsteg zur Trennung von Kabeln und Leitungen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zum Einbau in Kabelrinnen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schraublose Klemmbefestigung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korrosionsschutz: bandverzinkt, nach DIN EN 10327</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitenhöhe: 60 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Trennsteg</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGENPJI" RNoPart="160">
          <Qty>10.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steigeleiter 400 x 60 mm E30 Funktionserhalt</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit durchgängig gelochtem Seitenholm, mit eingenieteten, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach oben offenen C-Profil-Sprossen, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Befestigung von Kabeln und</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leitungen mit Bügelschelle, eingerollter</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitenholm zur Verstärkung und als Kantenschutz</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korrosionsschutz: bandverzinkt nach DIN EN 10346</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitenhöhe: 60 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: 400 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 6000 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Holmstärke: 1,5 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprossenabstand: 300 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragfähigkeit: 3,1 kN/m bei Stützabstand 1,5m</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und montieren</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Steigeleiter 400 x 60 mm E90 Funktionserhalt</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGFPAAA" RNoPart="170">
          <Qty>40.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Steigeleiter 400 x 110 mm E30 Funktionserhalt mit Abdeckung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit durchgängig geschlossenen Seitenholm, mit eingenieteten, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach oben offenen C-Profil-Sprossen, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Befestigung von Kabeln und Leitungen </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Bügelschelle, eingerollter Seitenholm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zur Verstärkung und als Kantenschutz</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inkl verriegelbaren Deckel </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Korrosionsschutz: bandverzinkt nach DIN EN 10346</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Seitenhöhe: 100 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: 400 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 6000 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Holmstärke: 1,5 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sprossenabstand: 300 mm</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tragfähigkeit: 3,1 kN/m bei Stützabstand 1,5m</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">liefern und montieren</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Steigeleiter 400 x 110 mm E90 Funktionserhalt mit Abdeckung</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGNGABI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Befestigungen - Kabelrinnen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle nachfolgend aufgeführten Befestigungen sind mit </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zugehörigem Montagematerial zu liefern und fertig </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu montieren. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Einschließlich Befestigungsmaterial und Montage.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungsmaterial und Kabelrinnenmontage sind</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in die Einheitspreise einzukalkulieren!</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Befestigung - Kabelrinnen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGGIDCKI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Wandausleger</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zur Aufnahme von Kabelpritschen oder Kabelrinnen,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einschl. systemgebundenem Zubehör, feuerverzinkt </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN 50 976, für mittelschwere Lastverhältnisse, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung mit Schwerlastankern an Beton- oder Mauerwerkswänden.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Wandausleger</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGICAAA" RNoPart="180">
          <Qty>10.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Wandausleger-Nennbreite</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennbreite: 410 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Wandausleger-Nennbreite 410 mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGGNAAA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Starres Kunststoff Isolierrohr, halogenfrei</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nach DIN VDE 0605 für mittlere Druckbeanspruchung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">flammwidrig (ACF).</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verlegung mit Schellen auf bzw. unter Putz.,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">inklusive aller Befestigungsmaterialien</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Starres Kunststoff-Isolierrohr, halogenfrei</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGGNPKI" RNoPart="190">
          <Qty>25.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoff-Isolierrohr halogenfrei</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nenngröße: M20</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kunststoff-Isolierrohr M20 halogenfrei</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGGCAAAA" RNoPart="200">
          <Qty>25.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoff-Isolierrohr halogenfrei</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nenngröße: M25</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kunststoff-Isolierrohr M25 halogenfrei</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGCIEAI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für Gebäudeaustritt des Kabels soll ein bestehendes </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gitterelement der in der Tiefgaragenwand durch ein </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metallelement mit Kabeldurchführungen getauscht werden. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Dieses ist in der nachfolgenden Position anzubieten.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGCJDOI" RNoPart="210">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Blech als Wandverschluss mit Kabeldurchführungen</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Metall-Element mit Rohrrahmen aus Stahl pulverbeschichtet </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in RAL-Farbe gemäß Kundenwunsch. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zum Einbau in bauseits vorhandene Wandöffnung in den </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Maßen:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Länge: 1m</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe:  0,6, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bestückt mit folgenden Kabeldurchführung :</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  - 15 x Kabelverschraubeung M40 19-28 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> -    2 x  Kabelverschraubung  M32 15-21 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> -    2 x  Kabelverschraubung  M25 11-15 mm</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Blech als Wandverschluss mit Kabeldurchführungen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFMDBEI" RNoPart="5">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>444.5 Installationsgeräte</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFMJJAI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">F</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ür den neuen NSHV-Raum ist eine Rauminstallation </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Feuchtraumwannenleuchte und Schaltersteckdosen- kombination in Aufputz-Installation herzustellen </span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFMKKKI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Installationsgeräte</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Alle nachfolgenden Installationsgeräte sind in einem </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einheitlichen Schalterprogramm und soweit nicht anders </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">benannt vom selben Hersteller anzubieten. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Rahmen und Abdeckungen / Wippen sind, wenn nicht anders beschrieben, mit in die Einheitspreise einzukalkulieren.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung der Einbaugeräte in den Gerätedosen erfolgt </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ausschließlich über Rahmenschrauben, </span>
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">nicht</span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> über Krallen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farben und Oberflächen sind auch in der Eigenschaft </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(z.B. matt oder glänzend) anzugeben.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Installationsgeräte</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFMLOFI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Schutzkontaktsteckdose</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für alle nachfolgenden Steckdosen gilt:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nach DIN 49440/44, DIN VDE 0620,</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">gemäß DIN VDE 0620 Teil 1.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Soweit nicht anders beschrieben mit:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">max. Nennstrom </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: 16 A</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Nennspannung </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: AC 250 V</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Material</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: Thermoplast</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigung</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">: Schraubbefestigung</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive Rahmen / Abdeckungen und Beschriftungen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Unterputzausführungen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive Befestigungsmaterialien und Beschriftungen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Aufputzausführung.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Schutzkontaktsteckdose</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGBAIEA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">SCHUKO Schalter-Steckdose, AP lichtgrau, 1-fach</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung wie zuvor, jedoch:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* schlagfeste AP-Ausführung,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* mit Steckklemmen,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Klappdeckel,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* IP44, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* beschriftbar mit Schriftfeld-Einsatz,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Farbe lichtgrau.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>SCHUKO Schalter-Steckdose, AP lichtgrau, 1-fach</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGGBCEGI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Geräte-Abzweigdosen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">DIN 49 073, aus Isolierstoff, Nennspannung 400 V, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Stutzen und Führungen für Aufbau von Kombinationen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Schraubbefestigung, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungsmaterial sind in die Einheitspreise </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">einzukalkulieren.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Geräte-Abzweigdosen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGGBDFMI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Verbindungsdosen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);"> </span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">(Abzweigdose) nach DIN VDE 0606, aus Isolierstoff, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Innenmaß 70, mit Steckklemmen, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: IP 54 mit Einsteckstutzen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Verbindungsdosen</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGGBEGOI" RNoPart="20">
          <Qty>2.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verbindungsdose 2,5 mm²</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung wie vor, jedoch</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">für Nennquerschnitt: 2,5 mm²</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Verbindungsdose 2,5 mm²</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGFMFCOA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">In den Betriebsräumen, welche von der Sanierung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Elektro-Anlagen betroffen sind, wird die Beleuchtung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit LED Feuchtraumwannenleuchten erneuert.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Remark ID="AAAAAAAAIGFMGHAI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Für alle nachfolgend aufgeführten Leuchten gilt: </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Liefern und betriebsfertig montieren.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umfang:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Annahme und Zwischenlagerung,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Montage der Leuchten,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Anschluss der elektr. Leitungen,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Komplettierung,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">* Inbetriebnahme.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Befestigungsmaterialien sind in die Einheitspreise einzukalkulieren!</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Für alle nachfolgend aufgeführten Leuchten gilt:</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFMHGMI" RNoPart="30">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Feuchtraumwannenleuchte</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Decken- und Wandleuchte für Feuchtraum-Standard-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">anwendungen.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für LED  min. 20 W. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Deckenbefestigung direkt oder mit beiliegender Schnell-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">montageklammer möglich. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abgehängte Montage erfolgt über beiliegende Edelstahlbügel. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit PMMA-Abdeckwanne, klar. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Außen glatt, mit innen liegenden Längsprismen und fein</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">strukturierten Stirnseiten, aus einem Stück gefertigt.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sicherer Halt der Wanne durch Kipphebelverschlüsse </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aus glasfaserverstärktem Polyamid.  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leuchtenkörper aus glasfaserverstärktem Polyesterharz, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">schwer entflammbar. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit stirnseitiger Einführung und Würgenippeln für Netzzuleitung.  </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leuchtenkörper Farbe lichtgrau, ähnlich RAL 7035. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzklasse I, Schutzart IP66, Schlagfestigkeit 0,2 J.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Mit elektronischem Vorschaltgerät, schaltbar. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzweiterleitung, mittige Einspeisung oder Anordnung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zu Lichtbändern mittels Innenverdrahtungszubehör.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Inklusive notwendigem Zubehör.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Feuchtraumwannenleuchte</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="AAAAAAAAIGFLAAAA" RNoPart="3">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>446 Blitzschutz- und Erdungsanlagen</span>
      </p>
     </LblTx>
     <BoQBody>
      <BoQCtgy ID="AAAAAAAAIGFLBAKA" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>446.4 Potentialausgleich</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFLDDEI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für den neuen NSHV-SV-Raum ist eine Potentialausgleichsschiene sowie die Anbindung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">an den Hauptpotentialausgleich herzustellen. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Trassen sowie Kabelführungssystem sind in den</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">PE einzubinden.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFLEDLA" RNoPart="10">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <CtlgAssign>
           <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
           <CtlgCode>053</CtlgCode>
          </CtlgAssign>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Potentialausgleichsschiene für den Potentialausgleich </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">nach DIN VDE 0100 Teil 410/540 und den Blitzschutz-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Potentialausgleich nach DIN EN 62305-3 / VDE 0185-305-3, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bestehend aus:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">2 Schienenböcke,1 Abdeckhaube aus halogenfreiem Kunststoff,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 Klemmschiene für 15 Teilungseinheiten aus Messing</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">galvanisch verzinnt, 3 Reihenklemmen für Runddraht </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Durchmesser 8-10mm oder Kabel bis 95mm² aus Stahl </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">galvanisch verzinnt, 9 Reihenklemmen für Kabel bis 16mm² Stahl galvanisch verzinnt, Abdeckung, Kabel und Kabel-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgänge, einschl. Beschriftung, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">komplett liefern und betriebsfertig </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">montieren.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Potentialausgleichsschiene 217 mm CuZn</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFLGANA" RNoPart="20">
          <Qty>1.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Potentialausgleichsschienen für den Schutz- und Funktions-</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">potentialausgleich nach DIN VDE 0100-410/540</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Ausführung:</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- geprüft nach DIN VDE 0609</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Reihenklemmen St/gal Zn</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bestehend aus:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:21.90mm 14.90mm 34.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-   1x Klemmschiene für Potentialausgleichsschiene -10x10 mm </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"/>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">         aus Messing, vernickelt, l=645mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">-   2x Schienenbock</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 30x Reihenklemme für PAS 2,5-16qmm St/galZn-NIRO</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">betriebsfertig liefern, montieren und anschließen</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Potentialausgleichsschiene mit Reihenklemmensystem 645mm CuZn</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFLHNGI" RNoPart="30">
          <Qty>50.000</Qty>
          <QU>m</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kunststoffaderleitung DIN VDE 0281 H07V-K 1 x 16,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Cu-Zahl 154, auf vorh. Kabelrinnen oder in offene Kanäle, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Farbton grün/gelb, Arbeitshöhe bis 4 m.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kunststoffaderltg. H07V-K 1x 16 vorh.Kabelrinne/Kanal</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFLJIEI" RNoPart="40">
          <Qty>20.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Anschliessen metallischer Teile</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Gewindeschraube M6-M8,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Unterlegscheiben, Sprengring, Mutter,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">in vorhandene Bohrungen </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">bzw. Gewinde-Steckbolzen, betriebsfertig erstellen, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">anschließender Ader mit Kabelschuh, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">passend zur Schraube und zum Kabel </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">6 - 50 mm2</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Anschliessen metallischer Teile</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFLLDII" RNoPart="50">
          <Qty>20.000</Qty>
          <QU>St</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bohrungen in vorhandenen Bauteilen aus Metall</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Gewindeherstellung bis M8, </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Gewindelänge: 12 mm</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Hinweis:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei Anlagen von Fremdgewerken ist die Ausführung </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Bohrung eigenverantwortlich mit</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">dem entsprechenden Fremd-AN abzustimmen.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Bohrungen in vorhandenen Bauteilen aus Metall</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
    <BoQCtgy ID="AAAAAAAAIGFIAAAA" RNoPart="4">
     <LblTx>
      <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
       <span>449 Starkstromarbeiten, sonstiges</span>
      </p>
     </LblTx>
     <BoQBody>
      <BoQCtgy ID="AAAAAAAAIGFIBAGA" RNoPart="1">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>449.1 Demontagearbeiten</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFJEBHI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Schaltanlage der RWA S2 muss von dem NSHV-AV-Raum über den Flur in den benachbarten NSHV-SV-Raum umgezogen werden. </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Leistung ist gemäß Beschreibung in der nachfolgenden Position anzubieten. </span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFJFDLA" RNoPart="10">
          <LumpSumItem>Yes</LumpSumItem>
          <Qty>1.000</Qty>
          <QU>PSCH</QU>
          <CtlgAssign>
           <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
           <CtlgCode>053</CtlgCode>
          </CtlgAssign>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Umzug  der Schaltanlage für die RWA S2 vom  NSHV-AV-Raum über den Flur ebenerdig in den benachbarten NSHV-SV-Raum.</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Daten Schaltanlage:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteiler aus Stahlblech mit Pulverbeschichtung mit der Schutzklasse IP 65 </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Raumaufstellung: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NSHV AV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                     </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Verteilerkasten aus Stahlblech / Standschrank</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Reihenspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">1 kV</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Betriebsspannung:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">0,4 kV, AC</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Netzform:</span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                    </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">TN-S</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Schutzart: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                  </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">IP 43</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Schrankabmessungen und Ausstattung</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Höhe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                        </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">200 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Breite: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                       </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">  80 cm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">                                                         </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;tab-stops:51.90mm 54.90mm 74.90mm;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Tiefe: </span>
               <span style="font-family:Arial;font-size:10;mso-tab-count:1;">                                         </span>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);"> 60 mm</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Anschlussarbeiten für folgende Kabel sind für diese Anlage sowohl für die Demontage als auch für die Wiederinbetriebnahme einzukalkulieren und anzubieten:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <ul style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">
               <li style="tab-stops:19.90mm 39.80mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W001 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">7x1,5mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">   </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH</span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W002 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4x4mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH </span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W003 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">3x4mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH </span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W004 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">4x4mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH </span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W005 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5x2,5mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH</span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W006 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">7x1,5mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH </span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W007 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">12x2x0,8 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Meldung </span>
               </li>
               <li>
                <span style="font-family:Arial;Color:rgb(0,0,0);">‑</span>
               </li>
               <li style="tab-stops:19.90mm;">
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">W000 </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;">          </span>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">5x4mm² </span>
                <span style="font-family:Arial;font-size:10;mso-tab-count:1;"/>
                <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">NHXH</span>
               </li>
              </ul>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Umzug Schaltanlage RDA S2</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFJIAAA" RNoPart="2">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>449.2 Brandschutzmaßnahme</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFJJAAA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für folgende Durchbrüche sind Schottungen eingeplant:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- 3x KB DN150 NSHV AV = NSHV SV Raum</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Promatkanal für kreuzende Leitung im NSHV-SV-Raum</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFOBFOI" RNoPart="10">
          <Qty>5.000</Qty>
          <QU>m2</QU>
          <CtlgAssign>
           <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
           <CtlgCode>047</CtlgCode>
          </CtlgAssign>
          <Description>
           <STLBBau>
            <STLBBauCtlg>
             <CtlgName>STLB-Bau</CtlgName>
             <VersDate>2024-04</VersDate>
             <WCtg>047</WCtg>
             <Group>1235</Group>
            </STLBBauCtlg>
            <STLBBauID>
             <ArtChrIdent>1936</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>4201</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>5</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>1932</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2163</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>105</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>3995</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>53</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2628</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>36</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>5308</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>45</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>9122</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>127</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>1631</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>4</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>10164</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2136</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>22233</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
           </STLBBau>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzbekleidung für den Funktionserhalt an Kabel-/Leitungsanlagen, Beflammung von außen, rechteckig, mit allgemeinem bauaufsichtlichen Prüfzeugnis, mit Brandschutzplatten aus Kalziumsilikat, Dicke 2 x 20 mm, Ausführung 4-seitig, Feuerwiderstandsklasse E 90 DIN 4102-12, im Gebäude, Arbeitshöhe der zu bearbeitenden oder zu bekleidenden Fläche bis 3,5 m über der Standfläche des hierfür erforderlichen Gerüstes.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Brandschutzbekl. Beflammung außen Kalziumsilikatpl D 2x20mm E90 Gebäude</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFJKAAA" RNoPart="20">
          <Qty>3.000</Qty>
          <QU>St</QU>
          <CtlgAssign>
           <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
           <CtlgCode>047</CtlgCode>
          </CtlgAssign>
          <Description>
           <STLBBau>
            <STLBBauCtlg>
             <CtlgName>STLB-Bau</CtlgName>
             <VersDate>2025-04</VersDate>
             <WCtg>047</WCtg>
             <Group>1204</Group>
            </STLBBauCtlg>
            <STLBBauID>
             <ArtChrIdent>2163</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>108</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>4201</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>3</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2628</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>36</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>7955</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>84</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>9122</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>126</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2439</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>66</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>1282</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>20</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>828</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>4207</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>4209</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>4</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>4206</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>3</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>172</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>7</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>10164</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>2136</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>15</ChVIdent>
            </STLBBauID>
            <STLBBauID>
             <ArtChrIdent>10970</ArtChrIdent>
             <ArtChIdx>0</ArtChIdx>
             <ChVIdent>1</ChVIdent>
            </STLBBauID>
           </STLBBau>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Brandschutzabschottung an Kabel-/Leitungsanlagen als flexibles Schott, Feuerwiderstandsklasse S 90 DIN 4102-9, mit allgemeinem bauaufsichtlichen Prüfzeugnis/allgemeiner bauaufsichtlicher Zulassung, runder Durchbruch, Durchmesser über 150 bis 200 mm, Baustoffklasse DIN 4102-1 A (nichtbrennbar), Schmelzpunkt größer gleich 1000 Grad C, im Gebäude, Wand aus Stahlbeton, Dicke 240 mm.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Brandschutzabschottung Leitungsanlagen flexibler Schott S90 Durchm. 150-200mm Gebäude Wand D 240mm</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFJCAAA" RNoPart="3">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>449.3 Schlitze, Bohrungen und Durchbrüche</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFJNDMA">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Hinweis</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Folgende Kernbohrungen sind eingeplant:</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- NSHV AV =&#x3e; NSHV SV 3 x DN 150</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Hinweis</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFJOFII" RNoPart="10">
          <Qty>3.000</Qty>
          <QU>St</QU>
          <CtlgAssign>
           <CtlgID>AAAAAAAAIGCJADGI</CtlgID>
           <CtlgCode>084</CtlgCode>
          </CtlgAssign>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Kernbohrung, Untergrundfläche senkrecht, aus Stahlbeton, Normalbeton, Bohrdurchmesser über 150 bis 200 mm, Bohrtiefe über 25 bis 30 cm, nicht schadstoffbelastet,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abfall ist nicht gefährlich, Zuordnung LAGA Z 0 (uneingeschränkter Einbau), Wichte des Abbruchstoffes DIN EN 1991-1-1 24 kN/m3,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Geräteeinsatz ist möglich, max. Gesamtgewicht bis 5 t, Ausführung innerhalb des Bauwerks, Ausführung im Erdgeschoss,</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">aufgenommene Stoffe sammeln, ohne Zerkleinerung,</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auf LKW des AN laden und entsorgen.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Kernbohrung Stahlbeton Durchm. 150-200mm T 25-30cm nicht schadstoffbelastet Geräteeinsatz mgl. Stoffe</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
      <BoQCtgy ID="AAAAAAAAIGFIDBDI" RNoPart="4">
       <LblTx>
        <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
         <span>449.4 Stunden und weitere Leistungen</span>
        </p>
       </LblTx>
       <BoQBody>
        <Itemlist>
         <Remark ID="AAAAAAAAIGFIEBII">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Stundenlohnarbeiten</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Vergütung der Stundenlohnarbeiten sind als feste Stunden</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verrechnungssätze gem. § 15 VOB/B anzubieten. In ihnen sind </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die Lohn- und Gehaltskosten, die Gemeinkostenteile einschl. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der Sozialkassenbeiträge und vermögenswirksamen Leistungen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">sowie Lohn- und Gehaltsnebenkosten enthalten.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zuschläge für Nacht-, Sonn- und Feiertagsarbeiten sind nicht in </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">die Verrechnungssätze einzubeziehen, sondern ggf. gesondert </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">auszuweisen.</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sämtliche Stundenlohnarbeiten dürfen nur nach ausdrücklicher </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Aufforderung der örtlichen Bauleitung ausgeführt werden.</span>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Stundenlohnzettel müssen eine nachvollziehbare Beschreibung </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">der ausgeführten Leistungen in Stichworten einschl. Material-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">verbrauch und Maschineneinsatz sowie Namensangabe </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">mit Berufsgruppe enthalten.</span>
               <br/>
               <br/>
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die Stundennachweiszettel sind der Bauleitung täglich jeweils </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vom vorhergehenden Tag zur Anerkennung vorzulegen. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bei verspäteter Vorlage erlischt der Anspruch auf Vergütung. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Die vereinbarten Stundensätze haben Gültigkeit unabhängig </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von der Anzahl der abzurechnenden Stunden. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Bieter erklärt mit seiner Unterschrift unter dem Angebot, </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">dass die Verrechnungssätze unter Beachtung der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">preisrechtlichen Vorschriften ermittelt wurden und unabhängig </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">von der Anzahl der abzurechnenden Stunden gelten. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Abgerechnet werden nur die auf Anordnung der örtlichen </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Bauüberwachung tatsächlich geleisteten Arbeitsstunden.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Fahrt- und Wegezeiten sowie Aufsichtsstunden werden nicht </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">vergütet.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Stundenlohnarbeiten</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFIFIBI" RNoPart="10">
          <Qty>5.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">OBERMONTEUR</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>OBERMONTEUR</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFIHCCI" RNoPart="20">
          <Qty>20.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">MONTEUR</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>MONTEUR</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFIIMDI" RNoPart="30">
          <Qty>20.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ELEKTROHELFER</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>ELEKTROHELFER</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Remark ID="AAAAAAAAIGFIKGDI">
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-weight:bold;font-size:10pt;Color:rgb(0,0,0);">Zuschlagssätze</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;text-decoration:underline;font-size:10pt;Color:rgb(0,0,0);">Hinweis:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zuschlagsätze für Arbeiten außerhalb der normalen Arbeits-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">zeiten. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für anfallende Arbeiten außerhalb der Regelarbeitszeit kann </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">ein Zuschlag je Arbeitsstunde zusätzlich zur Abrechnung der </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Leistungspreise abgerechnet werden</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Diese Zuschläge sind zu unterscheiden für die nachfolgenden </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Uhrzeiten und Wochentage:</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitszeit von 18:00 bis 22:00 Uhr / abends</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitszeiten von 22:00 Uhr bis 06:00 Uhr / nachts</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitszeiten Samstag ab 18:00 bis 22:00 Uhr / abends </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">- Arbeitszeiten Samstag ab 22:00 Uhr bis 6:00 Uhr/ nachts.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Der Samstag wird bis 18:00 Uhr als normale Arbeitszeit und </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Werktag angesetzt.</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;"/>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Für in diesen Zeiten ausgeführte Leistungen sind in den Bau-</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">tagesberichten aufzuführen und der Bauleitung wöchentlich zu </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">übergeben. </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Jede dort aufgeführte Stunde wird, mit den unten angegebenen</span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Zuschlägen, zusätzlich zu den normalen Herstellungskosten </span>
              </p>
              <p style="text-align:justify;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">abgerechnet.</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Zuschlagssätze</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Remark>
         <Item ID="AAAAAAAAIGFILJNA" RNoPart="40">
          <Qty>2.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Obermonteur </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeiten zwischen 18.00 Uhr und 22.00 Uhr</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Obermonteur für Arbeiten zwischen 18.00 Uhr  und 22.00 Uhr</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFINCKI" RNoPart="50">
          <Qty>8.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Obermonteur </span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sonn- und Feiertagszuschlag</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Obermonteur Sonn- und Feiertagszuschlag</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFIOLCI" RNoPart="60">
          <Qty>2.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Monteur</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Arbeiten zwischen 18.00 Uhr und 22.00 Uhr</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Monteur Arbeiten zwischen 18.00 Uhr und 22.00 Uhr</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
         <Item ID="AAAAAAAAIGFJAEDA" RNoPart="70">
          <Qty>8.000</Qty>
          <QU>Std</QU>
          <Description>
           <CompleteText>
            <DetailTxt>
             <Text>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Monteur</span>
              </p>
              <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
               <span style="font-family:Arial;font-size:10pt;Color:rgb(0,0,0);">Sonn- und Feiertagszuschlag</span>
              </p>
             </Text>
            </DetailTxt>
            <OutlineText>
             <OutlTxt>
              <TextOutlTxt>
               <p style="text-align:left;margin-top:0pt;margin-bottom:0pt;">
                <span>Monteur Sonn- und Feiertagszuschlag</span>
               </p>
              </TextOutlTxt>
             </OutlTxt>
            </OutlineText>
           </CompleteText>
          </Description>
         </Item>
        </Itemlist>
       </BoQBody>
      </BoQCtgy>
     </BoQBody>
    </BoQCtgy>
   </BoQBody>
  </BoQ>
 </Award>
</GAEB>
